Vertical 1 Ton Steam Boiler
Our preliminary investigation when the other side is very interested in fast boiler, a number of fast-party research and development as well as outstanding patent cases in all industry sectors, we have confidence in each other quickly this brand. After the cooperation, but also the strength and each staff fully aware of the fast boiler of a good attitude, and cooperation in the box, very at ease. --customer feedback
Daily hot water boiler hot water boiler blowdown precautions before working sewage water boiler should point higher than the normal water level is adjusted to the state, keeping in view the drain valve temperature, if the temperature is higher then the exploration drain valve leaks will have timely check the reason to eliminate as soon as possible. But also regularly check the sewage outfall hot water boilers to avoid damage to the sewage pipes are not smooth water circulation system. But also timely sewage, shift work after the handover should be promptly checked after outfall vertical 1 ton steam boiler for hot water boiler blowdown period of time to work, it is pressure boiler fire, sewage, or choose to work at low load, select this time period the reason is because the water circulating in the boiler convection slow, dirt in the pipeline is likely to accumulate time, so this time the sewage, then the effect is relatively good, nor will it contribute to steam hot water boiler affected. For the process of hot water boiler pollution suggest that you should be much shorter intervals in the case of repetition, so you can make the dirt more focused and more rapid discharge. Sewage process operator must not leave the scene, pay attention to water level changes, so as to avoid the phenomenon of water in the furnace.
The coal fired hot water boiler is a good heating equipment, with water-cooling membrane structure is economical and environmental protection, high efficiency and safety, easy operation, flexible, convenient and sturdy, longer service life. For coal fired hot water boiler stress area is larger, heat transfer effect is much better. Besides, coal hot water boiler pricing is leaner, bringing people less pricey and practical benefits.
A gas boiler maintenance, boiler feed water gas manufacturers give the boiler 1. Maintenance must be qualified treatment, which is to extend the life of the boiler, ensure the safe operation of the important issues. 2. The water temperature should be close to the furnace temperature, preferably above 20 ℃. 3. The need for low-water cutoff periodically inspect maintenance and cleaning. Water Level Controller cleaned at least once a month, rinse water table at least once a day. Rinse water table should be at the highest level; after flushing the water level should not be less than the minimum safe level, not as a net wash, can wash many times, but it must be flushed at the highest level. 4. require periodic blowdown operation, daily (per shift) at least once, after the sewage drain valve should be checked whether the influence by dirt and leaks; if it must be excluded. 5. Shutdown the steam pressure is not maintained, the boiler will produce steam space negative pressure air entrapment, and therefore should rise again to the fire burning total steam valve is opened. 6. smoke tube fouling will lead to increased exhaust gas temperature, so that boiler efficiency is lowered, so that the fuel consumption increases, it should periodically open the front door, brushing or blow smoke tube fouling. Second, the shutdown maintenance and corrosion in boiler 1. After the shutdown, in order to prevent corrosion of the pot must be maintained. 2. Short-term maintenance. Wet regimen employed; i.e. after the shutdown, the water will fill the furnace, the entire exhaust air. 3. Long-term maintenance. Regimen can be dry, i.e., after the furnace shutdown drain the water, open the lower hand hole, dry water pot, and through the lower hand hole, into the drying agent, and should be replaced periodically, may start to replace monthly check - times, after three months may once. It should be noted, before the boiler is enabled, be sure to remove all desiccant. Third, monitoring and maintenance of the boiler 1. The operation of every checking operation key and rotatable member boiler safety device for 1 hour to conduct an inspection apparatus. 2. Check the boiler equipment, testing and regular operation of the project cycle, make specific provisions and loading site as an icon. 3. Run the personnel records based on timely completion of the inspection. 4. The site must be kept clean, so that no debris, no fouling, no water, no grease.