Low Price 2 Ton Combi gas Fired Steam Boiler For Paper Making
Industrial gas boilers small volume itself, and these need not be equipped with auxiliary equipment, simply set up between a host and auxiliary room, set on more messy, covering economy. Industrial gas boiler city gas source is generally taken from the intermediate pressure gas supply line, the gas pipeline laying gas sampling point to the boiler room, then according to quell's brand, type and caliber regulating device applications, scheduling outlet pressure range, by metering the put into use. Establish a set fee just gas network tariffs, pipeline fees, hot walks pipeline fee. Gas pipeline network overall cost of capital is the sum of the gas company funds charged to the user, can be determined depending on the circumstances around the gas company. Usually adopted buried gas pipeline type, buried depth is generally about 0.8m ~ 1.0m, seamless steel pipe can be selected or PE pipes, pipe surrounding sand 15cm ~ 20cm plating, hot water pipe laying relatively simple, somewhat messy steam pipe walks . 3, industrial gas boiler room planning results in the presence of 3.1. Selection of the size of the heat load of the boiler and its expansion tend to choose the boiler capacity, the number of great links. The larger heat load, single boiler capacity should be large. The near future can be greatly increased thermal load, is also relatively large capacity boiler can choose, it will expand the load thought. The only thought to increase the long-term thermal load, the expansion device may leave the boiler placeholder deployment end in the boiler room, or space left on the total FIG. However, in the practice of project planning, often there is a lack of expansion heat load estimates, constitute improper boiler selection, pre-operation to cause unnecessary trouble. 3.2. Gas boiler gas regulator trivial results generally used in high-pressure (less than 5kPa) and medium voltage (5 ~ 150kPa) trivial. Gas usually before entering the boiler room will arrive this requirement. Now the gas hot water boiler is equipped with a high level of automation subsided, a calm requires the gas pressure is lower, so before further demand into a calm pace pressure boiler manufacturers themselves generally equipped. Gas pressure regulating trivial demands reliable equipment, but on the size of the gas pipeline valve is open due to the gas pressure when scheduling the gas pressure is high or low, and tempering will cause off, start and stop frequently subsided's configuration, thereby affecting the boiler work. 3.3. Gas boiler quality results planning standard gauge, the quality can not be ensured when the gas, should be provided or dust, oil and water, respectively, and a total closed drain valve before the gas main pipe before the regulator device. Most of the oil production plant in the use of oil with anger, it is often said of moisture in the summer cold weather, moisture and light hydrocarbons and other substances containing moisture, condensation will constitute a line blockage, an initiative to quell the flame, impact Heating. 3.4. Chimney condensate results because of the high thermal efficiency of industrial gas boiler, a low exhaust gas temperature, typically 180 degrees, the boiler room planning criteria (GB50041-2008) rules industrial gas boiler room chimney should be reinforced concrete or steel chimneys chimney. Chimney will appear directly in the outdoor summer steel chimney condensate freezing results, constitute icing light rusty steel chimney, would constitute a temporary corrosion, freezing severe affect chimney smoke. 3.5. The amount of air to quell the outcome's when quell Industrial gas boiler is in the boiler room, the air between the boiler must be satisfied the requirements apply to quell the device, otherwise there will be no abundant natural gas to quell working carbon monoxide poisoning.
Hefei Limin Pharmaceutical Co., Ltd. Nanjing Military Region, formerly the backbone of pharmaceutical companies, the main drug is slowly swallow rather teabag, relying on advanced R & D platform to carry out contract manufacturing, OEM OEM and other business cooperation. China's environmental protection development trend began to take shape, many environmental policies have been put forward for a positive response to the national environmental policy, Limin Pharmaceutical decided to introduce a gas station low price 2 ton combi fired steam boiler for paper makings. After an investigation of the boiler market, Limin Pharmaceutical fast boiler is strong comprehensive strength and wealth of experience working for many years in the pharmaceutical industry to attract, party fast according to the actual needs of customers for its recommendation of one of Taiwan 4 tons of steam condensate gas-fired steam boiler (WNS4-1.25-YQ).
Different natural gas low price 2 ton combi fired steam boiler for paper making energy-saving measures as well as gas-fired boiler with environmental issues become more critical, more and more people are concerned about the importance of the environment for our development. Today, gas steam boilers in industrial production is very common, how to reduce the energy consumption of gas steam boilers, which we have been explored. We can take the following measures in natural gas steam boiler operation for energy. 1, the amount of steam needed for industrial production of a reasonable choice, and the number of the rated power station boiler steam boiler gas, in both cases the higher the degree of matching with the actual exhaust gas loss is smaller, the obvious energy saving. 2, the fuel in contact with air: fuel amount so that an appropriate amount of air and the optimum composition ratio of combustion, this would both improve fuel combustion efficiency and reducing emissions of polluting gases, energy to achieve the dual goals. 3, reducing the temperature of the exhaust gas steam boiler: the temperature of the boiler flue gas to reduce the effective use of exhaust heat generated in general, the efficiency of the boiler used is 85-88%, the exhaust gas temperature is 220-230 ℃. If the setting of energy-using the exhaust heat or the like, the exhaust gas temperature falls to 140-150 deg.] C, the boiler efficiency can be increased to 90-93%. 4, recycle heat from the boiler blowdown water: water using continuous blowdown heat by heat exchange, in addition to improving water temperature itching water to achieve energy saving gas steam boiler. At the same time, measures energy-saving gas steam boiler can also be reasonably recovered condensate heating system, and the heat of the condensate water recycling. It is different from the gas boiler and gas boiler: 1. Gas circulating fluidized bed combustion boiler coal by crushing device by the belt into the coal bin, by using multicast coal stoker wind, thrown into the furnace; circulating ash by heating, fluidized combustion process. After coal to gas and coke oven gas and purge gas mixed together by the four burners directly injected into the combustor. 2. Combustion of Coal is mainly composed of water and ash content and the elements C, H, O, N, S etc., the heat released by combustion of coal to produce SO2, SO3, NOx ash and moisture, and SO2, SO3, NOx discharged from the flue gas the atmosphere, pollute the environment, cause harm to humans. And the main component of coke oven gas and purge gas are CO and H2, after combustion, produce mainly CO2 and H2O, SO2 emissions relative gas boiler gas boiler, SO3, NOx is much less. 3. Usually ventilation negative pressure combustion gas boiler, the combustion process is to group together to complete the mating with the mating blower and induced draft fan, the coal combustion process, requires a lot of air and the furnace wall due to the leakage of the flue, the excess air coefficient of up to between 2.1-2.5. Gas boiler combustion slightly positive or slightly negative pressure, a small amount of wind required, air is preferably premixed with the gas within the combustor. No leakage factor positive pressure combustion flue and the furnace wall, the flue outlet air ratio operation may 1.05-1.2.4. Fuel explosive gas boiler combustion safety, the furnace explosion hazard unlikely to occur. The gas-fired boiler in the explosive concentration limits encountered fire will explode. More dangerous. 5. Gas boiler control difficult due to coal boiler, material thickness, amount of the blowing, the amount of the wind, the wind mixture ratio of coal and other reasons, to be automatically adjusted according to the operating parameters of the boiler load is large. Less impact on the factors of the gas boiler, the burner may be adjusted according to the size of the load valve, easy to achieve automatic control.
The main reason gas low price 2 ton combi fired steam boiler for paper making produces smoke which fuel gas steam boiler main cause of smoke. A fuel gas steam boiler: oil, gas oil quality is not good when the gas contains more water, reduce the heat value of the fuel, while producing steam, the furnace temperature tends to decrease, making it difficult to burn, easy to produce smoke. Water and more oil, mainly when unloading rain water into the oil during heating the oil in water vapor penetration. When the oil contains impurities, the impurities unburned produce fine coke, the coke into fine smoke, dust becomes large, and the formation of soot. Impurities contained in the oil and gas, but also affect the pure oil and pure combustion gas generated soot. Oil impurities, mainly due to inappropriate choice of filters or filter difference impurity removal effect. Second, the failure of the fuel atomizing nozzle member main burner fuel oil atomizing nozzle. Atomizing oil burner nozzle fails, affecting the quality of the atomization, easy to poor combustion. 1, the adhesiveness between the bonding surface of the oil and the consequences of failure oil atomizers swirl atomizers and the splitter plate well, leakage will occur, atomized large oil particles, increasing the amount of fuel injection and the like. In this case serious deterioration of the quality of the combustion, the oil droplets have landed on the water wall, stacking up oil coke, partially unburned black smoke into droplets. The tangential swirl chip groove clogging mist causes uneven density distribution in the dense side of the oil mist, combustion air be insufficient. In the more dilute side of the oil mist, combustion air causes severe local excess. Mixed with oil, wind conditions deteriorated significantly, combustion conditions deteriorate, resulting in black smoke. 2, spray atomization slice failure and the consequences of failure to clogging and wear. Nozzle clogging, resulting in blockage of the fuel injection quantity is not glib increase, oil particle size thicker, the effect of fuel poor and black smoke. Wear injection port, a large hole diameter, increasing the amount of fuel injection, increasing the particle size of oil affect combustion efficiency, produce black smoke. The use of artificial gas burner, naphthalene and tar and other impurities will block the nozzles, the influence of gas distribution, resulting in black smoke. Should therefore be cleaned regularly, or clogging of the selected burner. 3, the partition partitioning poor poor, insufficient supply of air into and excess. The amount of air can not meet the requirements of the fuel combustion, so that combustion of fuel can not be sufficiently black smoke. The amount of air, will result in lower combustion temperature, black smoke and fuel difficult to burn. 4, the furnace temperature is too low when starting the furnace, fuel oil steam boiler furnace temperature is too low due to easy black smoke. 5, the furnace hearth product oil is sometimes caused by internal combustion nozzle oil accumulated inside the chamber, the oil reservoir coke black smoke at high temperature. Causes dripping of fuel combustion nozzle: ① The drip just work, just at the operating pressure is too low, the oil will flow from the nozzle, instead of the discharge. The reason for low oil pressure is a solenoid valve, the valve is clogged filter or the like or failure caused by contamination. ② In the dripping process work, probably because the relative position of burner nozzle mounting head too far, improper ignition electrode position, the oil into the atomizer, the nozzle holder is mounted is not tight, nozzle dirty, low oil pressure caused. ③ When the dripping stopped, because the line between the pump and the air nozzle, electromagnetic valve or a hydraulic valve or dirty failure. 6, the furnace flue purged countless consequences when the furnace flue remnants of oil and gas, when gas purging endless, high temperatures encountered in the explosion and black smoke. 7, the furnace smoke, sparks, the furnace pressure is too ①; ② inappropriate choice of the burner, the burner flame is too long or too much power; ③ improper combustion ratio, there are more to produce products of incomplete combustion; ④ atomization quality is not good nozzle or improper installation location, or affect the combustion flame into the furnace off port; ⑤ flue is blocked, poor smoke; ⑥ a secondary air mismatches; irrational ⑦ furnace structure; ⑧ oil spray angle is selected from with improper.