biomass thermo oil boiler
Biomass biomass thermo boiler case:
The animal feed plant has a seasonal operation, but a relatively consistent load profile. The peak load is for 850 kg/hour of saturated steam at 8 barg (~650 kW see Figure 3). There is a much smaller load required for longer periods for miscellaneous process steam. The load is currently supplied by a very old light fuel oil (LFO) boiler. The load profile here facilitates an almost complete switch from LFO to biomass. 96% of the steam requirement would be covered by a 650kW biomass boiler. A small oil boiler, or built-in oil burner in the biomass steam boiler would be required to meet the smaller steam loads which would not be met efficiently by the biomass boiler. A straight-forward moving grate boiler with fire-tube heat exchangers can be used. The range of suppliers of biomass steam boiler equipment is limited below 1MW thermal as economies of scale are diminished below this level – a 650 kW boiler costs almost the same as a 1MW boiler.
The difference between fuel gas biomass thermo boilers and oil-fired boiler fuel boiler is fuel (such as diesel, oil, kerosene, etc.), fuel gas-fired boiler to gas (such as natural gas, city gas, methane, etc.), depending on what fuel fired boiler combustion device called , a configuration called gas burner boiler gas boiler, oil boiler burner configuration called oil-fired boiler, oil-fired boiler and gas boiler difference lies in the use of fuel burners burn anything.
Burner and flue installation and electrical installation and the fuel supply system of the burner 1, burner 1) before installation read "burner manual", according to the installation requirements. 2) Burner mounting flange, the middle requirements, to ensure the burner to the biomass thermo boiler flue gas does not leak at the interface. 2, the installation of fuel supply system (see schematic) Note: To prevent a fire caused by generation of static electricity in the fuel tank, the tank should have a good grounding. 1) supply system tank top tank top-feed system suction recommended distance between the back plane and the tubing inside diameter of the oil pump axis, the total length of the suction pipe Hm, m, no greater than DL6-34DL40-75DL100-250Di = 10mmDi = 14mmDi = 16mm0.51.03030401.535452.03535452.540503.0404050 Notes: (1) when there is an elbow or valve on the suction pipe, each of the length of the suction pipe to be minus 0.25m. (2) Di recommended internal diameter suction pipe and return pipe. 2) the distance between the bottom of the tank bottom of the tank supply system supply system pipe inner diameter recommended oil pump axis and a plane, the total length of the suction pipe Hm, m, no greater than DL6-34DL40-75DL100-250Di = 10mmDi = 14mmDi = 16mm1.03030401.535452.03535452.540503.04040504.045 Notes: (1) when there is an elbow or valve on the suction pipe, each of the length of the suction pipe to be minus 0.25m. (2) Di recommended internal diameter suction pipe and return pipe. 3, gas pipe installation requirements Burner gas line itself has been connected, the intake port, the intake pipe bends should be minimized and good sealing performance requirements, to prevent leakage. (Iv) a chimney installation, to prevent leakage, the leakage of smoke, to prevent smoke inhalation chamber. 2, a vertical mounting, a right angle bend bends should be avoided. 3, the top of the chimney must be water-resistant measures. (E) mounting a power switch with electrical connection box 1, the power switch should be considered easy to operate, away from heat, fixation, meet the design requirements. 2, the use of 220V (380V), 50HZ power source, and a ground line. 3, voltage instability in the region use, should be safe regulators. Or affect the normal operation of the combustion engine. 4, the power cord to the electrical box must be connected in strict accordance with the requirements, otherwise, there will be dangerous!
Zhengzhou Sunrise Optoelectronics Technology Co., Ltd. by the Dongxu Group, Henan Province, the state-owned asset management companies and Zhengzhou Investment Holdings Limited jointly made, mainly engaged in flat panel display and solar industry design materials, manufacturing and sales operations. Sunrise Optoelectronics project has been put into a production line, the second phase will continue the expansion, three new production lines to meet the production needs of Project Phase II, Sunrise Optoelectronics urgent need to increase new biomass thermo boiler equipment. After investigation and screening of a number of boiler brands, determined to cooperate with the fast boiler, steam signed a 10-ton integrated condensing gas steam boiler (WNS10-1.25-Y.Q).