5 Ton Vertical Small Steam Boiler
Heard so much about fast boiler made a number of achievements in the areas of clean boiler, this time my unit and quick cooperation parties, give me your company's boiler unit is in line with the requirements of our team boiler, to achieve a clean, energy-saving, environmentally friendly way of heating . Moreover, your company for the Beijing authorities have provided more office cleaning boilers, a good reputation. So, we finally reached a cooperation. --customer feedback
Appear normal operation of the 5 ton vertical small steam boiler problems and solutions advanced steam boiler steam boiler automatic controller, Chinese LCD screen, man-machine interface, users simply relaxing setting, the boiler is able to start and stop according to user requirements, load regulation, automatic water supply and other automated operations. Boiler fully functional, complete protection, easy to operate, safe, reliable, self-diagnostic function. Boiler operation anomalies automatically interrupt burning, audible alarm once appeared. Burner supplied by well-known manufacturers in the world, according to the automatic combustion controller instructions, stop, separate control box has a number of security, safety and stable performance, low maintenance. Boiler steam boiler problem during normal operation of the operation should be done in a balanced water supply, as far as possible to maintain the water level in the normal range. When load is large, there may be a false level. As the load sudden increase in water level may appear to rise and then fall phenomenon, and when the load dump occurs first decline and then rise phenomenon. Therefore, when monitoring and adjusting the water level, pay attention to judge this temporary false water level, in order to avoid misuse. And on the bottom of the lower drum outfall header drain valve mounted in series two, closer to the boiler of a header and a slow valve opening, the other for the quick opening valve discharge should slowly open the valve to open, after ajar quick opening valve, after full preheating pipe. For better results the sewage, can switch several quick open valve. After discharge, turn off the quick opening valve, then slowly open the valve is closed, and finally open about fast opening valve between two valves to put water in the net. Sewage Note: ① first furnace before the sewage water is adjusted to higher than normal water levels to strictly monitor the water level of sewage, to prevent the boiler water shortage due to pollution caused. From time to time between the sewage, sewage pipes by hand after touching drain valve drain valve to test for leaks, such as feeling hot, indicating the drain valve leaks, the reasons should be identified to eliminate them. ② the spirit of diligence row, row less, the principle of uniform rows, each class sewage at least once, all the sewage outfall have to take turns, to prevent the deterioration of water quality and sewage pipes clogged furnace, and even cause damage to the water cycle and tube rupture. ③ sewage to perform the normal operating pressure in a low load. At this boiling pot of water to ease, easy to slag sewage sedimentation, sewage good effect. ④ discharge switch operation should be repeated several times, relying on reverse impact force from the slag dirt stirring, then concentrate is discharged, so that good discharge effect.
Low cost CFB boiler for bagasse
Because CFB Boiler fuel (and desulfurizing agent) is combusted repeatedly at low temperature with desulfurization reactions under the fluidized bed condition, it is a new generation of multiple-effect, low pollution, clean combustion boiler. bagasse fired boilers are commonly used to heat water and create steam for energy production. Bagasse-fired CFB boiler efficiency can often provide lower operating costs.
So, how to select the relevant parameters?
1. Make sure you are using steam boilers or hot water boilers, hot water boilers and then determine its power, usually expressed in kilowatts.
2, determine civil or industrial use, and then focus on the outlet pressure, small outlet pressure outlet pressure boilers civilian use than industrial.
3, according to site selection range, the size of the boiler selection. Nameplate pressure gas hot water boiler is in accordance with the national standard, the actual operating pressure gas hot water boiler is determined by the operating pressure of the circulating pump, generally below its nameplate pressure.