Factory Price WNS Series 1 Ton Industrial Diesel Oil Boiler
Exhaust gas has been plagued by sewage paper industry, paper industry pollution problems of the country very seriously. Fujian Heng paper packaging company has been committed to the use of clean-type factory price wns series 1 ton industrial diesel boiler paper processing. October 22, 2016, David Carse, the paper with my company, signed a 6 tons of steam an integral condensing steam boiler for the production of corrugated cardboard and other paper products. I provided the boiler greatly solve the problem of sewage wastewater Heng paper. After the boiler operation, both to meet local environmental requirements, but also reduce operating costs for the constant boiler paper products.
How to prevent running back pass secondary combustion 1, 30% of the rated factory price wns series 1 ton industrial diesel boiler to deal with the amount of purge air before boiler ignition; the boiler must be 30% of rated air flow purge less than 5 minutes after the boiler fire, or allowed to boiler re-ignition. 2, fine-tuning the boiler and combustion systems pulverizing system operating conditions, to prevent incomplete combustion of oil and coal accumulating on the tail heating surface or flue. 3, boiler burning oil, adjust the proper air flow, fuel flow, confirming good gun oil spray, burning completely. If you find a bad oil spray gun should be discontinued immediately, and clean up. 4, when the oil application group administered powder, cast powder should be confirmed before the oil burner ignition good, or allowed to cast powder. 5, the oil powder boiler during cofiring, and check the fuel oil gun system of fire reinforcement. 6, normal operation, operation personnel in monitoring the economizer, an air preheater flue tobacco in different conditions of temperature, abnormal, should be checked to detect a fire-place. 7, air preheater sootblowing steam system normally put into operation, the soot-blowing pressure and temperature in a predetermined range. When the unit load or less prolonged 300MW kerosene mixed combustion, air preheater sootblowing steam to be continuous. 8, the air preheater into a reliable fire alarm device. 9, an air preheater inlet and outlet fume / air damper, and should be able to put an electric shutter can be open, closed tight. 10, if found preheater stall, should be put into operation again immediately, if not turn back, they should be isolated.
Oil and gas factory price wns series 1 ton industrial diesel boiler application
The fuel gas boilers produced by ZG boiler are selling well overseas, for a variety of reasons. Fuel gas boilers are generally fueled by natural gas, light oil, heavy oil, etc., which are commonly used in various countries. While ZG boiler has been in the boiler field for decades, with talents and experience, ZG boiler has a good brand reputation and quality products and services, which are deeply loved by customers.
How to improve the thermal efficiency of gas steam factory price wns series 1 ton industrial diesel boiler steam boiler to improve the thermal efficiency of gas is a problem many users are taken, I believe this issue is the direction of each used in the production of various types of gas steam boiler manufacturers have been in the study. Many users at the time of the gas-steam oven operates, often in the actual production process, we found some new problems, but all the problems, the most vexing is the high temperature exhaust gas steam boilers, thermal efficiency than low phenomenon that a serious impact on our work, then how should we do to improve the thermal efficiency of it? need to know this is the best way to meet the low-temperature properties of gas and steam comes as synthetic gas steam. However, the vast majority of synthetic gas and steam biphenyls, benzene derivatives of both components of the complex, or a vapor of volatiles has strong carcinogenicity, it is strongly recommended that the client select the type of mineral oil vapor product gas. Second, gas and steam products to meet the low temperature performance process, but also have a relatively high flash point required. In general, gas steam engineers suggest, low temperature gas steam flash point not lower than the opening 200 ℃. After a professional manufacturer of continuous research and improvement of its equipment, in order to improve its thermal efficiency was found to be increased tail gas steam boiler heating surface of, say, air preheater and economizer. But when organic heat carrier furnace return temperature is high, you can not set the economizer, air preheater can only be set to alleviate the situation. So if no gas steam boiler and other heating systems for low temperature heat exchanger, then the only way to improve the energy efficiency is adding air preheater. After adding air preheater can be a corresponding increase in gas flow rate of steam, gas steam boiler in order to ensure safe, reliable and stable work, the thermal efficiency of gas-steam boiler plant will be a corresponding with the increase.