1 ton diesel horizontal steam boiler
Boiler and steam should have what conditions? (1) normal boiler plant, (2) a suitable material thickness, stable combustion furnace. (3) a pressure slightly lower than the superheated vapor pressure of the main steam pipe, generally 0.05 ~ 0.1MPa. (4) steam temperature between 370 ~ 400OC. (5) Drum Level of about -50mm. (6) steam quality qualified. (7) the tube conduit has fully warmed. Boiler Water Level Indicator How to deal with the failure of the boiler drum water level how to deal with failure? (1) such as boiler drum water level table has a damaged: damage to the door immediately closed water table level, valve, open its doors hydrophobic. With another drum water level meter to monitor the normal water level in the drum. Take urgent measures to repair or replace damaged water gauge. (2) Drum Level two tables are damaged, but the boiler feed water automatically, water gauge differential pressure within one hour and the front drum level table has proofreading, confirmed that the correct and reliable, with reference to the feed water and steam flow meter instructions, continue to run for 20 minutes. In both cases, the squad leader should report the value of long, to maintain the stability of the boiler load, and to take urgent measures to replace the drum level table. (3) If the two tables are damaged drum water level, water level gauge while the differential pressure is unreliable operation, should the emergency shutdown process. How to determine the boiler load plummeted? It plummeted What is the reason? What should I do? Come the following: boiler load plummeted phenomena: (1) steam flow plummeted, steam pressure soaring. (2) found the treatment is not timely boiler safety valve operating will result. (3) decreased instantaneous boiler water level then rises, a high level alarm signal. When the safety valve seat, the water level decreased rapidly, may cause low water level alarm signal. (4) When the transmission switch trip, to swing each of the auxiliary ammeter have abnormally, the flash lighting. Boiler load sharply reasons: (1) an outer line switch trips. (2) steam turbine emergency stop. (3) Isolation Valve core valve or the main valve off. Plummeted boiler load process: (1) The table indicates drum water level, steam and feedwater flow meter, automatic to manual feed water, to adjust the water level. (2) The rise and decline in steam pressure load, and timely Kohiki off, air supply, stop grate, holding BOILERS, open superheater hydrophobic. (3) timely adjustment of desuperheating water gate, so that the steam temperature is normal. (4) If the discovery process is not timely, the pressure exceeds the safety valve operating pressure, and when the security gate does not move, should Stokes Exhaust electric door open, until the normal pressure. (5) make contact with a load preparation, monitor and report the value of long. (6) accident, checked the action over the security door situation, is closed tight. When the boiler drum level is unknown how the "waters"?
According this project,We found that Spain have rich biomass resource can be used in industry for boiler as burning fuel.The Spanish have gone from consuming 100,000 tonnes of pellets in 2010 to 380,000 tonnes in 2013. And forecasts published by various organizations are saying that by 2020 the 1.1 million tonne mark will have been passed.
The difference between 1 ton diesel horizontal steam boiler and hot water boiler
What is a steam boiler? What is a hot water boiler? What is the difference between a steam boiler and a hot water boiler? The characteristics of steam boilers and hot water boilers are analyzed. In fact, the steam boiler is also used by the boiler to directly vaporize and generate steam after boiling the water.
Burns Hospital Affiliated Hospital of Shanxi Linfen Linfen Steel is attending a hospital burns burns and other diseases. Hot water boiler is essential hospital equipment heat, hot water output can provide disinfection of medical instruments and ward heating demand. With constantly improving our environmental policy, boiler correspondingly introduced more sophisticated Use. Linfen hospital burns to respond positively to the national environmental policy, decided to introduce an environmentally friendly low nitrogen gas hot water boiler. Taking into account the special circumstances of the hospital, the boiler should also have the use of safe, clean overall characteristics. Based on the above considerations, finalize the Linfen hospital with burns boiler party cooperation fast, fast is provided by one side of a gas condensing pressure hot water boiler (CWNS2.1-95 / 70-Y.Q).