best oil fired steam boiler for sale
Gas oil furnace fuel additive effect and the boiler room Notes: Gas oil furnace, oil furnace that is both in one, and, still in the boiler in this category, so, based on this, the following will continue be familiar with and understand the boiler, because it is the product website and keywords. Moreover, we can also derive some new knowledge, in turn, make progress and development in their learning path. 1. Gas oil furnace, which is a fuel additive, then what good? Gas conducting oil furnace, in which fuel additives, it is possible to optimize the fuel, and reducing soot and improving thermal efficiency. However, it should be noted that, in addition amount to control the well, in moderation, too much or too little, will always have problems, thereby, affecting the normal combustion of the fuel. 2. Gas-fired best fired steam boiler for sale and gas oil furnace, boiler room can both jointly built it? Gas-fired steam boiler and gas oil furnace, two boiler room, is jointly built, and that is no problem. However, it should be carried out in accordance with the steam boiler room equipment specifications and oil furnace room design specifications, avoid mistakes, and at the same time, to make the two boilers, a good use of effects.
Beiqi Panthers in the car to communicate with the company, expressed full confidence in our company, cooperation is very smooth. Since the boiler departure two years, our technical staff has been concerned about the relevant boiler operation through remote monitoring system to provide strong and stable technical support services for the Beijing auto Panthers. --customer feedback
Gas introduced gas best fired steam boiler for sale steam boiler stop sign Profile: natural gas steam boiler is a steam boiler gas, natural gas steam boiler with natural gas as fuel, the combustion in the furnace heat put out by heating the pot water, and allowed to vaporized into steam energy conversion device. Water pan (drum) is continuously released from the combustion of a gaseous fuel energy to heat the furnace temperature is increased and produce steam under pressure. Since the boiling point of water increases with increased pressure, the pot is sealed, the expansion of water vapor generated inside the pressure limited thermodynamic formed, strictly speaking, the steam boiler is heated in water at constant pressure saturated steam drum regasification water formed, is widely used as an energy source. Protection device: (1) protect the boiler water a boiler water level gauge plate supporting one to two, should always be compared with each other, inconsistent findings indicate that shall be corrected immediately. Class water level should be flushed, to determine their true level. While the water level comes electrode rod can accurately capture level signal to an alarm or a pump control. (2) steam pressure protection pressure controller: selection of high sensitivity of the pressure controller, the pressure is high, or low levels of signal to the electrical switches, other control lines or automatic control chain protection. Using pressure controllers and electrical contacts, the vapor pressure can overpressure alarm; single adjustable pressure controller or dual fire burning fire the actual operating pressure. Safety valve: safety valve is the last line of defense to protect the boiler, the boiler pressure exceeds the limit, according to the set pressure relief valve design with the school, the exhaust steam pressure relief, to ensure the normal operation of the boiler. (3) having a burner flame protection flame protection inlet means, combustion function is to detect, when the ignition failure or extinguish combustion middle, immediately off the burner into the oil (gas) solenoid valve, the blower continues to operate at this time, the furnace was purged combustible residual gas, after 20 to 30 seconds purge, and various auxiliary blowers automatically cut off power, the boiler operation stops. (4) self-locking power failure protection case, the boiler shutdown immediately burst self-locking power interruption, if the current power is restored, the boiler will not start at any time, you must reset release self-locking, to re-start the ignition. Editing boiler ignition procedures: 1. Check operation and (or) shift recording. 2, inspection, examination boiler, external. 3, check the main safety accessories. Safety valve, water gauge, pressure gauge, to be tight, reliable and sensitive. 4, check the water treatment equipment. 5, inspection equipment and soda water supply system pipe. Adjust the valves as required to start. 6. Check the oil supply equipment. After the above inspection qualified, you can start the boiler. Note: The boiler is a high-temperature, high-pressure thermal equipment, is one of special equipment, widely used in government agencies, public companies and all walks of life, it is dangerous and special equipment. Event of an accident involving public safety, it will cause huge losses to the state and people's lives and property. For public safety, people's lives and property safety, according to the State Council, "Regulations on Safety Supervision of Special Equipment", the boiler should use full attention the following matters: 1, should be accompanied by safety technical specifications of the factory boiler design documents, product quality certification, safety and the use and maintenance instructions, supervision and inspection certificate (safety supervision, inspection and performance certificate). 2, boiler installation, maintenance, alteration. Engaged in the installation of the boiler, maintenance, renovation of the unit shall obtain special equipment installation and maintenance certificates issued by the Provincial Quality and Technical Supervision, before engaging in the boiler installation, maintenance, alteration. Construction unit before construction will be prepared for installation, maintenance, alteration in writing inform the special equipment safety supervision and management department of the municipality or district, and will start informing sent to the local county level Quality and Technical Supervision for the record, told immediately after construction. 3, inspection of boiler installation, maintenance, transformation. After construction, the construction unit To State Quality and Technical Supervision of Special Equipment Inspection and hydrostatic testing of the boiler installation supervisory inspection declaration. After passing by the State Quality and Technical Supervision, State Special Equipment Inspection, County of Quality and Technical Supervision involved in overall acceptance. 4, registration boiler. After the boiler inspection, the use of units must be in accordance with the "special equipment registration and use of management rules", fill "boiler (census) Registration Form", the State Quality and Technical Supervision to register and obtain a "registration certificate to use special equipment safety . " 5, operation of the boiler. Boiler operation must be performed by trained and qualified to obtain "special equipment operator certificate" certified personnel to operate, must strictly abide by the rules and eight systems, six record. 6, check the boiler. Periodic inspection of boiler once a year, not be used without safety periodic inspection of boilers. Safety accessories safety valve of the boiler regular inspection once a year, pressure gauge biannually verified, may not be used without the periodic inspection of the safety accessories. 7, non-pressure boilers will be installed for the boiler pressure. Do not use water level gauge, safety valve, pressure gauge three safety accessories insufficiency boiler.
Three tempering tube hot water boiler installation and commissioning of the structure outlined hot water boiler is fast loading of the internal combustion level. A second high temperature flue gas successively washed roots and refluxed for three breathing tube, the smoke chamber into the atmosphere through the chimney. Gas hot water boiler equipped with the world famous burner, combustion using automatic adjustment, automatically adjust the water supply, the program starts, automatic control and other functions. The boiler has a compact, safe, reliable, easy to operate, installation speed, low pollution, low noise, high efficiency. Widely used in enterprises, hotels, hospitals, office buildings, civil construction and other industrial steam, life, mining and other facilities. This installation requires fast speed boiler installation, installation is very simple, the boiler does not require special ground base, only enough to withstand the ground to power. 1. Install the water supply line requires the highest level reservoir, generally not critical, the high from the ground to the reservoir tank, underground tank of water should be kept clean. Pool water outlet. For wire entrance filter water supply line. 2, the straight cross-section is mounted, the return pipe return pipe to be 0.5 meters above the bend radius should be 4 to 5 times the diameter of the pipe, the pipe should be installed at the highest automatic steam valve to prevent the steam from the pipe loop. At the same time, the general requirements of the highest level possible reliable reserve pool. When the boiler water level is below the line, the water will flow into the boiler when the next time you start. Filter wire 3 should be installed at the outlet (i.e., the inlet pipe) of the pool. Installation requires a supply line Burner fuel hose has two interfaces, and for the oil return into the oil, as long as the boiler return oil chamber and the oil corresponding feed pipe. Dedicated hydraulic system from the boiler tank to the burner pump port, an operation instruction for the burner 4 is provided. Chimney straight chimney installation requirements. The length of the chimney should not be too long, the stack height should be less than 5 meters. Chimney height should comply with relevant standards. Chimneys should be added raincap and smoke. Weight not directly on the boiler chimney host chimney 5, hydrostatic test shall be carried out after the installation of boiler water pressure test supervisor. Pressure test before proceeding to deal with internal boiler inspection, hydrostatic test pressure MPa, during hydrostatic testing, water pressure should slow down. When the pressure rises to 0.1MPa, the water pressure should be increased to 0.1MPa. When the ambient temperature is higher than 5C, hydrostatic test should be carried out; when the temperature is lower than 5, should be protected from freezing water pressure test. Hydrostatic test water is generally 20-70.6, should be as light fuel oil or gas oil (China) as the fuel, the fuel oil is generally heated to 100 deg.] C, a viscosity less 30E. Oil Qbw = 10200Kcal / kg LHV viscosity of the oil is lower than at 50 ℃ 200E, at less than about 80 ℃ 200E, 50e is less than the heat value of natural gas Qbw = 8550Kcal / kg LPG Qbw = 22000Kcal / kg.