2 ton Diesel Oil Fired wns Steam Boiler
What companies need to use 2 ton diesel fired wns steam boiler steam boiler uses a very broad, both in production and life plays a very important role. The use of a wide boiler, industrial and civil division, the following companies will be used in steam boilers: steam boiler through the heat exchanger, the heat exchange steam water supply, water heating, then heating, heating, bathing, production and other uses. Food industry: aspects of food processing, medical industry and is used as filling bottles and other disinfecting, the food industry can be used as steamed meat, meals. Wine also used steam. The petrochemical industry, the oil and steam may be heated to increase the flowability. Petrochemical manufacturing process also with steam. Manufacturers, with more extensive use of the steam, such as a sheet of foam insulation, heating with steam production foamed material production. Furniture made of wood to use steam drying, in order to make furniture. Filling brick building is also used for drying steam, can also generate electricity and so on. Washing Ironing industry: dry-cleaning machine, dryer, washing machine, dryer, ironing machine, iron and other equipment for the use of packaging machinery industry: labeling machines, standard sets of supporting the use of bio-chemical industry: a fermentation tank, reactor, supporting sandwich pot, mixer, emulsifier and other devices used food machinery industry: tofu machine, steamer, pot sterilization, packaging machines, coating equipment, sealing machine and other equipment for use in other industries :( oil, automobile) steam cleaning industry, (hotels, dormitories, schools) steam or hot water supply, (bridges, railways) concrete curing, etc.
Combustion gas treatment and a malfunction due to gas boiler burner ignition misfire bar: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Gas Burner fails, the action bar ignition misfire following five: Clear, renewal, adjust the distance, change and switching transformer. Second, the gas boiler the ignition spark rod misfiring but the reasons: 1, the disk space ventilation carbon cyclone is blocked, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Gas boiler ignition spark rod action but misfiring are: clear; the first washing, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel) ; check the pipeline and oil filters, insulation equipment; peripheral screw pump removed, carefully remove the cover inside out net oil, diesel oil immersion; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing the causes of instability: 1, air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, gas hot water boiler fuel oil water. When a small fire gas boiler normal and turn the fire extinguished or flashing instability action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; i.e., set to about 50 deg.] C may be; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Burner gas treatment increased noise: ① the check valve in the oil line is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.
Hefei Limin Pharmaceutical Co., Ltd. Nanjing Military Region, formerly the backbone of pharmaceutical companies, the main drug is slowly swallow rather teabag, relying on advanced R & D platform to carry out contract manufacturing, OEM OEM and other business cooperation. China's environmental protection development trend began to take shape, many environmental policies have been put forward for a positive response to the national environmental policy, Limin Pharmaceutical decided to introduce a gas station 2 ton diesel fired wns steam boilers. After an investigation of the boiler market, Limin Pharmaceutical fast boiler is strong comprehensive strength and wealth of experience working for many years in the pharmaceutical industry to attract, party fast according to the actual needs of customers for its recommendation of one of Taiwan 4 tons of steam condensate gas-fired steam boiler (WNS4-1.25-YQ).
What are the precautions in the loading and installation of gas-fired 2 ton diesel fired wns steam boilers?
Gas-fired steam boilers are a very wide range of special equipments, widely used in food, chemical, paper, textile, construction and other industries. In the process of loading and installing a gas steam boiler, some problems must be paid attention, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.
5. The fire resistance grade and fire protection requirements of the boiler house building shall comply with the requirements of the Code for Fire Protection of Building Design and the Code for Fire Protection Design of High-rise Civil Buildings. The ground of the gas steam boiler room should be flat, non-flammable, no water accumulation, and the foundation load should meet the requirements. The power supply voltage of the gas steam boiler room should be stable to avoid causing the electrical components to burn out. If the voltage is unstable, it is recommended to install a voltage regulator. Ventilation equipment should be installed in the boiler room, and the boiler should be kept at room temperature below 50 °.