Industry 1000 KW Gas fired Industrial Steam boiler
Coal-fired boilers to gas-fired boiler and the basic requirements of a program, the transformation of the basic requirements: 1, the boiler must be carried out in accordance with "Steam Boiler Safety Technology Supervision" and "Hot Water Boiler Safety Technology Supervision" and relevant national technical regulations, construction program should be sent to the local technical supervision departments for approval. 2, to determine the value in use based on the transformation of the boiler has the age and state of the art, taking into account the life expectancy of the boiler. If the boiler use a longer useful life, and the pressure there is a serious corrosion, scaling and overheating phenomena such elements, no transformation of value. 3, boiler walls, chimneys, water supply and air supply, the wind system should remain largely intact. 4, after the transformation of the original technical parameters should be kept constant boiler (operating pressure, temperature, etc.) or the load and to improve the efficiency of the original boiler. 5, after the boiler should comply with national environmental and technical indicators, solve the problem of smoke and dust, meet environmental requirements. 6, when the boiler should try not to change the original pot, and the body is pressed by the original system architecture, covers the smaller the better. 7, rehabilitation programs should be simple, low investment, short construction period and quick, safe and reliable. Second, the transformation method: 1, removal of the original coal-fired boiler slag machine, equipment on coal, dust, chain grate and gearbox. 2, according to the diameter and length of the flame, furnace installation height determining geometric dimensions and the burner. 3, making the furnace, the furnace bottom refractory brick, a semicircular shape. 4, the front arch openings mounted burner nozzle. 5, after that the flame away from the center position of the tube the arch, the arch of the pipe on the basis of the original slope, heightening baffle wall, the protective tube arch. 6, install blast doors. 7, install the induced draft fan drive. 8, the body of the boiler water test pressure 1.5 times the working pressure. 9, the automatic control system installed. Third, the technical proposal: 1, furnace design should consider the flame length and diameter of the flame of the combustion gas, so that the furnace space is filled with the best of the flame, the flame not Wall flush. 2, as the main component of natural gas CH4, H20 generated after combustion, steam share large, so that strong radiation, heating furnace suitably increased to take advantage of the radiation heat transfer, thermal efficiency, reduce the consumption of steel, ensure that the boiler output, and may increase the boiler output. 3, a slight positive pressure within the boiler furnace using a combustion or slightly negative pressure, the sealing performance of the boiler furnace walls to strengthen, not air leakage. 4, due to the smaller excess air ratio of the gas boiler, combustion requires less air flow, coupled with the removal of dust, dust and small flue system, the flue resistance is reduced, a large surplus primer fan flow, using file when the damper plate adjusting the power loss is large, frequency control can be induced draft fan air volume regulation. 5, after the furnace door and see the fire smoke chamber above the chimney, mounted two proof doors, in order to improve the antiknock performance of the boiler. 6, the boiler flue gas the volume of gas in the vapor component is generally 15% to 19%, well above the coal-fired boiler flue gases generated in the water vapor content of 6% by volume or less. Boiler shutdown and startup, due to the low wall temperature of the boiler heating element, when less than less 50 ℃, the flue gas water vapor dew condensation on the wall will, if not removed condensate with the condensate of the contact wall would be C02 acid gas corrosion of furnace wall and the insulation material due to water absorption and thermal insulation effect will be lost. Therefore, before and after the gas hot water boiler smoke box and the rear box and the rear flue smoke condensate discharge means to be provided, promptly boiler condensate removal. 7, the gas boiler-system control function should have combustion process. Pre-blowing may be implemented, auto-ignition, flame detector self-test, automatic load adjustment, flame monitoring, fault alarm interlock shutdown, the gas leak detection valve, induced draft fan and burner control sequential chain protection. 8, in order to prevent fluctuations in the gas pressure regulator to meet the burner requirements, the installation of a gas regulator metering panel outer gas inlet in the boiler room, the surge counter can be accomplished by filtration, regulating, metering, safety shut-off functions.
Which Xining Xining industrial boilers industrial boilers looking to find Which? There are a lot of companies need to produce industrial boilers in Xining area, industrial boilers had previously been dominated by coal, but now the purchase of multi-boiler is gas-based. This is also in line with the requirements of the current environmental policy. For the procurement of industrial boiler business, then Xining region, for businesses can be compared within the boiler manufacturers nationwide. The company Xining After initial screening decision Xianxiang fast boiler manufacturers for consultation. In this regard, fast boiler manufacturers for the accounting data for the current production status of the enterprise Xining, concluded that the plant with 1 table 6 tons of industrial gas industry 1000 kw fired industrial steam boiler on it. Initially, the company for the transport of Xining boiler still have concerns, however, listened to a detailed introduction side boiler fast personnel of the relevant technology. Completely dispel concerns. At present, the price of the model of industrial steam boiler at around 720,000. Recently, the Xining to fast Boiler companies will conduct field investigation, will talk about specific issues related to time after purchase.
We need boilers for central heating urgently. When it get cold, we need a lot of high pressure boilers for central heating. To meet your requirements, our ZG Boiler new type gas fired industry 1000 kw fired industrial steam boilers have launched to the global market. This WNS natural gas Fired Boiler adopts new technology developed by our ZG engineers. And this boiler adopts three pass design and spiral fin tube to enhance its heating efficiency. WNS series Condensing Boiler with Advanced technologies cooperated with German company are introduced into the WNS fire tube gas & oil fired steam boilers.
For the 2018-2019 autumn-winter air pollution prevention and control work, Jinhua City, Zhejiang Province issued a public draft, mainly in the autumn and winter to reduce heavy pollution weather Development frequency.
Take measures to reduce coal comprehensive, non-electric focused on reducing the total coal consumption, in 2018 the city's total coal consumption reduction of 1% compared with 2015. New non-owned coal-fired units, the implementation of new large-scale coal-fired units and coal consumption of the same amount of capacity reduction or substitution, elimination of energy consumption, water consumption, environmental protection and safety is not up to 300,000 kilowatts coal-fired units. Development of industrial parks "One District One heat source" action plan, and more than 300,000 kilowatts coal-fired units were heating transformation, promote backward and shutting down small coal-fired thermoelectric integration of coal-fired boilers in the range of 15 km radius of the heat. Optimize the use of natural gas structure, in principle, to new natural gas cogeneration and gas chemical projects, to the new "coal to gas" projects, should adhere to increase coal gas reduction synchronized to gas will change, the premise of the gas supply contract signed and orderly implementation.
Coal-fired boiler (with tea furnace, operating a stove, grain storage and drying equipment, coal-fired facilities) carried out an intensive investigation to ensure that no dead ends, no blind spot. Investigation and the coal-fired boilers to register one by one.
According to the law to increase the city's efforts to phase out coal-fired boilers in accordance with regulations. Before the end of December 2018, the city basically out of 10 tons of steam per hour of coal-fired boiler, built-up areas out of 35 tons of steam per hour coal-fired boilers. Complete 1 set (Yiwu) per hour, 40 tons of steam coal-fired boilers transformation of ultra-low emissions, coal-fired plants to achieve ultra-low emission levels.
In principle, the boiler NOx emission is not higher than 50 mg / m, and comply with appropriate safety boiler specification. New installation and reconstruction of gas-fired simultaneously supporting the low NOx combustion device.
Biomass boilers to carry out a comprehensive investigation, complete control of boiler scale, distribution, fuel, furnace, pollution control facilities and pollutant emissions, and establish a list of management accounting. Yan Gesheng biomass boiler registration, strictly control the new urban area of biomass boilers. Biomass boilers should be dedicated boiler, coal and other prohibited blended with other fuels, efficient dust bags and other ancillary facilities. Actively promote the urban area of biomass boilers ultra-low emissions transformation. For existing biomass boilers, environmental inspection carried out one by one, there are multiple distributed biomass boilers, the implementation of the demolition of small and large industrial agglomeration area.