1 ton gas fired steam boiler for industrial use
Boiler multiple protection: (1) the integration of boiler water level to protect water level and boiler design, the appearance of more compact appearance, accurately show the actual water level in the boiler body function. Coupled with dual independent electronic water level control system to achieve ultra-low water level in the boiler, low water level automatic adjustment function, the normal water level, high water level, ensure that the boiler in a variety of unforeseen circumstances foolproof, secure home. (2) steam pressure protection ☆ pressure controller: selection of high sensitivity of the pressure controller, the pressure is high, or low levels of signal to the electrical switch, other control lines or automatic control chain protection. Common pressure controller and pressure gauge, vapor pressure overpressure alarm can cut off the burner limit is reached; the pressure controller may be single or double fire burning fire the actual operating pressure regulator. ☆ safety valve: safety valve is the last line of defense to protect the boiler, the boiler pressure exceeds the limit, according to the set pressure relief valve design with the school, the exhaust steam pressure relief, to ensure the normal operation of the boiler. (3) having a burner flame protection flame protection inlet means, combustion function is to detect, when the ignition failure or extinguish combustion middle, immediately off the burner into the oil (gas) solenoid valve, the blower continues to operate at this time, the furnace was purged combustible residual gas, after 20 to 30 seconds purge, and various auxiliary blowers automatically cut off power, the boiler operation stops. (4) self-locking power failure protection case, the boiler shutdown immediately burst self-locking power interruption, if the current power is restored, the boiler will not start at any time, you must reset release self-locking, to re-start the ignition.
Pressure boiler furnace designed to fully consider the characteristics of the fuel pressure boilers body member are two main drum and furnace. Also known as the furnace combustion chamber, fuel combustion for space. The solid fuel on to the grate, referred to as a fire bed combustion furnace Stoker, also known as fire bed furnace; solid fuel furnace liquid, gas or pulverized, is injected into the combustion chamber is called the fire chamber burner, also known as the furnace fire chamber; air coal particles burn hold it was boiling, and the furnace is inferior fuel suitable for combustion is called fluidized bed furnace, also called fluidized bed furnace; coal particles so that an air flow rotated at high speed, and strongly called fire cylindrical cyclone furnace hearth. The overall structure of pressure boilers and boiler auxiliary equipment including two parts. Boiler furnace, drum, burner, water wall superheater, economizer, air preheater, and the furnace wall, etc. The main frame member constituting the core part of the steam production, called boiler. Furnace design needs to fully consider the characteristics of the fuel used. Each boiler should be fueled with the original design of the fuel. Boilers running economy and reliability are likely to vary greatly reduced when using the characteristics of fuel combustion. And the natural circulation drum is repeatedly forced circulation boiler receiving feedwater to the economizer, the coupling cycle and supplying saturated steam superheater cylindrical vessel. Simplified drum made from high quality steel plate, is one of the heaviest components of the boiler.
Innovation is the fruits of their labors in a timely manner to protect them, the group also set up a patent Group, to build the company's model workers Innovation Studio. By the end of 2017, the company applied for by the State Intellectual Property in standardization work, the establishment of a patent technology management platform. Industrial enterprises wang-wang, the city industrial prosperous and strong. Fast boiler threw himself into the path of innovation and intellectual development in the areas of clean fuel boilers, boiler industry forward to promote the development and enhance the overall strength of Anyang City, make yourself a contribution. Right now, fast boiler being saved enough strength, stir live a pond, in a move by chasing new road.
After electric 1 ton fired steam boiler for industrial use shutdown, how maintenance? When long-term disabled electric steam boiler, furnace should pay great attention to external corrosion and maintenance problems. First, after power shutdown cooling steam boiler, the ash must be thoroughly cleaned and the heating surface fouling the upper grate, the lower portion of the furnace. Then to maintain a certain degree of natural ventilation flue. In general, in order desiccant moisture should be placed in the furnace, flue. The quicklime as a drying agent, within the furnace or flue gas per cubic meter should be placed generally about 3kg. After placing all the ventilation should be tightly closed doors. After the change of lime powder to be replaced. Low-lying position as boiler room, ground during shutdown severe flood tide, often approach should be used and placed a small fire to dry desiccant combination. If the boiler shutdown a long time, after the complete removal of soot coated with an anti-corrosion red lead paint in oil or other metal surface furnace. As for anti-corrosion maintenance methods inside the furnace shutdown, the shutdown Yaoan the length of time to be. In general, no more than one month shutdown maintenance wet available, more than one month should be taken to maintain dry. To note the following problems when a dry maintenance: desiccant boiler not in direct contact with the metal surface, may be mounted in a container such as the iron plate after the desiccant is placed, and a hole for shutting the other hand hole cover, valve steam, the water pipe change must cut lime powder should be replaced.