8000 kg vertical style gas fired steam boiler
What are the precautions in the loading and installation of gas-fired 8000 kg vertical style fired steam boilers?
Gas-fired steam boilers are a very wide range of special equipments, widely used in food, chemical, paper, textile, construction and other industries. In the process of loading and installing a gas steam boiler, some problems must be paid attention, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.
5. The fire resistance grade and fire protection requirements of the boiler house building shall comply with the requirements of the Code for Fire Protection of Building Design and the Code for Fire Protection Design of High-rise Civil Buildings. The ground of the gas steam boiler room should be flat, non-flammable, no water accumulation, and the foundation load should meet the requirements. The power supply voltage of the gas steam boiler room should be stable to avoid causing the electrical components to burn out. If the voltage is unstable, it is recommended to install a voltage regulator. Ventilation equipment should be installed in the boiler room, and the boiler should be kept at room temperature below 50 °.
After the party soon receive an invitation, we attach great importance to this work, and the exclusion of professional and technical personnel around the boiler safety, the contents of energy saving measures, water quality management equipment, load matching programs have been carefully prepared. After the training, all enterprises and institutions representatives have said that through this training to learn a lot of knowledge of the safe use of the boiler, benefit, will do the safe operation of the boiler in accordance with the guidance of experts.
Vertical projection which features good 8000 kg vertical style fired steam boiler boiler having a vertical steam energy conversion device, the input of thermal energy by chemical, electrical, and high temperature flue gas to the furnace, thereby converted into electrical energy, and to provide the desired life for people heat, on the safety and convenience of all with excellent product qualities, then what good salient features vertical steam boiler has it? 1, reliable safety performance vertical steam boiler in terms of product safety has a lot of protection, by ground fault protection, overvoltage protection and power protection and other measures to make operation of the boiler can always be in a safe state, when the pressure is too low or there is leakage, the boiler will cut off its own power button, so to ensure the life and personal safety of the boiler. 2, the portable vertical steam boiler operation which is preferably used, which have to see ease of operation and convenient operation of the boiler does not require user intervention excessive production process, just to the introduction of the electric power source control box start button to enter the automatic operation state, and when the job if the amount of water in the furnace suddenly reduced, the vertical steam boiler control system is also used to automatically replenish the water in the water tank to fill the pump through the apparatus in order to achieve high efficiency of production operations process. 3, small size and yield stability compared with the conventional boiler products, the type and volume of the vertical steam boilers are an advantage, not only a wide range, and the volume of the boiler is very small, but it has a large steam room to make product productivity and quality are the most significant upgrade in order to obtain a more stable production company that won the biggest profits. The above is a brief introduction which has a prominent characteristic of a good vertical steam boiler, not difficult to find, the boiler reliability in terms of safety and convenience of operation have notable features, but also in the volume and yield stability also has a prominent feature , production efficiency and product quality to make the most significant upgrade, but also to ensure personal safety as well as the effect of the use of the boiler.
3 ton oil gas boiler for concrete mixing plant
The product of this project is the CBM wns series oil and gas steam boiler with a boiler capacity of 3 tons. The boiler is used in a building material factory in Russia to provide steam for concrete production.