Best Quality Steam Generator
Description electric heating boiler electric heating boiler convert electrical energy into thermal energy, the pressure of the water is heated to hot water or steam (saturated steam) a thermal device. It requires no furnace, flues and chimneys, and without the fuel storage site, greatly reducing the pollution caused by conventional coal-fired boilers. Electric boiler with no pollution, no noise, small footprint, easy to install, fully automatic, safe and reliable, the thermal efficiency of 98% or more other features, is a green product. Many countries in the late 1970s to the early 1980s, began to research and development of electric boiler. China in the mid-1980s, started developing electric boiler products, by the mid-1990s, many companies will be applied to electric heating boiler, central air conditioning and hot water supply. Category: Electric heating boilers are divided into three categories: LDR (WDR) electric steam boilers, CLDZ (CWDZ) electric hot water boilers and KS-D electric water boiler. Electric water boiler which is divided into KS-D electric water boilers and XKS-D electric storage water boiler. The impact of fuel: in the development process of the boiler, the type of fuel has a great influence on the furnace and combustion equipment. Therefore, not only requires development of various combustion furnaces to adapt to the characteristics of different fuels, but also to improve combustion efficiency to save energy. Additionally, technical improvements of the furnace and the combustion device further required to minimize contaminants (sulfur oxides and nitrogen oxides) in an exhaust gas boiler, coal and wood early shell boiler fixed grate, and multi-quality coal burning wood, coal and slag are added by hand. It began to grate after mechanized straight water tube boilers appears, chain grate has been widely used. Blowing wind never segmented cartridge system under development into segments blowing grate. Early furnace low, low combustion efficiency. Later, it was recognized that the role and structure of the combustion furnace volume of the furnace made high, and the use of furnace arch and secondary air, thereby improving combustion efficiency. 2, coal oil and generator power exceeds 6 MW, the size of these layers grate burner is too large, complex structure, easy arrangement, so 1920s using the burner chamber, the combustion chamber coal and oil burning furnaces . After the coal ground by the mill coal burner combustion injected into the furnace, then the capacity of the generator is no longer limited by the combustion apparatus. Since the beginning of the Second World War, almost all of the power plant boiler using the burner chamber. Pulverized early produced using U-shaped flame. Burner pulverized coal flow jetted to fall in the furnace, and then turns to rise. Later appeared cyclone burner front wall arrangement, L-shaped torch flame in the furnace. As the boiler capacity is increased, the number of cyclone burners also begins to increase, may be arranged on both sides of the wall, the back wall may be disposed on the front. Around 1930 he appeared in the four corners of the furnace and is arranged mostly circle tangential DC combustion burner. 3, after the Second World War, oil, cheap oil, widely used in many countries have begun to oil-fired boiler. Automated oil-fired boilers easily improved. After the 1970s oil price increases, many countries once again turned to the use of coal resources. At this power plant boiler capacity is also growing, combustion apparatus requires not only complete combustion, ignition stable, reliable operation, good low-load performance, must also reduce pollutants in the exhaust.
Rated evaporation gas steam boiler rated evaporation to choose the size of the boiler steam boiler is a proper noun, which is the power of steam boilers. Calculated: (ton unit) the general power best quality steam generators are rated by evaporation. Rated evaporation is a boiler to heat water per hour becomes steam production. This is the main argument when we need to consider the selection of steam boilers. How to choose the right Rated evaporation it? Generally, we first calculate the own use of steam per hour required, if the hotel laundry room and hospital disinfection equipment, you can see through the steam parameters parameters to calculate laundry facilities needed for every hour; if it is the plant process steam then it can be calculated per hour of steam required by the process. After calculating their required amount of steam we can choose the boiler, and generally we need to select the rated evaporation than we calculate the steam boiler with 20% of the amount. Because there may be some cases in the actual use of the process to increase the amount of steam, or steam boiler does not reach its ideal operating conditions. Here should be noted that, in accordance with our steam boilers are marked on the boiler rated pressure to calculate the rated evaporation, and some foreign steam boiler is zero pressure steam production to the subject. Such as poly rated pressure force is 1.0Mpa steam boiler, the steam temperature is 184 deg.] C to produce, while the zero pressure steam production refers to the production of steam output of 100 deg.] C, to the middle of the big difference.
Young workers from Tianjin, said the training is very timely, went through the last heating period we have a lot of operational settings, fault verification, exclude doubt want to learn the skills, the training targeted and very practical, lecturer lectures easy to understand, is a rare and rewarding "charge" in the hope the group can fast side of this type of open class continue gone out of existence, we have a great need for such training.
Steam boiler heat loss is what causes? Steam boiler heat loss caused to the user a lot of burden, whether it is hot steam boiler what is causing the loss of it? To analyze together with you today. Specific causes heat loss of the steam boiler at several: 1: heat loss of exhaust energy: smoke exhaust gas boiler comprises means losses are not completely absorbed by the steam heat loss. How caused? Short distance high temperature flue gas fan suction force is too high, the high temperature flue gas immediately excluded from the boiler; a small heating area, high temperature flue gas boiler can not be sufficiently absorbed. 2: the fuel gas does not completely heat loss: the combustible gas discharged from the flue gas generated in a boiler, the fuel in the combustible gas or gaseous fuel combustion process itself does not contain all of the incomplete combustion releases heat losses arising. As the incomplete combustion of carbon monoxide and carbon dioxide containing off-gas produced by combustion compared to the complete, only a quarter of the amount of heat released. 3: Solid incomplete combustion heat loss: refers to the solid fuel combustion process as a fuel grate down the drain does not release the heat of the flammable substance and ash contained in the combustion of the fuel can not completely burned released heat loss caused. 4: Loss steam boiler Grate: refers to the internal heat loss of the absorbent. 5: high temperature heat loss: Indicates high water temperature and hot water temperature, heat loss. 6: heat losses within the best quality steam generator tube due to furring bilingual.