SZL Water Tube 2 Ton Coal Fired Boiler For Textile Printing
Shutdown four tons of gas szl water tube 2 ton coal fired boiler for textile printing steam boiler shutdown and maintenance of fire into pressure shutdown, normal shutdown, emergency shutdown. A pressure fire fire shutdown shutdown pressure applied to temporarily stop the supply of steam, the boiler is shutdown pressure hot standby state. 1, before the pressure reduction appropriately to fire the boiler load, and according to the length of the seam thicker shutdown time, (up to 200mm) to accelerate the speed of the grate, the grate is stopped when rotated about 1.5 meters from the coal seam to the shutter. 2, stop blowers, blower suitably adjusted flap subsections, relying on a lean-burn natural ventilation is maintained. 3, the sewage, to allow the water level in the boiler water level. 4, Yang fire regularly, to prevent rotation of the furnace grate extinguish the fire bed. Young fire first before sewage water, then rinse water level gauge. II. Normal shutdown Normal shutdown for heating period ends, boiler pour fire into the buck repair or maintenance. 1, make a record before shutdown problems in operation, so that after the shutdown process. 2, the coal bucket coal memory runs out, the amount of toner to reduce the wind. 3. Stop the blower, draft fan stop and then the opened door grate ash. 4, after the steam supply is stopped out, the boiler to the boiler water to maintain a high level. 5, close the main steam valve, if the pressure rises to open the air exhaust valve suitable pressure relief. 6, stop the water supply to the boiler and economizer attention to monitoring changes in water temperature, open return pipe if necessary. 7, 4 to 6 hours after the furnace fire bed down exhausted, continued rotation of the cooling grate. Throughout the boiler throttle, the door should be kept closed. Allowed to naturally cool. 8, appropriate to open the pump, the boiler water and sewage. When the pressure drops to zero, open the air valve. 9, when the boiler water temperature is below 70 ℃, boiler water can be exhausted. Shutdown is complete. 10, less than 24 hours during shutdown. Avoid Shutdown cooling process, step-down too fast. Third, emergency shutdown emergency shutdown applies to the boiler accident, g combustion equipment damage, furnace or boiler structure collapsed wall is red-hot, a serious threat to the safe operation of the boiler when; h boiler pressure parts found serious distortion, leakage. when i found flue gas explosion or secondary combustion, boiler and seriously endanger the safety of operating personnel;; when endanger the safety of operation.. the safe operation of the boiler j endanger other unusual circumstances when. 2, the emergency shutdown procedures to immediately stop a blowing coal and reduce the wind; B rotates quickly grate, the pour slag pit coal or sand, wet ash coal burning fire to extinguish. , but not to the firebox water;. c boiler air valve, the relief valve opens quickly exhaust the steam pressure is reduced;. d after the fire goes out, stopping fan, opening the ash door and door, promote air circulation accelerated cooling; 3, emergency shutdown Notes a. when an accident and emergency shutdown due to lack of water, boiler feed water is strictly prohibited to, and shall not be such as to open the air valve or exhaust valve work on preventing boiler from sudden changes in temperature or pressure to expand accidents;. b when filled with water due to an accident and emergency shutdown, should immediately stop the water supply, reduce combustion, open the drain valve and drain, due to lower the water level, while opening the main steam pipe, the sub-cylinder and steam traps mother tube, water and prevent steam pipe with a large number of water hammer occurs. c. emergency shutdown operation to ensure the safety of the main event of an accident to calmly deal with, timely reporting, and make relevant records in the "log table boiler." d. Whether shutdown any case, we must maintain timely contact with steam departments.
Our other fast szl water tube 2 ton coal fired boiler for textile printing in the boiler industry strength already heard, through cooperation proves that our choice is correct. This water-tube boilers installed very quickly, basically no delay our production process, bring benefits to the enterprise. --customer feedback
75 ton coal-fired circulating fluidized bed power station szl water tube 2 ton coal fired boiler for textile printing
CBM provided a 75-ton coal-fired cfb boiler for power generation in a chemical plant in China. This boiler uses circulating fluidized bed combustion technology. The boiler steam pressure is 3.82 MPa, the steam temperature is 450 °C, and the boiler feed water temperature is 105 °C. Our circulating fluidized bed power station boiler has strong fuel adaptability and can burn anthracite, lignite, bituminous coal, lean coal and various biomass fuels.
Coal-fired steam szl water tube 2 ton coal fired boiler for textile printing oil requirements and whether the induced draft fan: fuel steam boiler in the boiler, we believe this a boiler will not feel strange, because the front, some of its articles related to getting to know and understand it, and not know about it yet. So the following, in order to promote familiarity with all of the following, will continue to explain knowledge in this area, in order to have the learning effect. 1.20 tons of coal-fired steam boiler, the standard amount of coal every day, about how much is? 20 tons of coal-fired steam boiler, which is the standard amount of coal every day, and if, the calculation explanation, then, is the need to know the specific values, so in order to give a specific value, such as: rated steam pressure of the boiler, is is 1MPa, the water temperature is 20 ℃, the thermal efficiency of the boiler is 90%, in addition, the standard coal heating value is 7000 kcal / kg, then 24 hours a day if the full load operation, then, with its daily the amount of coal is about 50-56 tons. However, in practice, due to some unavoidable factors, it will lead to its value, and larger than 56.