wood fired generators boiler
Hot water wood fired generators boiler vaporization problem the whole solution 1, hot water boiler steam boiler of the phenomenon (1) boiler and pressure suddenly increased safety valve starts to emerge from the water and steam in the expansion tank. (2) the impact of sound water boiler, pipes to vibrate. Impact or the like occurs in the water (3) circulatory system piping. (4) a sharp rise in the temperature of boiler water, over-temperature signal overtemperature alarm occurs. 2, because (1) hot water boiler pot all the water vaporization operator negligence or misuse. Such as forced circulation hot water systems, at startup, the first boiler ignition, after the circulation pump. When shutdown, stop circulation pump, after stopping the boiler operation; or storage of fuel and heat in the boiler does not distribute all do, eager to stop the circulation pump is running and so grossly erroneous operation. (2) the occurrence of circulating hot water boiler outage, improper handling. (3) hot water boiler circulation system or severe leakage, device malfunction or constant pressure, causing a sudden drop in pressure in the boiler. This situation occurs mainly in the high-temperature hot water boilers. (4) cyclic interrupt occurs, although the boiler immediately stop running, but the remaining fuel in the combustion chamber and heat storage water vapor of the pan. This usually heat storage capacity in the furnace, the occurrence of a small pot of water volume of hot water boiler. (5) stop the pump sudden power failure or failure of the circulation pump. (6) the temperature of the hot water boiler, the pressure indicating instrument malfunction, resulting in erroneous judgment. 3, the reason the hot water boiler local vaporized boiler water (1) within the reservoir portion of the tube boiler scale or debris, the local destruction of the boiler water cycle. (2) a boiler structure unreasonable or undesirable combustion conditions, resulting in the line between the parallel deviation is too large heat boiler or boiler water uneven flow distribution, resulting in local overheating vaporized. Local and overall circulation circuit (3) can not form a natural circulation boiler, causing local overheating of vaporized water circulation circuit occurs once the pump stops and the like. 4, treatment of hot water boiler steam boiler (1) stops running hot water boiler. (2) Check the hot water boiler and heating cycle causes vaporization system, and processed. (3) hot water boiler and hot water heating system natural circulation loop, loop back to the natural valve open road. (4) When a sudden power failure, the pump stops running, stopping in the boiler water cycle (forced circulation boiler), the temperature of the boiler water continues to rise due to heat accumulation surface of the combustion chamber of the boiler water to steam, because of a large water capacity If handled properly, usually does not cause accidents pot of water vapor. For hot water boiler tube DC (most of this is domestically produced boilers), because of its small water capacity, when a sudden power failure stop the pump, resulting in more accidents pot of water vapor. Hot water boiler should have suddenly prevent or mitigate the pot of water vapor measures to stop the pump during a power outage. China is now using more is to add water to the boiler and the boiler outlet slow release of steam, the pot of water on the one hand to maintain liquidity, on the other hand reduce the water temperature, up until the elimination of the combustion chamber of the regenerator. Some install the spare circulation pump driven by the internal combustion engine, when a sudden power failure, start the engine, but poor when asked to take into account, because the engine is not instantaneous will be able to start. There is provided a self-standby power supply or generator.
Opening the water supply valve motor, regenerative electric closing valve, a pressure pump to start the cycle frequency control constant voltage supply, electric wood fired generators boiler starts after about 30 seconds, in such a manner direct supply water to the user. At the end of the water supply, stop circulating pressure pump, electric boiler stops after 60 seconds. When the water reaches the time period, the electric power boiler feed water valve is open, regenerative electric valve is closed, the electric boiler is not working, the circulation pump frequency control water supply pressure. Electric power supply period of boiler feed water valve has been closed, not to pay it to avoid the cold water supply to the user. If the heat storage tank and the temperature is below the set temperature in the regenerator period of 5 ° C, pressure circulation pump into operation again, electric boiler start working after 30 seconds.
Thermal power plant wood fired generators boilers provide steam to turbine generator, including boiler and ancillary equipment. The fuel in the boiler furnace release heat energy after combustion, so that the heat be transferred to water in the boiler through the metal wall into the superheated steam with a certain pressure and temperature, and then fed the steam to turbine, the steam turbine drive generator to generate power.
Still 8 cultural and creative industrial park is located in the Chaoyang District, Beijing, Bali Zhuang Chen Lin, No. 2, construction area of 493,300 square meters. Surrounded by quintessence of Court, Red Sandalwood Museum, Shanxi Museum and other famous attractions. Due to its special geographical location, has very stringent requirements for providing heat wood fired generators boiler plants. Carefully selected to finalize cooperation with our company, signed a two He Lide series complete condensation pressure hot water boiler.