6 tph 1 25 mp coal fired steam boiler
How to avoid the food processing enterprises boiler water pollution? How to avoid the food processing enterprises boiler water pollution? How to avoid the food processing enterprises boiler water pollution? It is well known in the food production process, many sectors need to use boilers, such as cooking, faced with the problem of sewage treatment, also with a certain level sterilization, dry, wine and so on. In the country's growing emphasis on environmental protection, continue to increase supervision of enterprises under the enterprise adoption of what approach to avoiding disadvantages, complete sustainable development? Primary, flue gas collection equipment processing equipment. Since SMEs by financial constraints, skills, and other places, a time can not be cut all the transformation, it is possible, after passing through the coal-fired boiler exhaust gas purifying exhaust purification device tail device, such as a fume hood, an exhaust gas collection processing device, effectively to prevent the direct discharge of black smoke, a serious impact on the surrounding environment. Second, clean power conversion, such as coal gas, coal to electricity. I learned that a beer factory invested more than 10 million will replace all coal-fired boilers, gas-fired. Now, 180 tons of 6 tph 1 25 mp coal fired steam boiler plant now farewell all coal, burning a low nitrogen gas cleaning switch, effectively reduce pollution. And compared with previous coal-fired boilers, coal saving more than 80,000 tons per year business.
Beijing SL Pharmaceutical Co., Ltd. as China's key high-tech enterprises, has great influence in the pharmaceutical industry. In early 2017, two-Heron relevant person in charge to get in touch fast boiler, double-Heron Pharmaceutical according to demand, our company to provide a 1-ton split steam condensing 6 tph 1 25 mp coal fired steam boiler, and is responsible for subsequent transportation, installation and commissioning work .
Run chemical plant boiler problems that may arise is what chemical plant boiler operation possible problem is? There are two main chemical plant boiler evaporation: evaporation and rated maximum continuous evaporation. When the chemical plant boiler load is higher than the maximum continuous evaporation, it indicates the operating force or overload. The following problems may occur super-load operation: Main results are as follows: (1) due to increased fuel consumption, furnace volume heat load increases, the furnace temperature and furnace flue gas outlet temperature, resulting in the superheater and reheater the superheated steam temperature and wall temperature, and must therefore be strictly monitored and adjusted. Try not to let this time overheating. Coal furnace, furnace volume due to the increased thermal load, increasing the likelihood of slagging. (2) the flow rate of chemical evaporation apparatus system working fluid increases, the flow resistance is increased, it is not conducive to water circulation. Therefore, we should pay particular attention to the monitoring of the water cycle bad area. (3) the pressure differential between the drum and the superheater outlet flow increases as the working fluid and superheater flow resistance increases, so that the pressure of the steam drum and headers increases, the strength of these components must be considered . Space volume load (4) the steam drum, the load increases the evaporation surface, saturated with water vapor would increase, thus affecting the quality of steam. (5) chemical plant boiler safety valve Total displacement designed according to a maximum continuous evaporation. If the chemical plant boiler overload, once the sudden load shedding, the safety valve will not fully open, the steam pressure can not be reduced quickly. At this point, it is necessary to ensure the safety of the boiler by chemical vapor released into the air exhaust valve. (6) With the increase of the amount of air required for combustion and the amount of smoke produced, once sufficient air supply, the air volume is insufficient, the chemical conditions affecting the combustion boiler, increasing the likelihood of slagging; In addition, since the flue gas velocity the increase in fly ash increased the degree of wear of the heating surface. (7) during operation, the exhaust gas temperature rises, the exhaust gas heat loss; shorter residence time in the furnace the fuel, incomplete combustion heat loss of mechanical and chemical incomplete combustion to increase the heat loss, reduce the thermal efficiency of the chemical plant boilers. In summary, the excess chemical plant boiler operation have an adverse impact on the security and economic, should generally not excessive run. If the special emergency must also be strictly limited scope and excess power beyond the time required to force.
Steam boiler wear and electric test pump DSY Henan fast boiler's 6 tph 1 25 mp coal fired steam boiler small series with you about wear and DSY electric test pump wear is one common steam boiler heating surface defects, boiler heating surface is arranged in the boiler the furnace and the flue, in particular a heating surface in the steam boiler flue vertical tail, by the long brush smoke, soot in the flue gas so that the wall heating surface wear thinned, so that heat from the flue gas scouring wall ironed a phenomenon known as wear and tear. Flow rate, the concentration of soot in the flue gas and the hardness of the tube bundle arrangement such factors as the wear rate of the heating surface of the steam boiler and the flue gas is related to the flow rate of flue gas wherein the greatest impact on the wear of the heating surface. Experimentally measured, proportional to the cube of the wear rate of the heating surface tubes and the flue gas velocity, it is necessary to effectively control the flow rate of flue gas. Leakage of the furnace wall, a partial wall flue ash, convection heating surface partially severe slagging will cause a partial flue gas velocity is too large, so that the heating surface tubes local wear increased, further, when the soot blowers work failure, high pressure steam steam heating surface tube will blow erosion, so that the wall thinning. Heating surface tubes often wear area is: cool ash, burner, bullnose, and close to Manhole sootblowing waterwall tube aperture; a lower portion of the flue gas before the steering tube heating surface vertical chamber; vertical tail horizontal heating surface portion of the second row of three tubes of the flue, the lower portion of the second three tubes, tube support edge portion of the clip, close to the furnace wall side of the rows of tubes and the individual tubes and the like projecting tube rows. Heating surface wear reduction methods are: to reduce boiler load, reducing flue gas velocity; burning coal quality, reducing the content of fly ash in the boiler flue gas steam; change bundle arrangement, a staggered arrangement to the line arrangement; Clear slagging and blocking flue ash, flue gas flow area increases; leakage reduction furnace wall; the installation of a shoe or the spoiler like. Abrasion test on the electric pump plunger hole set DSY electric test checking pump plunger sleeve (1) Check the DSY type. If the pump DSY electric test has passed the test on sealing ST-990 or the tester 3,375,375, the plunger sleeve is available. If the leakage is large, it is necessary to replace the plunger and plunger sleeve. (2) using the burr, coke, and high-expansion magnifying glass to check the amount of deformation of the bore. When the metering orifice is damaged, DSY i.e. electric test pump is not working properly. Do not attempt to clean with a wire, plug, etc., should be cleaned with a solvent. (3) Check the fuel oil channel as well as choking loose plunger sleeve for cracks. (4) Check DSY electric test pump plunger sleeve surface endless belt black area and Degree how damage flatness. Some electric test pump head end of the barrel nozzle sump has been canceled. Henan is committed to fast boiler steam boiler manufacturing, product quality, reasonable prices and widespread industry praise, if you have any needs, please contact us!