Horizontal Type Coal Boiler Hot Water Boiler Central Heating Boiler
Fuxin City, Liaoning Province, Liaoning provincial government to respond positively to national policies according to the latest requirements, increase the intensity of atmospheric pollutants have increased in terms of the number of personnel or subsidies. Now funds raised 24.08 million yuan to support the removal of loose coal and coal-fired boiler control project.
According to statistics, since the fall of 2017, a total removal of Fuxin coal-fired boilers 488 units, a total of 1020.085 tons of steam, subsidies for 21.08 million yuan. At the same time, actively carry out the bulk coal Fuxin treatment project, the replacement of energy-saving small boilers 2,000 subsidy capital of 300 million yuan.
And, Fuxin City, developed a series of measures to scrutiny. To strengthen the management of special funds to ensure the flow of funds security, Fuxin City, the boiler license, inspection report and environmental impact assessment procedures to establish a furnace of a file basic information, to complete the formalities boiler users comply with the removal of subsidies standards, timely payment of subsidies to users hands.
After the implementation of removal of loose coal and coal-fired boiler control project implementation, Fuxin City air quality of the environment and the urban fringe have been greatly improved. According to the survey, this year, the average concentration of PM2.5 Fuxin City 35 micrograms / cubic meter, improved 12.5% year on year; PM10 average concentration of 67 micrograms / cubic meter, improved 17.8% year on year; air quality compliance rate of 81.6%, an increase of 4 %.
Henan how boiler manufacturers mainly clean gas boiler Henan boiler manufacturers boiler after a long run, the inevitable emergence of scale, the problem of corrosion, boiler manufacturers Henan boiler scale formation in water having a hardness of a composition, high temperature and high pressure after concentration continuous evaporation, a series of physical and chemical reactions in the furnace, the final formation of hard, dense scale on the heating surface, resulting in reduced heat transfer and the effect of corrosion under the scale factors, can cause Henan boiler waterwall boiler manufacturers endothermic reduction furnace, furnace outlet temperature of the boiler is increased, so that an increased loss of Henan boiler manufacturers boiler. While the effect of reducing the fouling of heat transfer within the water wall, the tube wall temperature may lead to increased lead Wall Wall squib, Henan Effect of boiler manufacturers safe operation of the boiler. Scale is "detrimental of the first" boiler, the boiler is the main cause of accidents, the danger main problems: wasting a lot of fuel: Because only one of very few steel thermal conductivity of scale, so when the heating surface fouling will transfer hindered, in order to maintain a certain boiler output Henan boiler manufacturers, it is necessary to increase the temperature of the side of the fire, so that the external radiation and flue gas heat loss. Now can be used efficient and environmentally non-corrosive cleaning agent for cleaning the gas boiler, so that the exposed metal tube device primaries, and to reduce biological fouling of algae because silt impact. At the same time stripping the role of iron oxide and iron oxide Asia, extended gas boiler service life, reduce energy consumption and improve productivity. Henan the maintenance of the boiler gas boiler manufacturers: 1, Henan boiler manufacturers during operation of the gas boiler the following points should be noted: (1) Henan boiler manufacturers do not allow pressurized gas boiler furnace combustion or smoke, plus easy to burn because coal hole covers. Not on the bottom of the water (2) Gas boiler ground surface to prevent moisture corrosion. 2, operation of the gas boiler boiler factory in Henan every 2-3 weeks, should be checked once. 3, run gas boiler boiler factory in Henan every 3-6 months after the shutdown should conduct a comprehensive inspection. (1) on the inside and outside gas boiler inspection, such as pressure welds, corroded steel inside and outside part of the phenomenon, if found should be repaired in a serious flaw, if the defect is not serious next time also to be shutdown to repair, if found when there is suspicious, but does not affect safety, records should be made for future reference. (2) can be checked and the water boiler primer coating to prevent corrosion.
Be careful when selecting pressure horizontal type coal boiler hot water boiler central heating boiler which cold days, just use pressure hot water boiler can feel as warm spring, enjoy the convenience of hot water. Extra large hot water boiler quality of life greatly improved. Pressure hot water boiler easy to use, but at the time of purchase the user must also confused how to buy, so the need to pay attention to what needs to select pressure hot water boiler For detailed understanding of. 1, when determining the use of boiler pressure hot water boiler purchase, you should consider using a different environmental requirements. If the client needs heating, you should choose a dedicated pressure hot water boiler is heated by circulating hot water in the hot water pump recycling. Back to the radiator, i.e. a heat sink, to deliver heat to every corner; hot water only, select a particular hot water, hot water circulating through the pump, hot water tank of hot water circulating in the hot water supply; number of users need to have two choices, so they have to choose to increase the heat exchanger in the piping system, so using two atmospheric pressure hot water boiler. 2, the heating area is determined, the amount of water by the calculation cycle, the required amount of hot water, boiler design used to determine the heating area or field. Accurate and scientific calculation and design can meet the requirements, without wasting resources. 3, to determine the fuel, boiler pressure hot water boiler style, coal or natural gas hot water boiler in three common, the boiler is electricity, gas hot water boiler coal or natural gas as an energy source. When selected, you can choose your own needs or favorable conditions. As long as meet the requirements of the boiler room, the style of choice should be simple and suitable for horizontal or vertical.
You have to know the energy consumption of boiler problems (flue gas oxygen content) 1, reasons 1.1 boiler leakage problems may increase the furnace exit of excess air ratio. 1.2 preheater leakage large. 1.3 or coal boiler load changes, wind, dust adjustment is not timely. 1.4 auxiliary burner throttle opening degree command deviations. 1.5 burner type, operation mode unreasonable. 1.6 determine the optimum boiler oxygen value is not accurate. 1.7 oxygen inaccurate measurements. 2, measures to address the problem of operational measures 2.1 2.1.1 Check to see if the fire door, be sure to close tight. 2.1.2 appropriate control the furnace pressure, amount of air leakage reduction furnace. 2.1.3 boiler load, when the quality variation, adjusting one, two air flow to maintain the optimal oxygen amount boiler control value. 2.1.4 maintain the normal water level in the water seal bottom, bottom to reduce the amount of air leakage. 2.2 carry out leakage test and damper characteristics before and after the test boiler maintenance routine maintenance and testing 2.2.1. 2.2.2 adjusted to optimize the combustion tests, the optimum value of oxygen boilers. 2.2.3 regularly test the air preheater leakage, provide the basis for air leakage control. 2.2.4 Periodic calibration of oxygen measuring devices to ensure the accuracy of measurement. 2.2.5 timely check and adjust the position of Flue Gas baffle system (such as: an auxiliary burner class inspection throttle opening degree, etc.), the identify problems in time. 2.3 2.3.1 downtime and a wear liner release duct, deformation, cracks, wear inspection process. 2.3.2 flue pressure test done to check the tightness of handling the leaking part. 2.3.3 flue damper position, the opening degree of chipping, deformation, loose seal, astringent card check process. 2.3.4 corrected assist air and the fuel damper flap opening position. 2.3.5 boiler, air preheater Leakage leak plugging. 126.96.36.199 boiler: furnace wall, roof sealing, see the fire holes, Manhole, bottom sealing plate is deformed, corrosion and tank leakage inspection process. 188.8.131.52 air preheater seal gap measurement adjustment, the deformation of the sector plate and curved plate, wear control check, the sealing gap adjustment mechanism inspection process. 2.4 2.4.1 transformation and a duct liner wear loose, deformation, cracks, wear inspection process, replacement, and a bluff body concentrator ceramic sheet, and silicon carbide wear measures. 2.4.2 boiler, air preheater, leakage leak plugging treatment. 2.4.3 the internal structure and the sealing means to transform the preheater, reducing air leakage. 2.4.4 boiler, flue joints and other advanced seal plastic material, to reduce leakage.