2 t coal boiler
Steam 2 t coal boiler wear and electric test pump DSY Henan fast boiler's steam boiler small series with you about wear and DSY electric test pump wear is one common steam boiler heating surface defects, boiler heating surface is arranged in the boiler the furnace and the flue, in particular a heating surface in the steam boiler flue vertical tail, by the long brush smoke, soot in the flue gas so that the wall heating surface wear thinned, so that heat from the flue gas scouring wall ironed a phenomenon known as wear and tear. Flow rate, the concentration of soot in the flue gas and the hardness of the tube bundle arrangement such factors as the wear rate of the heating surface of the steam boiler and the flue gas is related to the flow rate of flue gas wherein the greatest impact on the wear of the heating surface. Experimentally measured, proportional to the cube of the wear rate of the heating surface tubes and the flue gas velocity, it is necessary to effectively control the flow rate of flue gas. Leakage of the furnace wall, a partial wall flue ash, convection heating surface partially severe slagging will cause a partial flue gas velocity is too large, so that the heating surface tubes local wear increased, further, when the soot blowers work failure, high pressure steam steam heating surface tube will blow erosion, so that the wall thinning. Heating surface tubes often wear area is: cool ash, burner, bullnose, and close to Manhole sootblowing waterwall tube aperture; a lower portion of the flue gas before the steering tube heating surface vertical chamber; vertical tail horizontal heating surface portion of the second row of three tubes of the flue, the lower portion of the second three tubes, tube support edge portion of the clip, close to the furnace wall side of the rows of tubes and the individual tubes and the like projecting tube rows. Heating surface wear reduction methods are: to reduce boiler load, reducing flue gas velocity; burning coal quality, reducing the content of fly ash in the boiler flue gas steam; change bundle arrangement, a staggered arrangement to the line arrangement; Clear slagging and blocking flue ash, flue gas flow area increases; leakage reduction furnace wall; the installation of a shoe or the spoiler like. Abrasion test on the electric pump plunger hole set DSY electric test checking pump plunger sleeve (1) Check the DSY type. If the pump DSY electric test has passed the test on sealing ST-990 or the tester 3,375,375, the plunger sleeve is available. If the leakage is large, it is necessary to replace the plunger and plunger sleeve. (2) using the burr, coke, and high-expansion magnifying glass to check the amount of deformation of the bore. When the metering orifice is damaged, DSY i.e. electric test pump is not working properly. Do not attempt to clean with a wire, plug, etc., should be cleaned with a solvent. (3) Check the fuel oil channel as well as choking loose plunger sleeve for cracks. (4) Check DSY electric test pump plunger sleeve surface endless belt black area and Degree how damage flatness. Some electric test pump head end of the barrel nozzle sump has been canceled. Henan is committed to fast boiler steam boiler manufacturing, product quality, reasonable prices and widespread industry praise, if you have any needs, please contact us!
Combined with China's various policies, both from an economic point of view or the point of view of environmental protection direction, to develop gas-fired 2 t coal boiler is a clear trend, fast boiler has a lot of experience in the boiler Case "coal to gas", after the transformation of gas boilers whether harmful emissions or fuel utilization, have significantly improved. Help your business better production needs of life.
To comprehensively promote the prevention of air pollution control work, steadily enhance the quality of atmospheric environment, located in the northern part of Heilongjiang Province held a mobilization meeting Sunwu out of small coal-fired 2 t coal boilers to May 7.
Conference announced the "2019 Sunwu urban area out of 10 tons of steam per hour and coal-fired boiler embodiment."
To promote the elimination of built-up area of small coal-fired boiler work, the relevant departments should strictly follow the higher level requirements, the investigation to find out the use of coal-fired boilers and urban planning area of built-up areas, with their own reality, do a good job to implement; should attach great importance to raise awareness, according to the embodiment and objectives, and take various measures to actively promote the complete phase-out of coal-fired boilers small task; to actively publicize the relevant policies, regulations and requirements to the boiler owners, guided by the responsibility to implement, clear time node . To seek truth from facts, objective science, policy guidance, strict enforcement of the principle, in order to reduce air pollution, improve air quality and protect people's health as the goal, according to the classification regulation, departmental interaction, Duocuobingju, the overall advancement of the process steps to form a government command , business differentiation, market-driven, effective supervision, public participation in new air pollution control mechanisms, to promote the phase-out of coal-fired boilers built-up urban area.
Note the use of an industrial 2 t coal boiler fan which 1, strengthen the operation and management, ban illegal operation. Industrial boiler drum fan up and running, there must be strict rules. The induced draft fan starts to be unloaded, non-load starting, particularly when the boiler stoked, flue gas temperature is too low, such as the induced draft fan starts with load (i.e., open the blower inlet damper or fully open), a current will start increased a lot, and start-up time is too long, the fan motor can overheat, overloading is likely to burn out; when the boiler (particularly pulverized coal) Jan-fire operation, pay attention to drums, fan's opening sequence, can not be reversed. I.e., first open fan, run for 10 minutes, and to exclude the furnace flue fouling or flammable gases, before the blower starts. If the first open blower, the induced draft fan, so that both the induced draft fan load is increased, so that the induced draft fan motor overheating burned, and the furnace may lead to explosion. 2, industrial boiler flue gas dust removal blowers take measures to regularly clean the flue, induced draft fan to improve the working environment. Dust removal equipment units to strengthen the dust removal operation and management, improve the efficiency of dust removal; no dust removal equipment units to time quantitative dosing into the boiler furnace special cleaning agents, and timely removal of fouling of the flue, the flue avoid clogging, the impeller damage accidents. 3, the impeller blade surface hardening treatment to improve the wear resistance of the blade. Since the large fan boiler drum conveying high temperature flue gas is about 200 ℃, the flue gas contains large amounts of fly ash, SO2 and other corrosive gases, badly worn fan blades, fan output prone to drop, vibration, such as rupture of the blade. Therefore, to deal with a serious face or wear parts of welding blades to improve the wear resistance of the blade. Use DC welder welding, arc welding using manual method using a dedicated fan hardfacing strip (e.g., wear No. 1, Mo-Cr-B carbide electrode wear, etc.), and the electrode wear in 300 ~ 350 ℃ drying 1 hour use. Before welding, the surface of the blade should be fouling, rust cleaned, preheated to 100 deg.] C, with a small current, low voltage, temperature and speed, short arc welding symmetry. Practice has proved that, after surfacing treated leaves, wear resistance greatly improved, not only changed the fan impeller often wear, but also laid a good foundation for the safe operation of the fan. 4, insist on Boiler Fan periodic overhaul, maintenance of strict quality control. Industrial boiler drum Fan to be overhauled on a regular basis. The elimination before the accident hidden danger in the bud, to overhaul a comprehensive, thorough, carefully check the wear, the impeller shaft and impeller balanced operation, with or without internal connections loose, collision, inlet baffle switch is flexible and bearing lubrication and cooling Happening.