6Th Coal Steam Boilers
Steam Boiler with different fuels can be divided into biomass boiler, coal fired boiler, gas fired boiler, oil fired boiler, etc.
Blue Sky Battle horn started, our country constantly walking on the green road. Reduce atmospheric emissions of nitrogen oxides, improve air quality, but also the people a blue sky, the industry has invested in the construction of environmental protection go, Guizhou Baiyun Quan Lake Hotel is no exception. As we all know, fast boiler R & D in the field of clean fuel boiler never stopped, through market research and screening, Guizhou Baiyun Quan Lake Hotel in October 2017 signed a low-nitrogen Thalia T5 series vacuum hot water and fast boiler boiler for hot water supply and heating the hotel.
Which Xining Xining industrial boilers industrial boilers looking to find Which? There are a lot of companies need to produce industrial boilers in Xining area, industrial boilers had previously been dominated by coal, but now the purchase of multi-boiler is gas-based. This is also in line with the requirements of the current environmental policy. For the procurement of industrial boiler business, then Xining region, for businesses can be compared within the boiler manufacturers nationwide. The company Xining After initial screening decision Xianxiang fast boiler manufacturers for consultation. In this regard, fast boiler manufacturers for the accounting data for the current production status of the enterprise Xining, concluded that the plant with 1 table 6 tons of industrial gas 6th coal steam boilers on it. Initially, the company for the transport of Xining boiler still have concerns, however, listened to a detailed introduction side boiler fast personnel of the relevant technology. Completely dispel concerns. At present, the price of the model of industrial steam boiler at around 720,000. Recently, the Xining to fast Boiler companies will conduct field investigation, will talk about specific issues related to time after purchase.
The heat loss of exhaust smoke is the largest of all kinds of heat loss in boiler. Generally, the heat loss of exhaust smoke is 6% of the heat fed into the furnace, and the heat loss of exhaust gas increases 0.5% when the temperature of exhaust gas increases by 12 ℃ and 15 ℃. So the exhaust temperature is one of the most important indicators of boiler operation. The following are several possible causes of increased flue gas temperature in the furnace: (1) slagging and ash accumulation on the heated surface. No matter it is the slag accumulation in the water-cooled wall of the furnace, or the ash deposition in the superheater, convection tube bundle, economizer and preheater, the thermal resistance of the flue gas measurement will increase, the cooling effect of the flue gas will become worse due to the deterioration of the heat transfer, and the exhaust temperature will rise. (2) excess air coefficient Big. Under normal conditions, the exhaust temperature increases with the increase of excess air coefficient at furnace outlet. After the increase of excess air coefficient, although the amount of smoke increased, the rate of smoke increased, and the convection heat increased, the increase of heat transfer was not as much as that of the increase of flue gas. It can be understood that after the increase of smoke speed, the flue gas leaves the heating surface without time to transfer heat to the working fluid. (3) the air leakage coefficient is too large. The flue gas leakage in the furnace and rear shaft of a negative pressure boiler is inevitable and the leakage coefficient allowed by a certain heating surface is specified. When the air leakage coefficient increases, the effect on the exhaust temperature is similar to that of the superheated air coefficient. And the air leaks away. The closer the furnace is, the greater the influence on the rise in exhaust temperature. (4) Water supply temperature. When the steam turbine load is too low or the high pressure heater is out of line, the feed water temperature of the boiler will be lowered. Generally speaking, if the fuel quantity is kept constant, the heat transfer temperature difference of the economizer decreases and the heat absorption of the economizer decreases when the feed water temperature is increased, which makes the exhaust temperature increase. (5) moisture in the fuel. The increase of moisture in the fuel increases the amount of smoke, thus increasing the exhaust temperature. (6) Boiler load. Although the boiler load increases proportionally, the amount of smoke, the amount of steam, the amount of water supplied, and the volume of air increase proportionally, however, the flue gas temperature at the furnace outlet increases proportionally. Increase, so that the exhaust temperature increased. After increasing the load, the outlet temperature of the furnace increases, the heat transfer temperature difference of the convection heating surface increases and the heat absorption increases. Therefore, the more the convection heating surface is, the less the influence of the boiler load on the exhaust gas temperature is. (7) fuel varieties. When the low calorific value gas is fired, the radiative heat transfer in the furnace decreases due to the decrease of furnace temperature, and the non-combustible components in low calorific value gas, mainly N _ 2, CO _ 2 and H _ 2O, increase the amount of flue gas, so the exhaust temperature increases. Although the excess air coefficient of furnace outlet is lower than that of coal burning, the ash content in the fuel oil is very low after the pulverized coal furnace is changed to burn oil, although the excess air coefficient at the furnace outlet is lower when burning oil. There is no larger ash particle in flue gas, and there is no cleaning effect of larger ash particle on the heating surface, and the convection heating surface is polluted more seriously. Therefore, combustion is not good, often smoke-emitting boiler smoke temperature rise. When there is a steel ball dust removal device at the tail, the exhaust temperature is slightly lower than that of burning coal because the tail is cleaner. (8) the operation mode of pulverizing system. For a closed pulverizing system with a silo, when the pulverizing system is in operation, as a part of the water in the fuel enters the furnace, the furnace temperature decreases and the flue gas increases, and the cold air leaking into the pulverizing system enters the furnace as a primary air during the operation of the pulverizing system. Reduction of air flow through air preheater To raise the exhaust temperature. On the contrary, when the pulverizing system is shut down, the exhaust temperature decreases.