oil fired water boiler for bath
It provides fast side of boiler equipment, installation and commissioning after all normal, we immediately put into use, the hotel did not delay the normal heating. Meanwhile boiler capacity, energy efficient, fully able to meet the needs of heating and bathing water in our hotel rooms. --customer feedback
Matters needing attention in loading and installation of Gas-fired Steam Boiler
Gas-fired steam boilers are a very wide range of special equipment, usually built in boiler rooms. However, in the process of loading and installation, some problems must be paid attention to, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.
10 tons WNS-type gas heating boiler price is how much money? District, urban heating First, there are two ways of heating coal-fired hot water heating, and second boiler heating fuel gas, fuel oil and gas boiler heating is gradually replacing coal-fired boilers to be the main way of heating the moment, (the main reason can refer to gas-fired boiler and the difference between coal-fired boiler).
Maintenance of the boiler and burner maintenance 1, boiler maintenance and deactivation of backup boiler, should take anti-corrosion measures. 1) maintenance Calorimetry: maintaining the furnace pressure 0.05 ~ 0.09MPa, the water temperature of about 100 deg.] C, to prevent air entering the boiler, this method is suitable within a boiler shutdown week. 2) Wet maintenance: After disabling the boiler, put the water came out, the interior completely remove the dirt and cleaned, refilled been handled well demineralized water, softened water filled boiler. Then adding alkali to the boiler, when added with sodium hydroxide aqueous 5 kg per ton to 6 kg, per ton of sodium carbonate was added if the water 18 kg to 20 kg per ton of water when trisodium phosphate is added 10 kg to 12 kg, maintaining the PH value above 10. The furnace was then heated to 100 deg.] C water, the safety valve is opened, air is discharged in the furnace, and then closed. During maintenance should always check and found that leak that is to be cleared. When the boiler is enabled, it should be drained alkaline solution, and rinse with water, especially when the plot scale boiler must deactivate more clean, because the scale can be soaked in lye and fall off, clog pipes. The method is suitable for longer-term disabled boiler. 2, the burner maintenance: 1) cleaning and maintenance of the burner: Open the combustion head, with a cleaning wipe member or combustion gas, a flame detector wipe with a clean soft cloth, carefully clean the duct and the fan wheel. 2) maintenance of the oil (gas) passage system: Remove fuel (gas) pipeline, cleaning fuel (gas) each filter and nozzle, the drain valve is opened daily oil tank, with exclusion of moisture and impurities in the waste oil. 3) maintenance circuitry: Check whether each wiring is connected firmly assembly is intact and the like.