high quality best gas steam boiler
How to observe whether high quality best steam boiler is short of water and how to deal with itSteam boiler is a kind of energy conversion equipment. The energy input to the boiler is chemical energy in fuel, electric energy, heat energy of high temperature flue gas and so on. After boiler conversion, steam, high temperature water or organic heat carrier with certain heat energy is outputted out. Water level below the minimum safe water level, or invisible water level, water table glass tube (plate) appears white. The two-color water level meter shows all the gas-phase indication colors. Low water level alarm signals occur in high and low water level alarms. Low water level interlock device, water level below the specified value should stop the operation of fan, induced fan, grate reducer motor. There is also a sharp rise in superheater steam temperature above the normal outlet Steam temperature. The exhaust temperature of the boiler rises. The feed water flow rate is smaller than the steam flow rate, if the furnace tube or coal economizer tube rupture cause water shortage, the opposite phenomenon will occur. When the water shortage is serious, you can smell the scorching smell. When water shortage is serious, red water wall tube can be seen from the furnace door. When the water shortage is severe, the furnace tube may break, and a burst can be heard, steam and smoke will be ejected from the furnace door and the fire door. By calling water; for severe water shortage, it is necessary to stop the furnace urgently, and blindly feed water to the boiler. Reduce fuel, blast, draw wind, and supply water slowly when water is classified as a slight water shortage.
The main function is to ensure that the monitoring system burner safe and stable operation, the main components are: flame detectors, pressure monitors, temperature monitors and the like. Flame detector: monitoring conditions for forming the flame, and generates a signal reporting programmer. There are three main flame monitoring: photosensitive resistance, electric eye UV ultraviolet, ionizing electrode. Pressure Monitor: generally used for a gas burner, the main high-pressure gas, low voltage detection, and detecting elegant, if burner for high quality best steam boilers, and steam pressure monitoring. Detector Temperature: monitoring and controlling the temperature of fuel (heavy oil).
Startup boiler steam temperature does not mention how high do? A: In the unit to start the process, often encounter steam pressure has reached the requirements, and the steam temperature was too much difference, especially in front of the turbine and the blast furnace or red switch occurs. Should take the following measures: appropriate to increase the amount of coal to improve the furnace heat load; adjust the secondary air ratio, increase the amount of lower secondary air; improve wind, air pressure, increased gas velocity; hydrophobic and full of air and exhaust mother pipe in front of the main steam isolation all hydrophobic.
Fang Group is a fast open class in 2018 to promote important projects for regular classes, taught high-quality content for our customers to offer customized curriculum, careful management, a full range of intentions to provide value-added services, to create a worry-free collaboration experience.