low price gas fired hot water boiler
This szs series boiler is an oil and gas water tube boiler that uses natural gas as fuel. The boiler has adopted a low-nitrogen technology, a low-nitrogen burner, and a condensing recovery waste heat device. It is a low-nitrogen condensing boiler produced by CBM.
What are the indicators of factors affecting the efficiency of the steam boiler Shandong? State basically in full swing during the move from coal to natural gas, low price fired hot water boiler with greatly minus the fine dust contamination, together with nitrogen oxides and other harmful gas emissions have been manipulated. Power is an important goal of measuring target hot water boiler, give you a look behind the cause of a direct impact on several hot water boiler power targets. By examining the relevant departments, and hot water boilers consume more important from these two local: the burning air-fuel ratio unqualified and heat loss. Possible to decrease heat loss can be recycled at the end of the formation of the latent heat of flue gas hot water boiler assembly, or with more kinds of class condensing boiler. Burning fuel ratio unqualified inappropriate Summary: General hot water boiler according ejector incinerator machine, causing air-fuel ratio can not be flexibly adjusted. 70% of the hot water boiler is a mechanical blower according burning machine, leading to substandard fuel ratio has the following several reasons: the more important fuel ratio failure probability can be divided into two types: When oxygen is overrun, there will not be excessive cold air is heat, hot water boiler power lead to the use of improved hot water boiler output target weakened; when oxygen is non-compliant, there will be insufficient burning phenomenon, showing a hot water boiler output target weakened. Shandong gas boiler steam boiler talked about how sewage? (1) inside open blowdown valve; (2) gradually open the blowdown valve external to warm up and sewage pipes; (3) an external switch repeatedly discharge water valve, slow flush pan scale , so that as the scale is discharged; (4) locking the inner blowdown valve, between these two discharge water storage water drain valve; (5) locking the outer blowdown valve, sewage terminated. When the people usually use gas steam boiler, power outage situation is obviously occurs when there is, admittedly now very small probability of occurrence of a power outage, What, then the people can not ignore this kind of situation may occur. The author taught the people, process knowledge this type of situation from occurring. First, after the power outage, the total mass to quickly lock steam boiler gas valve, this kind of boiler is to avoid the effect of leaking. Second, the next step is to lock the main switch valve with various natural gas steam boiler circuit. Third, locking gas steam boiler slag coherent various water discharge valve block, otherwise will probably cause additional problems of a coherent gas steam boiler. Fourth, to lock the various air intake valve deaerator. Fifth, the above outline done, in accordance with the order of daily occurrence to stop using the shutdown to manipulate, and verify that the volume of water in the furnace, gas and other energy corresponding to the description. Power outages may now be able to basically be able to say that very little gas steam generating boiler work, What, then public still can not completely avoid this kind of situation, which also requires manipulation of the masses of standard rules of this kind of situation occurred after carefully , as if such a situation occurs, etc. without question.
Currently, this system through continuous innovation and improvement, has launched a cloud service 3.0 system, you can take advantage of fast, accurate boiler data collation and analysis of Things technology, and to help customers understand the use of the boiler through the data to ensure safe and effective boiler run. As of the current track, the number of systems online boilers 4600 units, enterprises and institutions to use fast boiler feedback to us, with this system uses a boiler more peace of mind, peace of mind.
After the gas-steam circulation pump approach failed for some time to use gas steam oven, it will produce a precipitate. At this point, we need to clean heat transfer oil furnace, but before cleaning, we need to know what kind of sediment, and then cleaned the right way, if the heat transfer oil, grease appears very easy to make the wall thermal resistance increases, will increase the production of energy, gas steam liquidity will deteriorate, production will be reduced, the operating cycle will shorten the life of the device will be. Shorten, which in turn affect production. Some of the more common gas steam boiler deposits are: sulfate, carbonate, silicon and iron. Acid sulfate does not bubbling, since relatively hard sulfates, carbonates decompose at high temperatures, the bicarbonate will dissolve, but the release of carbon dioxide will form an insoluble carbonate salt. When the temperature reaches 300 ~ 400 ℃, hot oil furnace thermally cracking occurs. It will produce carbon deposits on the inner wall and an inner wall, it affects the heat transfer efficiency. Easy to produce oil furnace heat transfer in high temperature environments. Thermal cracking, thermal polycondensation, and its kinematic viscosity increases, the fluidity deteriorates internal oxidation of the oil pipeline, oil conductive accelerated failure, the machine will be damaged, endanger human will be high. Steam oven gas processing cycle pump failure: (1) When the current is below the normal circulating pump, the circulating pump efficiency is lowered, the flow rate is reduced, the fouling of the heating pipe may be blocked, it should be cleaned. (2) circulating pump pressure constant, the current increases, flow decreases. Bad heat transfer fluid, the viscosity increased, should be replaced or regenerated. If the system does not remove water or aqueous decomposition newly heated conductive liquid should be immediately opened exhaust valve to the exhaust gas. (3) circulating pump current is reduced, the pump outlet pressure back to zero, indicating that the pump is not idle. It may be vaporized oil, gas and steam oven measures to find the cause vaporization; if the filter is clogged, the circulation pump should be evacuated and cleaned immediately opens the bypass filter; if the heating fluid contained in the new water or heated water, the system does not exclude the decomposition gas, the exhaust valves should be opened immediately exhausted.