Factory supplying oil steam boiler for sale
Combustion Adjustment of dual-use oil and gas boilers (Skills) boiler firing was successful, the load can be adjusted to normal operation. At this point, we should always observe the furnace combustion, if there is a bad oil and gas atomization, beating the flame, the flame hit the furnace and the exhaust gas temperature is too high or too low and so, it is timely for oil pressure, oil temperature, of steam, wind, air pressure, steam pressure hanging line adjustments to ensure safe and economic operation of the boiler. Size and load size of hydraulic, pneumatic boiler related to the oil pressure adjusted by adjusting the back pressure or fuel burner to achieve the size, by adjusting the air pressure to achieve the degree of opening of the valve. Adjust the amount of oil, air pressure adjustment load, at the same time, air volume control, must be synchronized to ensure a reasonable match of oil and the amount of wind, so as to achieve economic operation of the boiler. 1, the combustion method of determining boiler fuel gas: C02 content is determined from the flue gases and excess air ratio (1) the combustion quality (2) determines the length of the flame from the combustion quality (3) from the flame color and smoke color determination 2 is good or bad combustion, fuel combustion boiler adjustment method: the normal combustion, furnace flame stability was white orange, generally rumble, or if the flame beating abnormal sound, should adjust the fuel and air volume. If the adjusted still no improvement, it should identify the cause flameout, the measures to be taken and re-ignition.
Boiler plant equipment as three major important energy conversion device, fuel chemical energy into heat energy, and the pot was heated using thermal energy to become hot water having a sufficient quantity and a mass (steam temperature, steam pressure) steam turbine for use. The Anyang City, the power company to my company to buy a split 2 tons of steam condensing gas factory supplying steam boiler for sale for supplying electricity demand. The WNS series split condensing boilers using advanced technology designed to greatly improve the thermal efficiency of the boiler, up to about 96%.
Classification and characteristics of oil-fired boiler which when the weather gets colder, people will choose different heating methods, which have a more convenient way is oil-fired boiler, but many people do not understand his usefulness, then together below take a look. Category: oil-fired boiler is the practical use of fuel, the boiler various boiler with diesel fuel and waste oil, his overall construction and arrangement of the gas boiler is similar to a common classification of mechanical and steam materialized style. Features: Multi-Fuel bottom of the pot is made of the holding furnace bottom is inclined to the back wall for holding furnace bottom, in order to obtain good combustion characteristics. This is not the kind of boiler for the gas pipeline, also want to be able to lower the cost of the normal operation of the boiler, then oil-fired boiler is a good choice. Oil-fired boiler is an important sign of progress now era, the purpose is to serve humanity well, according to further improve the people's needs.
What problems should be paid attention to in maintenance Electric normal pressure Boiler
Nowadays, advanced electric atmospheric pressure boilers need to be used in industrial production as well as in daily life. However, the electric atmospheric pressure boiler is a highly operational mechatronics equipment, such as customer inspection, maintenance is not timely will result in equipment line aging, equipment oil circuit and oil pump wear and so on. Therefore, users need to pay attention to the maintenance of equipment when running boilers, then, what problems should users pay attention to in the maintenance of electric pressure boilers with good performance?
1, pay attention to stop furnace detection electric atmospheric pressure boiler in the maintenance, users should let the equipment according to the normal shutdown procedure operation to achieve slow cooling, at the same time, Users should use pot water circulation and furnace ventilation to gradually reduce the temperature in the pot and furnace. It is worth noting that when opening the door hole of the equipment, users need to pay attention to preventing the burning of steam, hot water and flue gas in the boiler.
2, note that when users maintain the insulation, the combustor and flue of the detected atmospheric pressure boiler should be separated from the total flue or the other running boiler flue. The test results are as follows: (1) the combustor and flue of the tested atmospheric pressure boiler should be separated from the main flue or other running boiler. And the flue gate should be closed tightly, and in the partition after ventilation. In addition, the blind plate used in equipment partition should have sufficient strength and hardness to avoid being bulged by high pressure medium in the operation of electric normal pressure boiler, and the partition position should be clearly indicated to avoid confusion.
3, note that the user must completely cut off the connection pipe between the vessel and the gas equipment, especially to the combustible and toxic medium equipment before the inspection of the atmospheric pressure vessel is carried out by the user of the equipment container. In addition, the equipment container not only needs to close the equipment valve, but also needs to use the blind plate of the equipment to close the valve so as to prevent the gas leakage into the container and cause the fire explosion or poisoning accident of the valve so as to cause the combustible or toxic gas to leak into the container.