6 3 mw gas boiler in japan
WNS is automatic gas (oil) parameters commonly used 6 3 mw boiler in japan. Where each letter implication is that
W: horizontal. A boiler according to the design and installation of the outer layout, was lying state. An exhaust gas stream produced by the boiler is of horizontal flow, the flow of hot gas, in the same section on the exhaust gas temperature is low compete.
You must know the 6 3 mw boiler in japan energy problems (induced draft fan power consumption rate, steam consumption) draft fan causes problems 1.1 boiler flue dust and fouling, in particular air preheater fouling, resulting in increased resistance to smoke duct . 1.2 boiler flue, tail heating surface and dust leakage. 1.3 Leakage Rate large air preheater. 1.4 furnace excess air coefficient is too large. 1.5 unit load changes, run the adjustment is not timely, resulting in furnace pressure is too large. 1.6 unit load or low frequent starts and stops. 1.7 coal into the furnace worse, from the design value. 1.8 low efficiency filter. 1.9 draft fan blade badly worn, low operating efficiency. 1.10 fan outlet flue gas desulfurization big resistance. 1.11 soda boiler pipes for leaks. 2, 2.1 to 2.1.1 operational measures to solve the problem of the strict implementation of soot blowing system to prevent the heated area ash, blocking ash, flue gas system to reduce resistance. 2.1.2 holding the induced draft fan, the flue gas separator baffles and dampers in the fully open position. 2.1.3 The experiment showed combustion boiler, proper control of excess air in the furnace. 2.1.4 adjustment chamber negative pressure, air leakage reduction furnace and the flue. 2.2 routine maintenance and testing 2.2.1 induced draft fan performance test to determine the optimum operating point and efficient workspace. 2.2.2 boiler, air preheater, a flue, ESP and other system leakage inspection, process. 2.2.3 timely check processing chassis, shaft seal leakage. 2.3C / D repair, eliminating defects 2.3.1 down strict accordance with movement clearance adjusting fan. 2.3.2 induced draft fan blade defect action elimination hand vane opening adjustment. 2.3.3 Importers and induced draft fan baffle opening check. 2.3.4 duct tightness check process. 2.3.5 wave plate replacement air preheater, rinsed sector plate gap adjustment. 2.3.6 eliminate dust defects and improve collection efficiency. 2.3.7 clean flue gas desulfurization system, flue resistance is reduced. 2.3.8 eliminate soda boiler pipe leakage defects. 2.4A / B repair and transformation 2.4.1 Check and repair the fan blades, replace seriously damaged blades if necessary. 2.4.2 for energy saving fan efficiency below 75%. 2.4.3 The fan motor frequency transformation. 2.4.4 of the precipitator, if necessary, transform and improve collection efficiency.
Gas-fired center 6 3 mw boiler in japan reminds you to shut off the fuel supply of the furnace immediately in case of quenching, close the electromagnetic valve for gas supply (oil and return), and then close the fuel supply valve for the operation of burners. Operate quickly so as not to cause a vicious risk when fuel continues or resumes supply. At the same time, find out the causes of boiler quenching, remove the found faults, and make preparations for restarting.
On the ISH heating HVAC industry event, fast Boiler bring new products customized for the paper and packaging industry well-built --- Euromonitor θ5 stunning debut, attracting various participants competing concerns. The product closed condensate recovery system, temperature condensate directly into the 6 3 mw boiler in japan design, three-pass boiler with economizer + + structure air preheater for recycling heat from the high temperature condensed water source, the thermal efficiency of up to 95%, to save operating costs with immediate effect.