1000KG Fuel Diesel Steam Boiler
We are one of the leading manufacturers and traders of a wide range of Horizontal Type IBR Steam Boiler. Featuring a superb capacity of 1000kg/hr to 35000kg/hr, these efficient 1000kg fuel diesel steam boilers are capable of tolerating pressure 10 kg/cm2,16 kg/cm2, 20 kg/cm2. Obtainable in single-phase design, these low maintenance boilers are set up with automatic burner system.
7, fuel consumption: the amount of fuel consumed by the boiler per unit time.
8, emissions: the amount of sewage discharged boiler blowdown.
9, the natural circulation: relying on the furnace decreased working fluid between the tube and the density difference between the riser furnace actively promote water circulation boiler drum, the drum is recycled back route, the downcomer, the header, the riser pipe, tubing, etc., is introduced soda composition.
Gas heating boiler to replace the various components to achieve what state? After gas heating boilers after a long period of use, how much will be showing some of the damage, when the damage reaches a certain extent, the gas heating boiler will be scrapped. If its status as a criterion heating surface, then under what circumstances need to be replaced? First, measure the duct changes in the internal gas heating boiler, if a carbon steel pipe, then, once it's expanding crude exceeds 3.5% should replace lost; the steel pipe replacement criteria should be expanding crude exceeds 2.5%, more stringent . Secondly, for high temperature gas heating boiler superheater, the surface oxide if it has more than 0.6-0.7mm, and a deeper grain boundary oxidation cracks, crack depth than the grain size of 3-5, it will be It is considered invalid. Gas boiler heating surface found to have visible cracks or other defects in time, we must pay more attention, if such cracks or defects have been unable to repair, it can only replace the entire device. It should be carried out in accordance with the relevant standards for check pipe wall thickness and pipe gas heating boiler, ensuring accurate detection value obtained. Moreover, on the gas heating boiler economizer tubes, the amount of wear and if it has reached thirty percent of the wall thickness, it is necessary to replace. There will replace Similarly superheater, reheater water wall tube, wall thickness abrasion to reach 25 percent. Timely replace the gas heating boiler damaged parts, as long as the purpose is to not because they affect the entire boiler heating effect, guaranteed to always maintain a good working condition.
Battle blue horn sounded, emissions of sulfur, nitrogen and oxygen compounds gradually strict national requirements. To improve the quality of the environment, but also the people a blue sky, in all industries around the environmentally friendly product revolution, Hainan Sinochem Pharmaceutical companies are no exception. By the company investigation and comparison of boiler products, in March 2017 signed a six-ton steam-cleaning integrated condensing gas boiler and steam fast boiler. Tested and post feedback, the boiler equipment installation qualification, operating normally, and successfully passed the inspection by local quality inspection departments of the boiler.