5 ton gas steam boiler project in spain
What is the heat unit of the boiler?
As we all know, the boiler is a kind of energy conversion equipment. The energy input to the boiler is in the form of chemical energy in fuel, electric energy, heat energy of high temperature flue gas, and through the conversion of boiler, steam with a certain amount of heat energy is outputted. High temperature water or organic heat carrier. Today, let's talk about its unit of heat.
After the gas hot water boiler hot water boiler vaporization emergency 1. Vaporization handler circulating pump stops abnormally pump failure caused by: ① blower stops running immediately. ② immediately open the door, take measures to pressure the fire, lift the chute gate, cutting off the supply of coal grate. ③ In the case of boiler pressure not greater than 0.6MPa (600KPa), the exhaust valve to follow, only a sharp rise in pressure in the boiler deflated, used only relief exceeds 0.9MPa, and the exhaust process to be carried out slowly, prevention boiler due to loss of pressure and more violently again vaporized. ④ close the boiler water, water main gas valve. ⑤ open stop valve recirculation line, to ensure that the water supply pipe velocity convection heating surface (economizer) to prevent re-vaporization of the economizer. ⑥ The operation of the above operation, at the same time to pay the boiler to reduce the boiler water temperature and the furnace pressure. ⑦ After the boiler pressure is normal, i.e., opening the standby circulating pump, into the normal combustion. 2. Treatment failure or sudden loss of power boiler vaporization of power: ① immediately open the door, lift the coal chute slide gate to take pressure fire measures to reduce the oven temperature. ② Grate with the fastest speed in order in the shortest time to fire onto the slag tap. ③ the degree of treatment in the first case. Once a short time can not supply heating network system, antifreeze should take emergency measures. 3. Due to excessive heat boiler boiler vaporization process: ① the immediate closure of the drum, induced draft fan. ② immediately open the door, take measures to pressure the fire, lift the supply of coal chute slide gate, off of coal, while the grate into fast gear. ③ In the case confirmed the presence of water, the boiler can supply water to the boiler body, boiler out of the water while closing the main valve. ④ Open line stop valve recirculation pump to ensure water velocity convection heating surface of the pipe, to prevent the economizer again vaporized. ⑤ Open circulating pump with jog mode, jog each time less than 30 seconds, again less than one minute jog interval. Jog purpose is to reduce the boiler water temperature, while preventing a large amount of steam into the pipeline system. ⑥ back into place after the safety valve, circulating pump running, and then the normal burning stove. 4. Water boiler system run vaporization process due to water loss, loss of pressure caused by: ① immediately closed drum, induced draft fan. ② out of the water while closing the main valve and the boiler circulating pump. ③ take the same measures to cool the furnace tube described above. ④ Open stop valve recirculation line. ⑤ rely exhaust valve until the safety valve back into place. ⑥ until the boiler water temperature drops below 50 ℃, when the temperature of the furnace temperature less number 200 ℃, again within the boiler feed water, water course to be carried out slowly, to prevent harm to the boiler when the temperature is too large. ⑦ After processing leakage fault, the system time to the replenishment, and out of the water boiler always open the valve, and the circulating pump, and then normal combustion.
Teach you how to properly operate a 5 ton steam boiler project in spain: steam boiler before use to conduct the inspection of the damaged insulation, burner check to see whether the normal operation, also check to ensure that the open position of the valve is correct, check the device controlled device instrumentation and safety equipment accessories, equipment must meet the requirements. Steam boiler furnace entry point confirmation are: Open the valve before and after the oil circulation pump, oil heating flow valve opens, the liquid level in the sump reasonable mediate high position, confirmed that the gas pressure before ignition of the gas burner to the range, the power supply is normal .
To speed up the transformation of coal-fired boiler project, the Tianjin Municipal Government were tender for coal-fired boiler products. In the bidding site, a number of boiler prosperity across the country have resorted to every means, come to bid on his own star product. Fang fast low nitrogen water tube boiler with its unique architecture and technology, will come to the fore in this bid, the successful bidder Tianjin Justice Drive surrounding district project.