industrial 1ton oil fired hot water boiler
Fuel gas-fired boiler is different from coal-fired boilers, which requires the use of a burner fuel is injected into the boiler furnace using a combustion chamber without the use of fire grate facilities. Because not produce fuel ash after burning fuel gas-fired boiler, fuel gas-fired boiler so without slagging facilities. Oil injected into the furnace, if the gas and air mixture within a certain range, or turned off, it is easy to explode. Therefore, fuel gas-fired boiler combustion required to adopt automation and control systems. Fuel gas boiler compact, small boiler and ventilation, water supply, control and auxiliary equipment are arranged on a distribution box, it may also be assembled and medium-sized factory.
Hot water boiler fuel components have whatever civilian commercial or industrial production, oil industrial 1ton fired hot water boiler is that we often need to use, so today small'll tell you about the structure of the relevant fuel hot water boiler. A blower: a filter and a suction port of the blower equipment, ventilation into the burner through the work-related apparatus for flame adjustment to achieve. Second, the supply pump: softened water from the main water pressure economizer into the next device, thereby removing heat emission of smoke caused by hot water boiler fuel to a water preheating effect. Third, natural gas systems: the interface includes a gas, burner, natural gas adjusting means. Fourth, the security valve: equipped with a pressure relief initiative greater than the preset value. Fifth, oil hot water boiler automatic control and other components sum of these components is tantamount to fuel hot water boiler said earlier, assuming that the output way, the boiler input indicators of poor water quality, is to keep from the furnace, need to pay close attention . On the way output, fuel hot water boiler to check the maintenance schedule, rigorous process of checking maintenance records, only rigorous work, unswerving overhaul inspection before they can improve production yields greater and greater extent, have does not appear to grasp the consequences.
Still 8 cultural and creative industrial park is located in the Chaoyang District, Beijing, Bali Zhuang Chen Lin, No. 2, construction area of 493,300 square meters. Surrounded by quintessence of Court, Red Sandalwood Museum, Shanxi Museum and other famous attractions. Due to its special geographical location, has very stringent requirements for providing heat boiler plants. Carefully selected to finalize cooperation with our company, signed a two He Lide series complete condensation pressure industrial 1ton fired hot water boiler.
Solutions and prevention of gas oil-fired boiler flameout Today we'll resolve what about gas fuel boiler flameout solutions and prevention fuel gas-fired boiler flameout Solution: First, the furnace pressure gauge indicates the value suddenly increases, the furnace black can not see the flame, burning furnace sounds disappear, extinguishing the flame supervision devices emit a signal; the temperature dropped sharply atmospheric pressure, the water level dropped after the first rise, and so are flameout phenomenon. Auxiliary flame caused by an accident, such as a fan, blower power interruption, there is an accident signal emitted; fuel supply as a result of intermittent, the boiler is oil or gas pressure drops to zero, only a single burner flame, the furnace may also be thrown skew central flame extinguished burner pressure change; as a result of the fuel supply interruption, the extinguished burner pressure or hydraulic indication may drop to zero, and the fuel consumption, the gas pressure is increased other operating burner. Causes gas boiler flameout are: sudden increase in gas pressure caused from the fire, the solenoid valve malfunction the gas supply interruption, the gas composition has changed so much moisture content is too high and so on. Blower, fan failure, the load is too low furnace pressure is too large excessive leakage and other excessive wind, so that the furnace temperature is too low can also cause the boiler flame. Cause misfire has oil-fired boiler: oil pump failure, the oil surface is exposed inhalation tube, clogging of the oil filter or oil supply pipe, a solenoid valve malfunction or misoperation caused by oil running intermittently. During transport the fuel with steam by heating water; inappropriate position inhalation tube with the pumping of water; improper contaminated oil floating on the water; poor dewatering tank drain plug such that the fuel with water. After the explosion should be taken to prevent the furnace boiler flameout, it must immediately cut off the fuel supply to the furnace, and then block the electromagnetic valve of the gas supply valve to seal off the fuel supply to run the burner. When the action to be fast in order to avoid inheritance or restore fuel supply during operation, causing the furnace explosion. And identify the cause of boiler flameout troubleshooting find a good job and then start the preparatory work. Before starting the boiler should be enhanced ventilation purge, purge time is more than 5min, then procedures ignition. It is forbidden to send fuel directly to the high-temperature furnace without using an ignition spark ignition device to prevent furnace explosions. If due to fan failure caused when the flame should be quickly cordoned off the fuel supply line of each valve, with special attention because the valve is not tight blockade caused by leaking fuel. Ventilation and purging of the furnace and flue in accordance with the approach of an emergency shutdown. Ignition step by step in the recovery operation after the fan. Single burner flame burner only block the fuel supply valve, the burner off a small damper identifying and troubleshooting and then re-ignition by the ignition process. Boiler flameout of prevention: For oil-fired boiler should minimize the possibility of fuel transport, storage and handling of water in all sectors. Tank initiative measures should dehydration and dehydration on schedule. In any case, it should ensure the security of oil supply. The supply of oil and acceptance testing, cutting oil change when the master species. When a large change in oil types, varieties and the need for the oil tank to store the original varieties contaminated test to determine whether the same storage tank, to prevent the density and viscosity differences between a large number of decomposed oil mixed insoluble material, clogging oil pipeline. For the operation of the gas boiler should be closely monitoring the evolution of gas pressure, the timely processing of exceptions thrown up air pressure, ensure the supply pressure in the normal range. To always understand, repair gas composition, gas composition changes when large, to take the necessary adjustment measures on the boiler operation.