horizontal type oil or gas steam boiler
The oil and gas water tube boiler produced by ZBG is a fast-assembling boiler that can be used in bread factories to steam supply, hot water supply, heating and other uses. Moreover, the boiler has a small footprint, which reduces the investment in the boiler house, and the boiler is highly automated and reduces labor costs.
In order to ensure boiler safety, to run smoothly, you must ensure that the use of high-quality natural gas. 1, equipped with one gas separator to increase the capacity, it can effectively store oil and water. Secondly, a level gauge designed to directly observe whether there is liquid in the separator. While the design of the automatic drain pressure relief device is installed. A single control pressure of the air is improved dual control, i.e. the pressure regulating valve is mounted on the main line to control the water separator, the pressure to stabilize, improve security purposes. 2, safety monitoring natural gas as a boiler room burning materials, natural gas leak monitoring must be done. The portable display technology poor performance, poor sensitivity. Host combustible gas alarm system with digital control scaling circuit having an alarm function and a secondary alarm, ensure the safe operation of the boiler. 3, check before firing the safe operation of: (1) whether the boiler inspection gates normally open or closed, check the gas pressure is normal, not too high or too low, open the supply valve leading to the boiler. (2) in the flue baffle must be fully open, otherwise it will affect the purge, causing accidents. Each knob and keep control cabinet to check the normal position. If the stove has a residue should be cleaned. (5) Check the boiler ignition and fire protection program control means should be flexible and reliable. Blast doors should be flexible and rigorous on the boiler. Before the completion of ignition, the ignition is not possible to start the ignition operation: After successful ignition, the load can be adjusted in the normal operation of the boiler when the combustion gas boiler adjusted. We should always observe the combustion furnace, and adjust the amount of steam, wind and steam pressure to ensure the safe operation of the boiler. Note: Program: first five minutes were furnace cleaning, automatic ignition after 5 minutes, observe the ignition is successful, the success of one minute after a small fire can be operated automatically converted to fire properly. For the boiler load and the air pressure adjusted by adjusting the pressure regulator to achieve. When adjusting the load, adjust the air pressure at the same time, it must be synchronized to adjust the air flow to ensure a reasonable match air volume and air volume, in order to achieve economic operation of the boiler. In normal operation, the amount of gas should not be adjusted or reduced drastically in order to avoid dramatic changes in combustion, the pressure receiving member sudden expansion, shrinkage and damage. When the boiler is running, the pressure gauge must be monitored regularly in order to maintain stable water pressure. BCP pressure changes observed, reflecting the relationship between water temperature and steam consumption. In the boiler operation, when the steam pressure is automatically adjusted, the main purpose of the staff is to monitor automatically adjusts the boiler system is sensitive and timely solutions to problems and ensure the sensitivity and reliability of the automatic control system. 4, first close the main valve shutdown operation, the air supply is stopped, the circulating pump and the water pump is still running, when the boiler water temperature falls below 70, and supplies or stops the circulation pump in operation of the pump after about 4 hours. Note: In addition to the accident and emergency parking stop, parking general approach should not cut off the power. After the shutdown, it is timely for the boiler and ancillary equipment to conduct a comprehensive inspection. If you find a defect in the device, and repair should be recorded at the time of shutdown. Safety Precautions 1. burner startup, if the burner is repeatedly locking and alarm, you should find out the cause of the malfunction, press the reset button after troubleshooting, press the reset button and then continue to boot. Note: Press the Reset button for less than 10 seconds. A lower burner inlet must be clean and clean, and does not allow offal. 2. burner once the ignition is unsuccessful, Boiler Fan should be restarted. Ventilation After 5 minutes, start the second startup burner igniter. three. During normal operation, the thermal device near the burner portion (e.g. flange connections) will be very hot, in order to avoid burns. Do not put flammable materials in the vicinity so as not to cause a fire. 4. The operation of the boiler circulating pump must be closely monitored and the hot water boiler pressure, gas distributor, pipeline valves, pressure gauges, flow meters, water level gauge and the like. 5. When the firefighters open the door or fire door observation, you should wear gloves and a side view. 6. A burner working environment should be kept clean and dry, in particular, a flame detector (i.e. electric eye) should be kept clean, part of the control circuit should humidity and temperature; class should cleaning and maintenance of a combustor. 7. During use, the filter should be cleaned regularly check or replace the filter cartridge in accordance with impurities of the fuel. 8. Check the electrical installations include: wire is damaged, the sheath is damaged, the screw is loose, the contact is good, whether the motor is running abnormal noise. Describes the advantages and disadvantages of natural gas boiler, editor of Sin sets introduced, the use of technology and safety precautions. Industrial boilers to energy efficient, environmentally friendly development direction. Natural gas boiler to meet the needs of these three points. They are the future of the boiler market trend, more and more restricted energy policy, energy saving and environmental protection requirements.
How do I care after the horizontal type oil or steam boiler shutdown method Recently, many users did not know how to call maintenance shutdown after steam boilers, boiler maintenance is very simple in fact, today we explain the steam boiler and hot water boiler after shutdown maintenance. Since the cause of boiler failure or power shutdown required boiler, a steam boiler before travel should stop combustion boiler, the boiler slowly lowering the temperature until no pressure boiler, should pump before shutdown, induced draft fan and turn off the blower. After the maintenance shutdown home for boiler, furnace divided into external corrosion and home for the pot. Pot corrosion enjoying, enjoying their home for two kinds of wet and dry selected based on the length of shutdown time. When long-term disabled boiler, furnace should be paid close attention to external corrosion problems take care of themselves. First, the boiler shutdown cooling is necessary as far as possible completely eliminate fouling and ash grate heating surface of the upper, the lower portion of the furnace. Then have to adhere to certain natural ventilation flue. Under normal conditions, should be placed to dry moisture-proof agent in the furnace, flue. The dry quicklime as used, the furnace or the flue gas per cubic meter of ordinary should be placed about 3kg. After placing all the ventilation should be tightly closed doors. Lime powder to change after change. Such as boiler rooms in low-lying position, the air during shutdown severe flood tide, the method should be used regularly and placed a small fire to dry dry agent phase separation. If the boiler boiler long time, in order to thoroughly clean the soot topcoat red lead oil furnace or other metal surfaces in the anti-corrosion paint. As for the way home for corrosion inside the furnace shutdown, the shutdown Yaoan the length of time to be. Under normal circumstances, no more than one month shutdown of the available wet home for a month or more should take care of themselves dry. Dry to pay attention when enjoying the following questions: Do not dry agent in direct contact with the metal outer boiler, can be housed in a container such as an iron plate; dry agent after standing, for shutting the hole and the other hand hole cover, the vapor, the water pipe necessary to cut off valve; variant lime powder should be replaced. . Enjoying while wet, to pay attention to boiler water condensate is preferably used, followed by the available existing boiler water, demineralized water again; after adding the base, with a slow fire boiler water is heated to 80 [deg.] C the pressure rose to 100 0.2 when the 0.3MPa to maintain 2-3 hours, alkalinity boiler water circulated reach equilibrium, reduced pressure, then filled boiler water, a certain gauge, and continue to adhere to this pressure throughout the home for, alkalinity should Regular testing, decreases should be added at any time; in winter, wet enjoying pay attention to antifreeze, especially the local sewage channel and economizer; before re-use should release all the pot boiler lye, best prepared sump, in order to facilitate then. At the same time should be rinsed with clean water.
Heating and hot water daily is an important basis for maintaining the northern region of the normal operation of enterprises; for Legal Daily organs and units, the hot water boiler is one of the indispensable energy equipment. Currently, work is facing north Heating equipment and facilities aging, increase energy conservation and environmental protection requirements and other issues. Daily logistics-related legal person responsible for improving the overall level of heating units, and the response advocated by the national energy saving, plans to purchase energy-efficient heating boiler. Considering the increasingly stringent environmental policy, Legal Daily authorities decided to use natural gas as boiler fuel. Fast boiler for 20 years, specializing in the production brand boiler, which had been successfully assisted more than Beijing enterprises and institutions, to provide clean heating. The party technical consultant fast boiler based on actual usage Legal Daily units, providing commercial condensing units 99KW vertical 1 hot water boiler.