Hot Water Boiler 10 Mw Coal
How to do when severe water shortages steam boiler? In the event of a loss in water sometimes makes fireman process steam boiler operation, in the end how to solve it? How do we analyze today with severe water shortages steam boiler? In the operation of the steam boiler process, generally there will be some of the most common failure, the most serious is the boiler water shortages, lack of water is the main cause improper operation fireman, a long time to leave their posts, not the normal water supply. When there is a serious lack of water, do not have an immediate psychological pressure water supply, this is not correct, because the furnace severe water shortages, the various components of horizontal steam boiler is already red, not water supply, must wait until the boiler temperature drop immediately down, square and feed water may access the various components is malfunctioning. The above is how to do when severe water shortages steam boilers and today I will introduce? Content. After nearly a year of research and development company to launch coal, oil, gas steam boiler, the boiler is the biggest feature of this inspection is not required, all operations are automated, and now the case in Anhui, Jilin, Shanxi, Jiangsu and Guangdong have my company's .
Exhaust gas temperature factors affect the efficiency of the boiler 1. High boilers (1) ring-shaped heating surface. A protective pot operation due to the heated area ash causing poor heat transfer. Secondly heating surface by erosion wear of the high temperature flue gas, resulting in good convection bank vent for taking soil pipe powder blocking manner with less number F, powder powder increases the number of block f will inevitably result in decreased heat transfer effect of the heating surface, the deterioration of the operating parameters. such that the exhaust gas temperature medium (2) bits leakage furnace, the burner burning roll. Wind refuse mud furnace, burner combustion burning material will travel in incomplete protection technology, resulting in frameshift flame, which led to the degree of BU smoke Mi (3) poor operating conditions. A secondary air must have appropriate warehouse Shan ratio during burning. Secondary air Diao large ring-shaped hold burning effect, will affect the wind. Powder mix. 2. boiler water quality factors is an important indicator of pot care, but also a very appropriate to link, the water quality directly affects the safe and economical operation of boiler protection, internal cleaning of the heating surface of each pier can add endothermic t, It will increase the efficiency of the care of the pot. Shanghai each newly installed boiler heating surfaces are clean, the indicators are good, heat transfer efficiency is higher. But with longer run time, the inside of the tube or bi or furring rights corrosion, resulting in decreased heat transfer efficiency, pot nursing efficiency drops, after scaling or corrosion deterioration. Pot can also cause over-temperature protection wall even Los iron . 3. mechanical incomplete Tanzania Heat loss if the twist burner for burning Yan basin, coal dust mixed into the retaining find not carried out, resulting in insufficient fuel you burn. Shan increase mechanical incomplete burning loss. On the other hand due to air leakage protection Mu. Mi will lead to reduced care. Shan burn rate of decline. Powder fire longer, is not conducive to coal combustion rate, resulting in an incomplete tender burn solid increase in losses. Division personnel to operate the operation level of the level 4. 0 operator is not high, not be reasonably performed with the wind, the rotation speed control discharge protection, timely cleaning, descaling, resulting worthy material is not completely burned proud. Long low thermal efficiency in the actual operation, often occurs due to the experience of the operating personnel, resulting in decreased operating efficiency of the unit, adjust the low level of security decline. 'On the other hand, there is a difference operator P forced cultural quality and the level of practical skills.
Gas boiler ignition failure divided into several categories? How to deal with? With the advance of coal to gas, gas boilers have been gradually replaced by coal-fired boiler, with a high market share. But gas boiler often encounter some problems, mainly gas-fired boilers can not be said today about the firing of several reasons. 1, a boiler ignition pressure is too high or too low, the range of no ignition. Solution: Check boiler pressure, to see whether the pressure within the pressure range of the ignition of the burner, can be operated in a control cabinet. 2, the boiler water level is too low, ultra-low water level below the boilers, automatic interlocking, burner misfire. Solution: Check the boiler water level is below the low water levels if the boiler. 3, the exhaust gas temperature is too high, automatic chain protection boiler, burner does not ignite. Solution: Check the boiler flue gas temperature, smoke to see if the shutdown temperature is higher than the boiler 4, the gas inlet pressure is too low or too high, the burner is not firing. Solution: Check the burner inlet gauge to see whether the pressure composite ignition pressure boiler 5, natural gas leaks, burner does not ignite. Processing Method: General burner comes with leak detection means may be self-monitoring. 6, a gas burner commissioning and unreasonable air distribution control, auto-off after burner ignition. Processing method: the ratio of gas and air not debugging, the inlet air is too large, the firing automatic fire 7, the boiler emergency stop switch is erroneous, misfire burner (boiler is not in operation) Processing Method: General this time all the features are not method used, can be self-monitoring. 8, own fault burner, burner ignition contact rod iron, programmer failure, warning lights flashing. Approach: this time do not operate their own troubleshooting, and quickly find the right service door.
The use of central heating hot water boiler 10 mw coal is the best choice for winter heating in northern China. Shanxi Province is located in Chang Darrow Heating Co., Ltd. mainly provides heating and post-service maintenance of heating equipment, heating clients involved in enterprises and institutions, office buildings, residential housing and a variety of commercial and other entertainment venues. With the wide blue sky covered Battle of the project, China's gradual increase in the proportion of heating for cleaning, heating, Ltd. Dalong Chang respond positively to the call of national policy, high pollution intensity wishing previously used, low thermal efficiency of coal-fired boiler to replace the traditional use hot water boiler clean fuel. After comparing many boiler manufacturers, choosing the optimal selection, determined and professional cooperation parties do fast boiler fuel boiler cleaning equipment. Providing a fast side 35 MW gas tube hot water boiler (SZS35-1.6-Y.Q) according to their actual needs.