Hot sale WNS oil or gas burning steam boiler
1. oil and gas hot sale wns oil or burning steam boiler system
A complete gas boiler system mainly includes the boiler body, burner, control system and other auxiliary structures
Boiler + Things, security, intelligence is our reputation. Based on advanced networking technology, remote monitoring group launched the operating system of the boiler, which in the domestic boiler industry are unprecedented breakthrough, the country has more than 4,600 boilers supporting the remote monitoring system, safe and stable running.
Matters needing attention in installation of Gas-fired BoilerGas-fired boiler also says that gas-fired heating boiler is a kind of boiler which uses gas combustion to heat water to satisfy people's heating. It belongs to the category of domestic boiler. By gas-fired heating boiler we usually refer to gas-fired atmospheric hot water boiler, gas including natural gas, liquefied gas, city gas, coke oven gas, biogas and so on. There are explosion-proof doors on the rear of the fuel-fired boiler or on the smoke pipe, and the position of the explosion-proof doors should be conducive to the discharge of the explosion. In cases where explosive gas may endanger the safety of operators, a pressure relief guide tube shall be installed on the explosion-proof door. The installation of boilers, auxiliary machines and water treatment equipment shall be in accordance with the technical requirements of the equipment manufacturing plant. . The equipment foundation must wait until the equipment arrives and checks correctly with the design drawing before construction. 3. When installing the equipment, avoid the equipment, and the installation material should be stacked on the floor. When using building column, beam lifting equipment, the bearing capacity of beam and column must be verified in advance. 4. After installation of oil, gas, hot water and steam pipes, the pressure test acceptance shall be carried out according to the Code for Construction and acceptance of Industrial Metal Piping Engineering GB 50235 / 1997.
Details installed gas boiler combustion system that we need to pay attention when installing a gas boiler combustion system, inviting professional staff in advance of the circuit diagram design, so that when installing the status line installation will not appear unreasonable. Also, pay attention to install some fire-fighting equipment, which can provide protection for our security. Unit ventilation should generally remain the total combustion air amount at the rated load. Combustion process controller provides a separate set of contact start-stop control. May be formulated in a variety of burner start-stop loop cascade control relay 10A is a fuse, relay start-stop control stops the control terminal may be connected to the burner, may directly control the power of the burner. Both constant pressure sensor, water power, fuel, gas pressure set value is detected after the automatic controller opens. Time pressure sensor, water supply, oil, gas, and their detection circuit, alarm and found the problem immediately shutdown flame protection, the controller automatically displays the point of failure, an alarm sounds machine. Installation room oil, gas line gas boiler, boiler room should be strictly in accordance with design, specification, and should refer to the burner. Fuel system pressure test after installation is complete, should be 1.25 times the working pressure (minimum test pressure of not less than 0.4MPa). After the fuel pipe installation system should be flushed with water or steam flushing, flushing should have approved technical measures, the number of washing is not less than the secondary blowing, blow up until the clean medium, should be cleared after the purge debris and dead. After installation of fuel system should be oil circulation system-wide test. The gas should be the shortest route to the burner, the air supply pipe diameter must be larger than the constant value parts of the burner duct.