industrial 5 ton gas fired steam boiler
Fang fast open class formal lecture: products, services both hands April 18, Fang fast open class smooth commencement, partners from across the country converge in the exchange of learning party headquarters R & D building fast training room, professional trainers to share a boiler features, installation and operation precautions, commissioning maintenance process, rapid fault verification, and troubleshooting tips, and other professional knowledge, students listen carefully, positive answer questions, and the atmosphere is very active.
Steam boiler has wide usage in different industries and factories, such as packaging factory, beer industry, food industry, textile industry, chemical industry, power plant, etc. ZG Boiler manufacturers different kinds of industrial boilers, and its capacity is from 1 ton to 410 ton. From 1 ton gas fired industrial 5 ton fired steam boiler to 400 ton coal fired power plant boiler, ZG Boiler has widely product lists. Thus, you will find one most suitable for your industry or factory in ZG. To improve sales performance, ZG Boiler give more profits to dear consumers in steam boiler categories, specially for WNS, SZS gas and oil fired steam boiler, DZL and SZL coal and biomass fired steam boiler. Those four types with fast assembly structure, horizontal style, is easy to be shipped and installed. If you want to get the newest best price lists of industrial steam boiler, please contact with our consumer service. Or email me: [email protected]
Commissioning of Boiler gas boiler commissioning must be carried out after the hydrostatic test. Before commissioning, should be a comprehensive inspection of each furnace parts, electronic control devices, wiring, etc. are normal, water supply, oil furnace if opened, electrical contacts are in the set position. 1, depending on the size of the fuel consumption, the initial damper, the hydraulic pressure. 2, the power is turned on, the power switch to open the cabinet, the water pump starts furnace, (if the pump is rotated into the anhydrous, pump purge valve is opened, the air exhaust pump). 3, control checks whether the normal water level electrode. 4, check the burner operation is normal. Starter burner starts combustion when the water level rose to a predetermined level, the start of combustion is normal to observe: Start no vibration noise, stable combustion, no smoke, orange yellow flame, burning bright clear. Otherwise, to make the appropriate adjustment (refer to burner instructions). Note: The oil pressure between 0.8 ~ 1.0Mpa, after a good tune, do not easily change, oil pressure is too high or too low have an effect on burner performance life. 5, check the pressure gauge pointer swing is smooth, with or without loosening stuck. 6, whether the discharge check valve is set at the set pressure steam: Pressure controller first maximum working pressure, a safety valve is adjusted to the set pressure higher than 0.05MPa, when the furnace pressure was raised to whether the exhaust pressure setting, if exhaust , pulling the safety valve a few times, and try again, if not enough to deal with safety valve to adjust. Pressure relief valve setting: boiler rated pressure + 0.03MPa. 7, check the electrical contacts of the operation: When the pressure is raised to the maximum working pressure (not exceed the rated working pressure), should stop burning, open the safety valve blowing off steam, the pressure to a minimum operating pressure (maximum operating pressure is generally lowest set to 0.10MPa), combustion burner should be restarted. Note: When the adjustment screw should slow, especially when the pointer approaches the end, otherwise, damage the screw off the wire.
A industrial 5 ton fired steam boiler is an industrial boiler that heats water to a certain parameter and generates high-temperature steam. Water is heated into steam in the drum, and the furnace gives out heat, which is the principle of a steam boiler. Steam boiler belongs to special equipment. Boiler design, processing, manufacture, installation and use must be supervised by the technical supervision department. The user can only use the steam boiler by obtaining a certificate of use of the boiler. According to fuel (electricity, oil, gas), steam boiler can be divided into three types: electric steam boiler, fuel steam boiler and gas steam boiler. According to the structure, vertical steam boiler and horizontal steam boiler can be divided into small and medium steam boilers. Double-return vertical structure and large-scale steam boiler are mostly three-cycle horizontal structure. Steam boiler scale inhibitor is a composite product composed of organic phosphonic acid and polycarboxylic acid, which has high corrosion inhibition and scale inhibition. After washing the gas steam boiler, the water distribution tank becomes the water wall bottom box and the temperature resistance is very good, which can be effectively applied to the water treatment of the low pressure boiler. Gas-fired steam boilers are suitable for corrosion and scale inhibitors, as well as for seawater desalination, distillation and automobile water tanks. The use of scale inhibitors in steam boilers can effectively suppress copper tubes and carbon steel composite components in the process; anti-F E3, Cu 2 accelerates corrosion resistance. The scale inhibitor used in gas-fired steam boiler is the guarantee of the safety of the equipment, it can be easily removed completely and at the same time reduce, the operation is simple, safe and reliable. The scale inhibitor used in gas-fired steam boiler is simple, can be discharged after neutralization, safe and environmentally friendly. It can reduce the use of scale inhibitors to maintain the performance of gas-fired steam boilers, which is conducive to the direct use of users and regular cleaning and maintenance of gas-fired steam boilers, saving equipment maintenance costs. According to the specific operation conditions of gas-fired steam boiler, descaling is simplified and easy to install and operate.