6 ton coal fired steam boilers
Gas Steam Boiler non-normal stall, a phenomenon and treatment, flame reasons: 1, the operation of the auxiliary power supply or trip interruption. 2, boiler combustion instability. 3, the load is too low, so that the load sharply mill automatic ignition energy loss or failure of combustion. 4, mutant coal, coal volatile or low calorific value. 5, the automatic combustion flame detector failure or failure caused by tripping mill. 6, or blast furnace wall tubes serious improper boiler soot-blowing operation, a large amount of water vapor into the combustion chamber. 7, coal pulverizing system, fuel system failure, resulting in a significant amount of fuel reduction or interruption. Or with a large amount of water in the fuel oil gun blocked too many impurities, low pressure steam or atomized. Second, the phenomenon: 1, a significant increase in furnace pressure, furnace flame monitoring flameless CRT display. See the fire no fire hole, BTG warning window MFT warning lights. 2, the unit load decrease, the steam flow drops rapidly, each segment working medium temperature, the vapor pressure decreases, the value of oxygen surge. Third, the method of treatment: 1, if the MFT tripping protection, should an emergency shutdown processing, stop the supply of fuel. 2, identify the cause flameout, and try to eliminate, to conduct a comprehensive inspection of the boiler, after confirming the device properly, can restart. How early circulating fluidized bed boiler ignition achieve the protection of reheaters? Fire causes of valve failure chemical industry regulation and Countermeasures bearing parts heat treated high boiler common defects due to low bypass the security gate and reheaters failure phenomenon and treatment of condensate pump turbine worm gear failure cause analysis and improvement measures in the pneumatic valve powder operating system instructions on how to implement.
Horizontal 0.5 tons supervisory inspection-free amount of gas 6 ton coal fired steam boilers is how much? There are a lot of users call and ask when will the relationship between the amount of gas steam boilers are, of course, this problem is related to the user's operating costs, and all of us today about 0.5 tons of horizontal gas-free amount is how much steam boiler inspection supervisor . First to introduce my company developed its own supervisory inspection-free steam boiler, only about 110 degrees this steam boiler exhaust gas temperature, and ordinary steam boiler exhaust gas temperature as high as 250-350, saves considerable steam boiler if the index is to see its exhaust gas temperature, exhaust gas temperature is lower fuel burn more fully explained in the furnace, the more fuel is absorbed by the heat from the steam boiler, the more fuel-efficient, the company supervisory inspection-free horizontal 0.5 tons of steam per hour coal boiler is about 40-50 kg, Common horizontal 0.5 tons coal consumption is about 70-80 kg.
Run chemical plant boiler problems that may arise is what chemical plant boiler operation possible problem is? There are two main chemical plant boiler evaporation: evaporation and rated maximum continuous evaporation. When the chemical plant boiler load is higher than the maximum continuous evaporation, it indicates the operating force or overload. The following problems may occur super-load operation: Main results are as follows: (1) due to increased fuel consumption, furnace volume heat load increases, the furnace temperature and furnace flue gas outlet temperature, resulting in the superheater and reheater the superheated steam temperature and wall temperature, and must therefore be strictly monitored and adjusted. Try not to let this time overheating. Coal furnace, furnace volume due to the increased thermal load, increasing the likelihood of slagging. (2) the flow rate of chemical evaporation apparatus system working fluid increases, the flow resistance is increased, it is not conducive to water circulation. Therefore, we should pay particular attention to the monitoring of the water cycle bad area. (3) the pressure differential between the drum and the superheater outlet flow increases as the working fluid and superheater flow resistance increases, so that the pressure of the steam drum and headers increases, the strength of these components must be considered . Space volume load (4) the steam drum, the load increases the evaporation surface, saturated with water vapor would increase, thus affecting the quality of steam. (5) chemical plant boiler safety valve Total displacement designed according to a maximum continuous evaporation. If the chemical plant boiler overload, once the sudden load shedding, the safety valve will not fully open, the steam pressure can not be reduced quickly. At this point, it is necessary to ensure the safety of the boiler by chemical vapor released into the air exhaust valve. (6) With the increase of the amount of air required for combustion and the amount of smoke produced, once sufficient air supply, the air volume is insufficient, the chemical conditions affecting the combustion boiler, increasing the likelihood of slagging; In addition, since the flue gas velocity the increase in fly ash increased the degree of wear of the heating surface. (7) during operation, the exhaust gas temperature rises, the exhaust gas heat loss; shorter residence time in the furnace the fuel, incomplete combustion heat loss of mechanical and chemical incomplete combustion to increase the heat loss, reduce the thermal efficiency of the chemical plant boilers. In summary, the excess chemical plant boiler operation have an adverse impact on the security and economic, should generally not excessive run. If the special emergency must also be strictly limited scope and excess power beyond the time required to force.
Our business-to-6 ton coal fired steam boilers produces steam attaches great importance to the quality of good or bad, it will indirectly determine the quality of our food is produced dates. The fact that we choose fast boiler is correct. We are very grateful to our fast boiler manufacturing plant in a short time, installation and commissioning of these two steam boilers, advance our production line went into operation. --customer feedback