horizontal coal fired steam boilers used for industrial
Blue Sky Battle horn started, our country constantly walking on the green road. Reduce atmospheric emissions of nitrogen oxides, improve air quality, but also the people a blue sky, the industry has invested in the construction of environmental protection go, Guizhou Baiyun Quan Lake Hotel is no exception. As we all know, fast boiler R & D in the field of clean fuel boiler never stopped, through market research and screening, Guizhou Baiyun Quan Lake Hotel in October 2017 signed a low-nitrogen Thalia T5 series vacuum hot water and fast boiler boiler for hot water supply and heating the hotel.
SZL coal fired chain greate horizontal coal fired steam boilers used for industrial for sale
Coal fired boiler design features:
1.By adopting of double wings gas ducts, the fuel gas can go into the front gas tank easily, so the temperature of different front plates can be same. In this way, it can avoid the crackles happening in the plates.
2.Spiral tubes are installed in the drums, which can strengthen the heating transferring efficiency, at the same time, spiral tubes have the ability of dust removal, which can avoid the dust stratification in the tubes.
3.Both of the front and the back arches of the 10t/h series coal fired boiler design adopt mason work of water cool tubes wall structure, which can form permanent arches.
4.Separate adjustable wind chambers. Wind is feed from two sides. It adopts new type crank screw wind adjustment structure, so that the wind adjustment and ventilation cross section proportion is 100%, which can ensure the easy wind adjustment and make it symmetrically.
5.There is push-pull damper dust removal equipment. The damper adopt finish machining cast iron seal structure, thus the secondary combustion distortion and air leaking in the grate is effectively prevented.
Learning materials heat boiler 1, the boiler is three safety accessories: water gauge, pressure gauge, safety valve. 2, the normal operation of the boiler water level is 0 ± 40mmH2O, the maximum does not exceed 0 ± 80mmH2O, the normal water pressure of 5.5MPa, to allow the fluctuation range of 4.5-6.0MPa, normal pressure boiler feed water temperature should be 105 degrees Celsius. 3, steam flow is not larger than the normal water boiler feedwater flow reasons, the measuring device instrument to do so. 4, the steam flow rate is less than the abnormal overheating damage reasons of water flow, water wall damage, damage to the economizer, the boiler is full of water, measuring device instrument to do so. 5, points on the furnace process CCP washed three times water gauge, pressures of 0.05-0.1MPa, 1.0MPa, 2.8MPa. 6, it is determined whether the normal water table and put into operation to see if the water level fluctuates slightly exemplar. 7, the boiler water pressure test and the test is divided into P overpressure test of two, when the water pressure P test, the boosting speed of not more than 0.35MPa 0.5MPa down rate does not exceed per minute. To the boiler water blowdown 8, the pressure in the boiler shutdown boiler water temperature drops below 80 degrees Celsius. 9, the position of each ordinary pressure test is hydrophobic doors: a door opening, the second door is closed. 10, the boiler-burner with a swirling-type and DC type two. 11, elemental analysis of coal with a composition: C, H, O, N, S, moisture, ash. 12, the main component of the blast furnace gas is: CO.'S time, nitrogen gas, blast furnace gas pressure is lower than 1500Pa, the user must reduce the amount of gas. Fire stop its pressure 1000Pa, working pressure 4000-8000Pa, the upper limit for the dangerous pressure 10000Pa, the lower limit is 2000Pa. 13, the main component of the coke oven gas: CO, nitrogen gas, coke oven gas pressure is lower than 1500Pa, must reduce the amount of gas, which pressure is 500Pa fire stop, working pressure 5000-7000Pa, the upper limit is 8000 Pa pressure the risk, the lower limit is 1500Pa . 14, the high, the main features of coke oven gas is flammable, explosive, toxic. 15, proximate analysis of coal with a volatile content, fixed carbon, ash and moisture. 16, boiler water circulation loop fault has stagnated, cycling back down the tube vaporization, soft drinks stratification. 17, the pulverized coal burning furnace radiation heat from a heat source of flame, high temperature flue gas convection heat. 18, the pulverized coal ignition and quick combustion conditions are sufficiently high temperature furnace, a sufficient amount of air mixed well, pulverized coal and air. Enough burn time. 19, ignition of pulverized coal into the combustion stage, the combustion stage, burning ember stage. 20, boiler mechanical rolling bearing does not exceed a predetermined temperature 80 degrees Celsius, the slide bearing does not exceed 40 degrees Celsius. 21, with factors affecting the steam load boiler water, boiler water salinity, pressure change, the vapor space of the drum height. 22, the principle of the steam separator drum gravity separation, inertial separation, centrifugal separation, separation of the water film. 23, the first ignition of the pulverized coal volatiles, fixed carbon is the latest ignition, the combustion of carbon is the longest. 24, steam soluble salt contaminated steam quality reasons, mechanical carryover. 25, the normal operation of the boiler drum water level in the glass tube than the water level high 50MM, when the water level in the steam table overall door leak, the water level high water table, the total gate leakage when the water level is low. 26, a method for enhancing heat transfer with a heat transfer coefficient is increased, raising the average temperature difference between the heat transfer, the heat transfer area is increased. 27, into the boiler furnace wall refractory layer, three-layer insulating layer and the sealing layer. 28, light blue flame blast furnace gas, as a bright golden yellow flame co-firing light yellow flame, coal, coke oven gas when the combustion gas as a combustion time. 29, the boiler by the "pot" and "furnace" composition, "pan" refers to a soft drink system is mainly composed of the drum, the downcomer, the header, waterwall, economizer, superheater composition; "oven" refers to a combustion system, a furnace, a burner, an air preheater composition. Calorific value 3.27GJ 30,1 tons of steam.
Problematic fired boiler (1) Henan small boiler gas boiler should be noted, by the Henan coal into gas boiler, i.e. the original becomes a negative pressure is now slightly positive pressure combustion burner, the furnace must be noted that the structure and the sealing wall problem; (2) prevent explosion of the furnace, a gas fired boiler furnace to Henan, when defective or incomplete combustion of fuel atomization gas in the furnace or heating surface of the end aggregate, fire or explosion occurs, and therefore, in appropriate sites shall boiler explosion vent means, while the control program should be added to the ignition and flame protection device of automatic control, to ensure safe operation of the boiler; (3) the selection and arrangement of the burner close to the furnace in the form of, should the flame in the furnace better fullness without forming dead air; adjacent flame of the burner to avoid mutual interference; low load flame holding in the furnace central position, offset from the center of the furnace to avoid the flame center of symmetry; unburned gas-air mixture is not in contact with the heated surface , to avoid the formation of incomplete combustion gases; hot flame to avoid high-speed heating surface erosion, in order to avoid excessive heating surface so that the wall strength of overheating. Burner arrangement also consider the gas pipe and duct arrangement, easy to operate, inspection and maintenance; (4) Mechanized layered coal-fired boiler, gas boiler to change Henan, first removing its longitudinal arch, taking into account the increase in the bottom heating surface to replace the grate, grate to prevent overheating burn; (5) gas velocity Henan convection heating surface is not limited by the gas boiler ash abrasion conditions, gas velocity can be increased properly, so the convection heat transfer heating surface coefficient increases, without increasing the heating surface of the boiler, can increase the pressure of the boiler, steam-water separation capability should be noted that at this time means the pot to ensure the quality of steam, hot air for the boiler had particularly important.