3000kg heavy oil steam boiler manufacturer
Gas boiler Burner Failures and gas boiler burners Failures and - best ￼ a gas boiler, gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer. Second, gas boiler, but spark ignition rods misfire reasons: 1, the cyclone disc space ventilation is blocked carbon, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Measures are: Clear; first wash, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel); Check tubing and oil filters, insulation equipment ; remove peripheral screw pump, carefully remove the cover inside out oil network, with immersion oil; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing instability reasons: 1, the air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, fuel oil boiler water. Action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; approximately set to about 50 deg.] C; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Processing methods: ① the oil line check valve is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.
oil and gas 3000kg steam boiler manufacturer for textile
zbg is one well known boiler manufacturer with 70 years boiler manufacturing history and produced various kinds of boilers, autoclaves and boiler accessories.
There are many types of power plant boiler such as biomass power plant boiler, gas power plant boiler, oil power plant boiler, CFB power plant boiler and so on. However, when comes to the term of cost, coal fired power plant boiler is the most popular either in developed countries or in developing countries. Zimbabwe is rich in coal reserves and it has 30 billion tons of coal in 21 known deposits that could last for over 100 years, therefore, the coal fired 3000kg steam boiler manufacturer in power plant has earned great popularity in Zimbabwe.
Heating and hot water daily is an important basis for maintaining the northern region of the normal operation of enterprises; for Legal Daily organs and units, the hot water boiler is one of the indispensable energy equipment. Currently, work is facing north Heating equipment and facilities aging, increase energy conservation and environmental protection requirements and other issues. Daily logistics-related legal person responsible for improving the overall level of heating units, and the response advocated by the national energy saving, plans to purchase energy-efficient heating boiler. Considering the increasingly stringent environmental policy, Legal Daily authorities decided to use natural gas as boiler fuel. Fast boiler for 20 years, specializing in the production brand boiler, which had been successfully assisted more than Beijing enterprises and institutions, to provide clean heating. The party technical consultant fast boiler based on actual usage Legal Daily units, providing commercial condensing units 99KW vertical 1 hot water boiler.