water tube 5 ton natural gas boiler
Industrial gas steam water tube 5 ton boiler room planning considerations: industrial gas steam boiler room Planning Considerations What? Followed by the degree of technological progress from time to time, the rapid expansion of social economy, people's requirements for industrial gas boiler room planning have become more sophisticated. Now now, in the industrial gas boiler room planning there are still many achievements in urgent need of treatment, therefore, we have to enhance the learning and use of advanced planning practices and advanced technology, from time to time suspend the development and review of industrial gas boiler room planning, the industrial gas boiler housing plan is more suitable, safe, reliable and economical. 2, selection and use of industrial gas boiler at a reasonable selection of urban planning, boiler, environmental management and other mission boiler type is dropped purification, waste power, an important part of reasonable expenses. Set the cost of the boiler is one of the essential elements of when thinking of selection. Because the characteristics of industrial gas boiler itself, the boiler room and equipment to establish a more economical, should be used in high load industrial gas furnace heat boilers in order to reduce the volume of the furnace. Due to the absence of heating surface cleaner, slagging, wear results, the smoke may use a higher speed, reduced scale of the convection heating surface, convection through the rational placement control the industrial gas boiler capacity of coal-fired boiler with a more compact structure, dimensions small, light weight, in order to decrease equipment investment; supporting auxiliary boiler optional satisfactory work. Industrial demand for gas-fired boiler is not equipped with soot blowers, dust, slag and other equipment and fuel dryer slave device, and can save and land acquisition costs placed above equipment; the use of a gas pipeline walks as boiler fuel, not only no fuel storage equipment, supply calm and without prior preparation of fuel processing equipment, greatly simplified the trivial; civil engineering boiler room investment costs and other related costs will lower; no fuel storage, can save shipping costs, place and rest force. Boiler room non-essential equipment such as leak detection equipment for the surge equipment, measurement equipment, gas. Coal, oil, gas boiler three kinds of heat load in the opposite situation, a huge volume of coal-fired boilers, additional slack style drums, Fan, Java machine, dust collector, but also with storage of coal, slag heap place, It covers an area larger. Industrial gas boilers small volume itself, and these need not be equipped with auxiliary equipment, simply set up between a host and auxiliary room, set on more messy, covering economy. Industrial gas boiler city gas source is generally taken from the intermediate pressure gas supply line, the gas pipeline laying gas sampling point to the boiler room, then according to quell's brand, type and caliber regulating device applications, scheduling outlet pressure range, by metering the put into use. Establish a set fee just gas network tariffs, pipeline fees, hot walks pipeline fee. Gas pipeline network overall cost of capital is the sum of the gas company funds charged to the user, it can be determined depending on the circumstances around the gas company. Usually adopted buried gas pipeline type, buried depth is generally about 0.8m ~ 1.0m, seamless steel pipe can be selected or PE pipes, pipe surrounding sand 15cm ~ 20cm plating, hot water pipe laying relatively simple, somewhat messy steam pipe walks . 3, industrial gas boiler room planning results in the presence of 3.1. Selection of the size of the heat load of the boiler and its expansion tend to choose the boiler capacity, the number of great links. The larger heat load, single boiler capacity should be large. The near future can be greatly increased thermal load, it is also relatively large capacity boiler can choose, it will expand the load thought. The only thought to increase the long-term thermal load, the expansion device may leave the boiler placeholder deployment end in the boiler room, or space left on the total FIG. However, in the practice of project planning, often there is a lack of expansion heat load estimates, constitute improper boiler selection, pre-operation to cause unnecessary trouble. 3.2. Gas boiler gas regulator trivial results generally used in high-pressure (less than 5kPa) and medium voltage (5 ~ 150kPa) trivial. Gas usually before entering the boiler room will arrive this requirement. Now the gas hot water boiler is equipped with a high level of automation subsided, a calm requires the gas pressure is lower, so before further demand into a calm pace pressure boiler manufacturers themselves generally equipped. Gas pressure regulating trivial demands reliable equipment, but on the size of the gas pipeline valve is open due to the gas pressure when scheduling the gas pressure is high or low, and tempering will cause off, start and stop frequently subsided's configuration, thereby affecting the boiler work. 3.3. Gas boiler quality results planning standard gauge, the quality can not be ensured when the gas, should be provided or dust, oil and water, respectively, and a total closed drain valve before the gas main pipe before the regulator device. Most of the oil production plant in the use of oil with anger, it is often said of moisture in the summer cold weather, moisture and light hydrocarbons and other substances containing moisture, condensation will constitute a line blockage, an initiative to quell the flame, impact Heating. 3.4. Chimney condensate results because of the high thermal efficiency of industrial gas boiler, a low exhaust gas temperature, typically 180 degrees, the boiler room planning criteria (GB50041-2008) rules industrial gas boiler room chimney should be reinforced concrete or steel chimneys chimney. Chimney will appear directly in the outdoor summer steel chimney condensate freezing results, constitute icing light rusty steel chimney, would constitute a temporary corrosion, freezing severe affect chimney smoke. 3.5. The amount of air to quell the outcome's when quell Industrial gas boiler is in the boiler room, the air between the boiler must be satisfied the requirements apply to quell the device, otherwise there will be no abundant natural gas to quell working carbon monoxide poisoning.
Since our company uses WNS6-1.25-YQ split two condensing water tube 5 ton boiler, the boiler runs very stable, high degree of automation, greatly reducing the labor intensity of fireman our staff, because running very clean without any emissions, but also greatly improved our paper mill house and the surrounding environment, high operating efficiency boilers. Service is also very timely response to our technical consulting reply quickly and accurately. Especially for regular visits to thank! --customer feedback
How to divide the bath hot water water tube 5 ton boiler and selection class to the bathroom, then select the main boiler needs heating hot water boilers generally refers to the bathroom so hot water boiler, it probably belongs to the scope of civil boiler life. Jacuzzi bathtub boiler electric boiler, bath oil-fired boiler, gas boilers bath tub and coal-fired boilers. Baths annual major need for heating in winter and hot water, then bath boiler how to choose it? Selection 1, the number of choices bath of hot water boiler (1) is currently the best configuration choice 1 hot water boiler heating units, 1 hot water boiler with hot water for bathing. (2) selection of large hot water boiler with a plate heat exchanger. Classification bath hot water boiler and selection of the former large investment, but it is more economical to run, since the summer, late spring and early autumn does not require heating, so running a boiler to provide hot water for a bath. By increasing the plate heat exchanger, the latter method can be implemented with a double oven, small footprint, saving the original investment. 2, select the type of coal-fired boiler pollution. Most Chinese cities are prohibiting the installation and use of coal-fired boilers. Thus, other environmentally friendly boilers, such as oil-fired boiler, gas boilers and electric boilers, are still in the selection. Bath with a gas-fired boiler more economical than oil-fired boiler and electric boiler.
Fangkuai water tube 5 ton boiler for you to sort out 30 boiler operation common problems and solutions, after learning, do not forget to share with your friends oh. (6) what are the main factors affecting the wear rate? 1 flue gas, 2 flow rate of the material, 2 particle size of the material in the flue gas, and 3 the surface shape of the worn component. The velocity of air flow is the most important factor affecting the relative direction of motion of the worn material and the wear is proportional to the third power of the velocity. 7. Why should the bed temperature be controlled between 850 and 950? 1 the ash will not melt at this temperature, thus reducing the risk of slagging 2. Higher desulfurization efficiency 3 less nitride gas in combustion gas at this temperature 4 Alkali metal in coal does not sublimate at this temperature, which can reduce slagging on the heating surface. 8, why do you have to blow the boiler pipe? Some equipment in boiler steam-water system, such as dewarming water, start-up bypass, superheater, reheater pipeline system, are not suitable for chemical cleaning due to structure, material, arrangement and other reasons. So it is necessary to use the physical method to remove the residual debris before the new boiler is put into operation, so the steam produced by this furnace is used to blow the steam-water system and equipment. 9, what are the common methods of boiler maintenance? (1) Wet protection: there are diammonium method, ammonia method, maintain feed water pressure method, steam heating method, alkali liquefaction method, trisodium phosphate and nitrous acid mixed solution protection method; (2) dry protection: there are drying method (with pressure discharge) and desiccant method. 10, which causes the deterioration of steam quality (steam pollution)? (1) steam with water. The boiler's feedwater contains impurities. The feed water is heated into steam after entering the boiler, and most impurities are transferred into the boiler water. So many cycles, the impurity concentration in the boiler water becomes higher and higher. Furnace water containing high concentrations of impurities is carried by saturated steam, which is called steam carrying water, which is called mechanical carrying. The first reason for steam pollution. (2) Steam-soluble salt. At higher working pressure, steam can dissolve some salts, which is called selective transport, which is the second reason of steam pollution.