Szl Series Water Tube Coal Boiler
How to improve the energy efficiency of industrial szl series water tube coal boilers 1, focusing on the transformation of practicality (1) above to recover waste heat can be effectively used. For example: high temperature organic heat boiler flue gas, but the process does not require the production of steam and hot water, attention should be considered heated by flue gas waste heat recovery techniques combustion air. (2) improved gas boiler should focus on energy-saving technologies improve the automation level of combustion control, precise control of the combustion state. (3) Consider first the application of energy-saving technologies and sophisticated equipment. 2, considering the technical nature to further improve the thermal efficiency of industrial boilers, it is necessary to consider new energy-saving technologies and equipment. Advanced (1) energy conservation technology and equipment, difficult to implement. Such as: waste heat recovery heat exchanger and the new technology: heat pipe technology, the condensed waste heat recovery technology; new water treatment device: microbial fouling and electromagnetic processing techniques (e.g., hydraulics); combustion automatic control technology. (2) spraying pulverized coal combustion technology (stratified combustion mode and suspension-fired boilers) design, construction and operation of high demand management, oxyfuel technology, such as high temperature air combustion technologies require large investments. 3, forming a complete transformation handle (1) must be considered boiler energy saving, heat insulation of synchronization is complete, sealing, and improved methods of burning fuel adjustment, and the fuel air distribution system of the inverter, reduced nicotinamide tube improved resistance to treatment. (2) pay attention to clean the boiler heating surface, and providing technical improvements boiler water, slag, ash, etc., to ensure that the boiler has good heat transfer properties. (3) the necessary training for technical operations and daily management of energy-saving equipment.
Industrial szl series water tube coal boilers and heating boilers What is the difference? Industrial boiler product in two ways, one steam used to generate electricity or gas, such as steam vaporized available fertilizer plant, coal as raw material, synthetic fertilizers, which is typical of industrial boilers, coal-fired industrial boilers still account for a large most gas is generally waste heat boiler for recovering waste heat. Industrial boilers commonly circulating fluidized bed boiler industrial boiler thermal power equipment is important, our country is today the world's largest production and use of boilers country. China's manufacturing industry is established and developed after the founding of New China. The term "industrial boiler" in the late 1930s, with the boiler thermal power generating units with capacity increasing, in order to distinguish high-capacity power plant boiler gradually adopted. Modern large-scale industrial boilers evaporation capacity has reached 100 to 200 tons / hour. Industrial boiler structure type in the structure can be divided into fire cartridge type, water and fire tube type 3 class. ① fire tube boilers; it is an early boilers, fire tube containing only water in the boiler twelve heating pot shell fire cylinder combustion means. Low thermal efficiency, large volume and steel consumption, since substantially no production 60s. ② fire tube boiler: it is in the vertical or horizontal potshell in addition to the fire tube, a plurality of means further smoke tube. The fuel in the combustion chamber high temperature flue gas produced after combustion smoke flows through these pipes heating pot of water, and then discharged into the chimney. Compared with fire tube boiler, since it is the number of multi-smoke tube, heated area increases, the exhaust gas temperature is low, high thermal efficiency, and the consumption of steel are relatively small volume of the boiler. FIG. 1 is a horizontal tempering tube boiler. When evaporation fire tube boiler is generally not more than 15 t /, working pressure not greater than 1.6 MPa, the thermal efficiency of coal is generally about 70%, of all oil-fired boiler automatic operation, the thermal efficiency can reach 85%. ③ water tube boilers: mostly used for larger capacity, higher pressure industrial boilers. Water tube boiler has a natural circulation type and DC two. Natural circulation water tube boiler with a single drum and double drum and other structures. Figure 2 is a double drum water tube boiler. Such boilers generally disposed in the convection tube economizer, an air preheater and sometimes, in order to reduce exhaust gas temperature. When coal efficiency up to 80% higher when the fuel. No drum DC industrial boilers, and the tubing coiled behind the inner wall of the furnace tubes of the convection heating surface composition. From the end of the tube into the water supply, the steam output from the other end. Industrial boilers small current, typically with separator and automatic control devices. The fuel and fuel combustion equipment is widely used in variety of industrial boilers, coal (bituminous coal, anthracite, lignite and coal waste, etc.), oil (heavy oil, residual oil and diesel, etc.), gas (natural gas or various industrial by-product gas) plant and urban waste (wood, bagasse, black liquor and waste, etc.) and so on. Therefore, industrial boiler combustion equipment is also varied. There layer belongs chain grate combustion apparatus, the feed grate, reciprocating grate, vibrating grate, chain grate stoker plus the like (see grate). Also useful way of fluidized bed combustion (see boiling furnace). In the evaporation of 65 t / h coal-fired industrial or larger capacity boilers generally use coal. Heating boilers boiler belongs to the category of civilian life, as people's safety awareness, and after 2000 are based on building heating hot water as heat medium, it does not allow the use of steam boilers, so in general we are talking about heating boilers often refers to pressure hot water boiler. There are many types of heating boilers, their classification is mainly divided in accordance with the fuel type, fuel heating boilers can be divided according to the different electric heating boiler, oil heating boiler, gas heating boilers, coal-fired heating boilers, biomass heating boilers. Which includes fuel: diesel, kerosene and heavy oil; which includes gas: Natural gas, LPG, city gas and biogas.
Blue Sky Battle horn started, our country constantly walking on the green road. Reduce atmospheric emissions of nitrogen oxides, improve air quality, but also the people a blue sky, the industry has invested in the construction of environmental protection go, Guizhou Baiyun Quan Lake Hotel is no exception. As we all know, fast szl series water tube coal boiler R & D in the field of clean fuel boiler never stopped, through market research and screening, Guizhou Baiyun Quan Lake Hotel in October 2017 signed a low-nitrogen Thalia T5 series vacuum hot water and fast boiler boiler for hot water supply and heating the hotel.
The method of adjusting the temperature of the superheated steam heating stove have? The method of adjusting the temperature of the superheated steam heating stove have? DC szl series water tube coal boiler steam temperature is mainly adjusted by adjusting the quantity of fuel to water. In actual operation, because the efficiency of boiler feed water and fuel heat enthalpy (depends on the water temperature) and the like will change, so the actual boiler operation to ensure the water-fuel ratio of the exact value is not easy. Coal-fired furnace will fluctuate because of the amount of coal and the amount of fuel due to the steam temperature. So, except DC boiler fuel to water ratio as the coarse adjustment means, but also must be used as a method of spray desuperheater means of fine-tuning adjustment. There is also some boiler flue gas recirculation, dampers and methods of the swing center of the flame as an auxiliary adjusting device.