92 high efficiency oil Fired Hot Water Boiler
On the following safety rules for oil or gas boiler from Henan fast boiler manufacturers of small series to tell you about the maintenance of the fuel gas-fired boiler. Servicing fuel gas-fired boiler can be divided into quarterly and annual maintenance service. Maintenance quarter (1) wash pump inlet filter and oil filter screen. (2) Check the pump packing and the like. (3) open manhole, hand hole cleaning boilers, internal inspection of boiler fouling and corrosion conditions, to determine the treatment and determine the need for periodic regeneration chemical cleaning. (4) washing water level gauge, three-way stopcock, etc., to check for leakage situation. (5) whether the control box to check that the circuit portion is loose, and clean fouling. (6) Check that all valves are good, and the cleaning operation. (7) on the rotating part of the machine once the lubricating oil is added or oil change. In maintenance (1) to open the fire door before and after the smoke box, check the gasket and soot corroded to decide whether to replace and clean up. (2) when opening the front smoke box, check the burners burner is burned, so that update. (3) check the corrosion of water and sewage pipes and the like. An insulating case (4) Check the electrical, electronics, circuitry, cables. (5) Check the electrical meter box of each instrument, buttons, pressure gauge accuracy.
Modulation (the capacity to vary the boiler output) is a key concern for biomass steam boilers. Generally biomass boilers will only modulate to 40% of their capacity. A typical oil burner will modulate to 20%, and with the installation of multiple burners, oil boilers can modulate to very low output. Biomass boilers respond much less rapidly to variations in load. From start-up they can take several hours to get up to the required temperature and pressure. Steam is much more difficult to store than hot water. The boiler will have some in-built thermal storage and the use of steam accumulators provides some flexibility, but the key barrier at many sites is that a biomass steam boiler should be designed for a consistently required base-load.
March 11, we learned from the Harbin municipal government: Harbin win the 2019 New Blue Sky Battle embodiments released this year, Harbin will be coal-fired pollution control, pollution discharge standards, high Vehicle emission control, comprehensive improvement of urban and rural non-point source, and prohibiting straw utilization as the main direction, precise Shi policy. Strive to the end, so that the sulfur dioxide, nitrogen oxide emissions are reduced by more than 17.6% in 2015 and 20%; concentration of PM2.5 decreased to 52 micrograms / cubic meter or so, and strive to 50 micrograms / cubic meter or less; and more severe reduce the number of pollution days to 21 days or less.
After the proposed scheme, Harbin bulk coal strengthen management and control, strengthening coal quality testing, to improve the sampling frequency. This year will develop clean heating embodiment, the priority development of the city urban central heating; central heating covered areas being difficult to accelerate the implementation of natural gas heating and electric heating, and other distributed clean heating. Unit embodiment "coal to clean energy" should be synchronized removal of coal-fired boiler, gas boiler need replacement after low NOx combustion technology, clean heating rate of 60% or more. City buses, taxis or car clean energy proportion of new energy and strive to reach 94% and 80%. Promote the use of gas vehicles to achieve the national emission standards for six. Six to stop selling below the country's gasoline and diesel. Establish responsibility dust control system, built-up areas prohibit the construction site mixing of concrete, mortar and use of bagged cement 9 city and county (city). Under the premise of protecting people's livelihood, heating boilers should be relatively conducive weather conditions during the pollutant dispersion from the oven, in the same area by different heating boiler early in the evening three periods of peak load shifting from the furnace.
In order to ensure boiler safety, to run smoothly, you must ensure that the use of high-quality natural gas. 1, equipped with one gas separator to increase the capacity, it can effectively store oil and water. Secondly, a level gauge designed to directly observe whether there is liquid in the separator. While the design of the automatic drain pressure relief device is installed. A single control pressure of the air is improved dual control, i.e. the pressure regulating valve is mounted on the main line to control the water separator, the pressure to stabilize, improve security purposes. 2, safety monitoring natural gas as a boiler room burning materials, natural gas leak monitoring must be done. The portable display technology poor performance, poor sensitivity. Host combustible gas alarm system with digital control scaling circuit having an alarm function and a secondary alarm, ensure the safe operation of the boiler. 3, check before firing the safe operation of: (1) whether the boiler inspection gates normally open or closed, check the gas pressure is normal, not too high or too low, open the supply valve leading to the boiler. (2) in the flue baffle must be fully open, otherwise it will affect the purge, causing accidents. Each knob and keep control cabinet to check the normal position. If the stove has a residue should be cleaned. (5) Check the boiler ignition and fire protection program control means should be flexible and reliable. Blast doors should be flexible and rigorous on the boiler. Before the completion of ignition, the ignition is not possible to start the ignition operation: After successful ignition, the load can be adjusted in the normal operation of the boiler when the combustion gas boiler adjusted. We should always observe the combustion furnace, and adjust the amount of steam, wind and steam pressure to ensure the safe operation of the boiler. Note: Program: first five minutes were furnace cleaning, automatic ignition after 5 minutes, observe the ignition is successful, the success of one minute after a small fire can be operated automatically converted to fire properly. For the boiler load and the air pressure adjusted by adjusting the pressure regulator to achieve. When adjusting the load, adjust the air pressure at the same time, it must be synchronized to adjust the air flow to ensure a reasonable match air volume and air volume, in order to achieve economic operation of the boiler. In normal operation, the amount of gas should not be adjusted or reduced drastically in order to avoid dramatic changes in combustion, the pressure receiving member sudden expansion, shrinkage and damage. When the boiler is running, the pressure gauge must be monitored regularly in order to maintain stable water pressure. BCP pressure changes observed, reflecting the relationship between water temperature and steam consumption. In the boiler operation, when the steam pressure is automatically adjusted, the main purpose of the staff is to monitor automatically adjusts the boiler system is sensitive and timely solutions to problems and ensure the sensitivity and reliability of the automatic control system. 4, first close the main valve shutdown operation, the air supply is stopped, the circulating pump and the water pump is still running, when the boiler water temperature falls below 70, and supplies or stops the circulation pump in operation of the pump after about 4 hours. Note: In addition to the accident and emergency parking stop, parking general approach should not cut off the power. After the shutdown, it is timely for the boiler and ancillary equipment to conduct a comprehensive inspection. If you find a defect in the device, and repair should be recorded at the time of shutdown. Safety Precautions 1. burner startup, if the burner is repeatedly locking and alarm, you should find out the cause of the malfunction, press the reset button after troubleshooting, press the reset button and then continue to boot. Note: Press the Reset button for less than 10 seconds. A lower burner inlet must be clean and clean, and does not allow offal. 2. burner once the ignition is unsuccessful, Boiler Fan should be restarted. Ventilation After 5 minutes, start the second startup burner igniter. three. During normal operation, the thermal device near the burner portion (e.g. flange connections) will be very hot, in order to avoid burns. Do not put flammable materials in the vicinity so as not to cause a fire. 4. The operation of the boiler circulating pump must be closely monitored and the 92 high efficiency fired hot water boiler pressure, gas distributor, pipeline valves, pressure gauges, flow meters, water level gauge and the like. 5. When the firefighters open the door or fire door observation, you should wear gloves and a side view. 6. A burner working environment should be kept clean and dry, in particular, a flame detector (i.e. electric eye) should be kept clean, part of the control circuit should humidity and temperature; class should cleaning and maintenance of a combustor. 7. During use, the filter should be cleaned regularly check or replace the filter cartridge in accordance with impurities of the fuel. 8. Check the electrical installations include: wire is damaged, the sheath is damaged, the screw is loose, the contact is good, whether the motor is running abnormal noise. Describes the advantages and disadvantages of natural gas boiler, editor of Sin sets introduced, the use of technology and safety precautions. Industrial boilers to energy efficient, environmentally friendly development direction. Natural gas boiler to meet the needs of these three points. They are the future of the boiler market trend, more and more restricted energy policy, energy saving and environmental protection requirements.