Natural Automatically Gas Or Diesel fired Steam Boiler
Shandong Zhaoyuan Mining Group Co., Ltd. is a large state-owned local asset management companies, gold mining dressing and smelting for leading industries, operates in the area of tourism, services, precious metals, real estate, eco-agriculture, with total assets of 10.2 billion yuan, Shanghai gold Exchange is an international provider of standard gold bullion. July 2017, Shandong Mining Group and fast boiler steam signed a 0.5-ton electric heating natural automatically or diesel fired steam boiler which mainly produce steam for metallurgical mineral processing and other manufacturing processes, energy defeating small, strong ability to supply steam .
11.Steam exiting the high pressure steam turbine is called cold reheat.
It is reheated in the re-heater and sent back to the second steam turbine. By the time the flue gas exits the boiler most of the energy in the coal will be transferred to the water in the boiler. The hot gases are cleaned up before they are sent to a stack. Feed water is generally supplied by condensed steam from the low pressure steam turbine. Large amounts of cooling water are used to condense this steam into liquid water in the condenser.
Greater than 65t / h industrial boiler of what air pollutant emission standards should be executed? A: The State Environmental Protection Administration, Central Division-standard  No. 012 document pointed out that the emergence of a small number of parameters currently higher than GB1921-80 "industrial natural automatically or diesel fired steam boiler parameters Series" and GB3166-82 "hot water boiler parameters Series" layer burning, stoker boiler, regardless of its use Zanan GB1327-91 execution. Therefore> 65t / h or more (except coal, circulating fluidized bed, and fuel, gas fired boilers) industrial boilers should be performed "boiler air pollutant emission standards."
The inlet speed of gas-fired hot-water boiler before start-up should not be too fast, usually no less than 4 hours in winter, and 2-3 hours in other seasons, especially in the initial stage of water intake. The inlet temperature of a gas-fired hot water boiler is generally 50 °C, so the difference between the feed water temperature and the steam wall temperature in the drum is less than 40 °C. For gas-fired hot water boiler, the inlet water temperature can be equal to that of steam drum wall without complete cooling, otherwise the inlet water speed should be slowed down. When feed water enters the drum, it always first touches the lower part of the drum. If the difference between the feed water temperature and the drum wall temperature is too Large, the inlet speed is fast, and the upper and lower walls of the drum, the inner and outer walls will have a large expansion. Bad, on the drum caused a lot of additional stress, resulting in drum deformation, serious cracking. Due to the thickness and slow expansion of the drum wall, the tube wall connected to the drum wall is thinner and expands faster. If the inlet temperature of the gas-fired hot water boiler is too high or the inlet speed is too fast, the expansion will be uneven, the welded joint will appear cracks and the gas-fired hot water boiler will be damaged. The inner diameter of the decompression tube is usually φ 7~13mm (water and steam), and its length should not be too long (< 60m). Straightness of pressure pipe If the diameter is too small and the length is too long, it will affect the dynamic transmission of pressure measurement and increase the dynamic error. The inner diameter is too large to be easily maintained and installed. Pressure pipes should not be placed in the horizontal part to prevent the accumulation of bubbles (when measuring liquids) and water columns (when measuring gases). The pressure tap shall be perpendicular to the flow of the medium. Pressure faucet must not have chamfer, flange and burr. When measuring the hydraulic pressure of an electrically heated natural automatically or diesel fired steam boiler, the pressure outlet should be removed from the lower part of the pipe to prevent the gas in the liquid from entering the pressure guide pipe; When measuring the gas pressure, remove the pressure splice from the upper part of the pipe to prevent dust and dust in the gas The droplets enter the ignition line. The installation site of the electric heating steam boiler pressure gauge (pressure transmitter) should meet the environmental conditions (temperature, humidity, vibration, etc.) used by the instrument, and should be easy to observe, repair and ensure safety. Insulation should be laid on pressure pipes in high temperature media to avoid burning during flushing. Pressure lines are equipped with needle valves (for cutting off pressure in the event of pressure line failures during operation), auxiliary needle valves (for use with instruments, stopping, replacement), condensing coils and elbows (isolation elastic elements from high-temperature media), Easy to install sealing gaskets) as well as sewage valves and sewers. For special pressure measurements, it's still pressing. Install discharge valve, isolation room and so on in the force pipe.