water tube automatic boiler used in textile industry
Battle blue horn sounded, emissions of sulfur, nitrogen and oxygen compounds gradually strict national requirements. To improve the quality of the environment, but also the people a blue sky, in all industries around the environmentally friendly product revolution, Hainan Sinochem Pharmaceutical companies are no exception. By the company investigation and comparison of water tube automatic boiler used in textile industry products, in March 2017 signed a six-ton steam-cleaning integrated condensing gas boiler and steam fast boiler. Tested and post feedback, the boiler equipment installation qualification, operating normally, and successfully passed the inspection by local quality inspection departments of the boiler.
Condensing gas water tube automatic boiler used in textile industry working principle and key points: the concept of condensing gas boiler condensing gas boiler, by definition is condensing gas boiler, condensing gas boiler can now be divided into commercial gas condensing boilers and industrial gas condensing boiler, condensing the product is the difference between the horizontal vertical boiler and condensing boiler two series. The most important is to realize the nature of condensing technology which condensing gas boiler.
Configure and use on steam water tube automatic boiler used in textile industry water supply equipment should look out for steam boiler feed water requirements of the equipment four points: (1) steam boiler feed water system shall ensure safe and reliable water supply. (2) steam boiler should spare water supply equipment. And the number of spare capacity and a water supply device is arranged water supply system, the following request should be satisfied: ① boiler up to two due to the pump work stand ** (one spare). ② Two capacity to pump, not less than 120% of the nominal overall operation of the boiler and the amounts of evaporation. ③ When the boiler room above three feed pump apparatus, which feed water total capacity should be: when the maximum capacity of a feed pump deactivation, the remaining capacity can always run parallel to the pump is not less than the rated boiler all running evaporated 120% of the sum of the amounts. (3) to the pump head (i.e., height of the water column required to overcome the static pressure of the respective dynamic pressure) should be greater than or equal to the algebraic sum of the following: ① water pressure drop difference water supply system (water column hydrostatic) and the water supply system. ② hot water boiler safety valve at the design pressure set pressure. ③ economizer system pressure drop drum. ④ The above three multiplied by the algebraic sum of the amount of 1.05-1.1 rich as appropriate.
7MW WNS series gas-fired hot water water tube automatic boiler used in textile industry for OUTLET MallHot water boilers are mainly used for heating system of cities and enterprises. Maple leaf town outlet mall is located in Songbei District, Harbin and covers an area of 170,000 square meters. The basic form of business operation of outlet mall is set to be outlet stores, travel & leisure and culture & entertainment, covering the elements of shopping, catering, leisure, entertainment, art, etc. Since the winter in Harbin is extremely cold, to improve consumer satisfaction, the project leader of this company decided to open bidding and purchase several sets of heating boilers to provide heat energy for maple leaf town hot spring and outlet mall. ZOZEN successfully won the bidding with excellent products and complete solutions. The sales manager of ZOZEN provided the company with 4 sets of gas-fired hot water boilers (WNS7-1.0/95/70-Q) and 2 sets of gas-fired steam boilers (WNS2-1.0-Q) after conducting a field investigation. WNS series gas-fired boilers are designed and manufactured with domestic and foreign advanced technology and experience, which feature fully automatic running, safety and reliability, high efficiency and environmental protection. Special Equipment Inspection and Research Institute made an energy efficiency test to the WNS boilers, and the results showed that all the indicators were exceeded design requirements; performance had reached international advanced level.