Heating Coal Steam Normal Pressure Fire Tube Boiler For Sale
Response to national environmental policy in recent years, Changzhi City, various enterprises and institutions from themselves, have the heating coal steam normal pressure fire tube boiler for sale environmental transformation and selection. However, due to various boiler plant manufacturers of products of varying quality, there is a variety of security risks in the operation; taking into account the level of professional fireman some units of non-compliance, the boiler operating procedures less skilled, the above reasons, Changzhi City Special inspection at this year's "safety month" held gas boiler safety planning activities of technical training courses, the city's use of gas-fired boiler units represent 233 enterprises and safety training. Fast boiler has a strong position in the field of clean-type gas boilers, and has a wealth of experience. Changzhi City, the special prosecutor of the special fast Boiler training for each unit represents.
Horizontal steam heating coal steam normal pressure fire tube boiler for sale accident treatment method: 1 overpressure accident boiler, boiler overpressure phenomenon of (1) a sharp rise in steam pressure, the pressure exceeds the allowable working pressure gauge pointer over the "red line" safety valve operating pressure is still elevated. (2) the operation of the device is the interlock overpressure protection, should send overpressure alarm signal, stops the air blowing, the wind, coal. (3) steam temperature and steam flow rate reduction increases. 2, to treat boiler overpressure (1) weakened rapidly burning, manually open the valve or bleed valve. (2) increase the water supply, while the lower reinforcing blowdown drum (It should be noted at this time to maintain the normal water level of the boiler), in order to reduce the temperature of the boiler water, thereby reducing the pressure in the boiler drum. (3) as a safety valve malfunction or all of the pressure gauge damage, emergency shutdown, safety valves and pressure gauges are to be repaired after the boost operation. When endanger the safe operation of (4) Boiler excessive pressure, blood pressure should take measures, but too fast buck is strictly prohibited. (5) boiler overpressure eliminate serious, to the shutdown of the boiler internal and external inspection, to eliminate the overpressure caused by deformation, leakage and other safety accessories and maintenance unqualified. 1, the phenomenon of the boiler water (1) below the minimum safe water level line, or no visible water, the water table glass (plate) as a white. (2) as a full-color water level gauge vapor instruction color. Low water level alarm signal (3) water level alarm occurs. (4) low water interlocking means, the water level should be below a prescribed value blower, Fan, grate reduction motor stops running. (5) a sharp rise in the superheater steam temperature, higher than the outlet steam temperature. (6) boiler exhaust gas temperature rises. (7) the water flow is less than the steam flow, causing Should the water tube due to tube cracking or economizer, an opposite phenomenon occurs. (8) When a serious water shortage, can smell the burnt smell. (9) When a serious shortage, the door can be seen from the red-hot waterwall tubes. (10) a serious water shortage, the furnace tube may rupture, then can hear the explosions, smoke and steam from the door, watching spray the fire door.
About six tons of steam heating coal steam normal pressure fire tube boiler for sale shutdown of a temporary shutdown: It is planned, therefore slow cooling during shutdown protection device, it should also pay attention to safety, pause furnace according to the rules in Chapter IV Fenghuo (pressure fire) get on. 2, safety shutdown: care should be completely stopped even on normal operation plan for 1 to 3 months to be a shutdown, shutdown should maintain more safety injection apparatus, after the shutdown, and other water-cooled furnace to below 70 ℃ when they let go of the gas, open manholes, hand holes, rinse the pot with water scale. 3, emergency shutdown: the boiler operation, when the case of the following circumstances, should an emergency shutdown, and notify the relevant authorities. (1) expanding the cease-fire should first see if the water table level is called to take water law. If Inception water table, water cock side, and then close the steam cock, and then turn on the water faucet open and close repeatedly called after water, still can not see the water. (2) All water supply equipment failure. (3) All water gauge, pressure gauge, safety one of all the failures. (4) a boiler or furnace wall element damage, serious threat to the safe operation of the boiler, emergency shutdown, should focus on preventing the stop of the accident and the specific steps as follows: ① first blowing off; ② the coal on the grate red raking; ③ Close induced draft fan.
ZG Boiler can supply oil & gas fired steam heating coal steam normal pressure fire tube boiler for sale, coal fired steam boiler, biomass fired steam boiler, CFB steam boiler, waste heat steam boiler to paper mill. However, biomass fired steam boiler is the most suitable one for paper mill.