Best Boiler In China Gas Steam Boiler
The preparation you need to do before the boiler is installed
The boiler is a device that supplies steam and hot water for industrial production or daily life. After the company purchases the boiler model, it needs to consider the installation problem. The installation of the boiler is directly related to the important steps of the smooth operation of the boiler, except for the installation of the auxiliary machine. Also need to pay attention to the preparation before installation.
1. Handling the registration of natural gas boiler installation: According to the “Safety Supervision Regulations for Steam Boilers”, the units that use the boilers should go through the registration procedures one by one. The boiler use unit shall have a person responsible for the boiler installation work, responsible for contacting the local boiler supervision agency and filling out the installation notice. When the boiler is installed, it must be attended by a furnace, and it is equipped with a pipeman, a fitter, a hoist, a cold workman, an electric welder and an auxiliary worker.
2. Determine the installation location and qualification of the boiler to determine the installation location. The boiler installation unit must have a boiler installation qualification certificate issued by the superior authority in accordance with the installation scope.
3. Inspection of boilers and accessories: Before the installation of natural gas boilers, the boiler body, combustion equipment, components, natural gas boiler auxiliary machines and accessories shall be inspected and accepted according to the drawings, and records shall be made. If it is found that the relevant standards are not met, it shall be promptly submitted to the factory. .
Recently, market supervision bureau issued the Notice on Strengthening the National Energy Board within the scope of the power station boiler piping material quality safety risk prevention and control (the "Notice"), to further enhance the quality and safety supervision and management of boiler tubes, effectively preventing security risks, protect the power production safety , as follows.
First, carry out the verification of boiler tubes
The electricity business, special equipment manufacturers to immediately organize boiler tube inspections, to verify whether the focus of the pipe to meet the technical conditions stipulated orders, including the source, size, quantity, quality certificates, raw material procurement contracts, procurement contracts and other piping components. For imported pipe material, but also the verification of the customs declaration, commodity inspection report (proof of entry inspection and quarantine of goods), combined with the production, inspection and testing during use and operation of the situation, in-depth investigation pipe quality boiler safety issues and risks.
Second, effectively prevent security risks
Boiler pipe quality and safety hazards or other problems threatening the security and stability of power station boilers, power companies, special equipment manufacturers to take practical measures immediately, the complete elimination of quality and safety problems; there are significant quality and safety problems, it should stop running generator sets , boiler or stop production and sales of the pipe elements, and replace the boiler pipe complying with relevant standards.
The actual boiler pipe manufacturing unit is unknown or if there are doubts, the relevant information or data can not be traced authenticity, power enterprises, special equipment manufacturers to immediately in accordance with industry standards, inspection and testing institutions have entrusted the appropriate qualifications for boiler tubes were identified test. Test results show that failed boiler or pipe quality does not meet the technical requirements stipulated in the order, power companies, special equipment manufacturers to eliminate hidden dangers in a timely manner or be replaced.
Third, strengthen the source of control boiler pipe
Special equipment manufacturing enterprises, power enterprises should strengthen boiler pipe source control, in strict accordance with the standard provisions of China's relevant laws and regulations and orders technical conditions agreed to carry out boiler pipe design and manufacturing, procurement orders, admission acceptance, inspection and testing, installation and commissioning work, resolutely eliminate substandard or counterfeit boiler pipes enter the field of electricity production; to strictly implement the special equipment safety supervision and management regulations, establish and improve the technical archives and long-term care, to ensure that relevant information can be traced back.
Special equipment manufacturing enterprises, power companies are finding there are significant quality and safety risks of boiler tubes, to report to the local market regulators, power management departments and the National Energy Board sent energy regulators, and to take effective measures to thoroughly rectification to ensure the safe operation of generators . Provinces, autonomous regions and municipalities and Xinjiang Production and Construction Corps Market Authority (Hall Commission) should work together with the same level of power management departments, the National Energy Bureau sent energy regulatory agencies and other units, the organization of supervision and inspection, supervision and hidden rectification, effectively preventing security risks.
In order to ensure boiler safety, to run smoothly, you must ensure that the use of high-quality natural gas. 1, equipped with one gas separator to increase the capacity, it can effectively store oil and water. Secondly, a level gauge designed to directly observe whether there is liquid in the separator. While the design of the automatic drain pressure relief device is installed. A single control pressure of the air is improved dual control, i.e. the pressure regulating valve is mounted on the main line to control the water separator, the pressure to stabilize, improve security purposes. 2, safety monitoring natural gas as a boiler room burning materials, natural gas leak monitoring must be done. The portable display technology poor performance, poor sensitivity. Host combustible gas alarm system with digital control scaling circuit having an alarm function and a secondary alarm, ensure the safe operation of the boiler. 3, check before firing the safe operation of: (1) whether the boiler inspection gates normally open or closed, check the gas pressure is normal, not too high or too low, open the supply valve leading to the boiler. (2) in the flue baffle must be fully open, otherwise it will affect the purge, causing accidents. Each knob and keep control cabinet to check the normal position. If the stove has a residue should be cleaned. (5) Check the boiler ignition and fire protection program control means should be flexible and reliable. Blast doors should be flexible and rigorous on the boiler. Before the completion of ignition, the ignition is not possible to start the ignition operation: After successful ignition, the load can be adjusted in the normal operation of the boiler when the combustion gas boiler adjusted. We should always observe the combustion furnace, and adjust the amount of steam, wind and steam pressure to ensure the safe operation of the boiler. Note: Program: first five minutes were furnace cleaning, automatic ignition after 5 minutes, observe the ignition is successful, the success of one minute after a small fire can be operated automatically converted to fire properly. For the boiler load and the air pressure adjusted by adjusting the pressure regulator to achieve. When adjusting the load, adjust the air pressure at the same time, it must be synchronized to adjust the air flow to ensure a reasonable match air volume and air volume, in order to achieve economic operation of the boiler. In normal operation, the amount of gas should not be adjusted or reduced drastically in order to avoid dramatic changes in combustion, the pressure receiving member sudden expansion, shrinkage and damage. When the boiler is running, the pressure gauge must be monitored regularly in order to maintain stable water pressure. BCP pressure changes observed, reflecting the relationship between water temperature and steam consumption. In the boiler operation, when the steam pressure is automatically adjusted, the main purpose of the staff is to monitor automatically adjusts the boiler system is sensitive and timely solutions to problems and ensure the sensitivity and reliability of the automatic control system. 4, first close the main valve shutdown operation, the air supply is stopped, the circulating pump and the water pump is still running, when the boiler water temperature falls below 70, and supplies or stops the circulation pump in operation of the pump after about 4 hours. Note: In addition to the accident and emergency parking stop, parking general approach should not cut off the power. After the shutdown, it is timely for the boiler and ancillary equipment to conduct a comprehensive inspection. If you find a defect in the device, and repair should be recorded at the time of shutdown. Safety Precautions 1. burner startup, if the burner is repeatedly locking and alarm, you should find out the cause of the malfunction, press the reset button after troubleshooting, press the reset button and then continue to boot. Note: Press the Reset button for less than 10 seconds. A lower burner inlet must be clean and clean, and does not allow offal. 2. burner once the ignition is unsuccessful, Boiler Fan should be restarted. Ventilation After 5 minutes, start the second startup burner igniter. three. During normal operation, the thermal device near the burner portion (e.g. flange connections) will be very hot, in order to avoid burns. Do not put flammable materials in the vicinity so as not to cause a fire. 4. The operation of the boiler circulating pump must be closely monitored and the hot water boiler pressure, gas distributor, pipeline valves, pressure gauges, flow meters, water level gauge and the like. 5. When the firefighters open the door or fire door observation, you should wear gloves and a side view. 6. A burner working environment should be kept clean and dry, in particular, a flame detector (i.e. electric eye) should be kept clean, part of the control circuit should humidity and temperature; class should cleaning and maintenance of a combustor. 7. During use, the filter should be cleaned regularly check or replace the filter cartridge in accordance with impurities of the fuel. 8. Check the electrical installations include: wire is damaged, the sheath is damaged, the screw is loose, the contact is good, whether the motor is running abnormal noise. Describes the advantages and disadvantages of natural gas boiler, editor of Sin sets introduced, the use of technology and safety precautions. Industrial boilers to energy efficient, environmentally friendly development direction. Natural gas boiler to meet the needs of these three points. They are the future of the boiler market trend, more and more restricted energy policy, energy saving and environmental protection requirements.
20 tph oil and gas boiler for Paper mill
Paper mills consume a lot of steam because of their production needs. In order to meet the production needs, paper companies need to purchase boilers for steam production. A paper mill in Iran purchased a 20-ton szs series of fuel gas boilers produced by CBM according to production needs.