High Capability Szs Coal Fired Steam Boiler
"Create convenient boiler boutique user" is the eternal quick side mission. To this end, we will make unremitting efforts to push the zero defect product quality and service, striving to "China Clean boiler brand"! Let us work together to guard the blue sky!
About six tons of high capability szs coal fired steam boiler shutdown of a temporary shutdown: It is planned, therefore slow cooling during shutdown protection device, it should also pay attention to safety, pause furnace according to the rules in Chapter IV Fenghuo (pressure fire) get on. 2, safety shutdown: care should be completely stopped even on normal operation plan for 1 to 3 months to be a shutdown, shutdown should maintain more safety injection apparatus, after the shutdown, and other water-cooled furnace to below 70 ℃ when they let go of the gas, open manholes, hand holes, rinse the pot with water scale. 3, emergency shutdown: the boiler operation, when the case of the following circumstances, should an emergency shutdown, and notify the relevant authorities. (1) expanding the cease-fire should first see if the water table level is called to take water law. If Inception water table, water cock side, and then close the steam cock, and then turn on the water faucet open and close repeatedly called after water, still can not see the water. (2) All water supply equipment failure. (3) All water gauge, pressure gauge, safety one of all the failures. (4) a boiler or furnace wall element damage, serious threat to the safe operation of the boiler, emergency shutdown, should focus on preventing the stop of the accident and the specific steps as follows: ① first blowing off; ② the coal on the grate red raking; ③ Close induced draft fan.
6 tons adjusting a combustion gas high capability szs coal fired steam boiler, normal combustion boiler three basic aspects of indicators include a uniform supply of the fuel, reasonable ventilation, adjustment the combustion. 1, to maintain the high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100 ~ 1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. 2, fuel ash to reduce ash content in the combustibles to be below 10%. 3, reducing the temperature of the boiler flue gas exhaust gas temperature should be controlled below 200 ℃. 4, holding furnace negative excess air boiler is 1.2 to 1.4, by adjusting the balance of the blowers to maintain the furnace pressure is -20 ~ -30Pa. 5, the thermal efficiency of the boiler to improve the thermal efficiency of the boiler should be kept above 60%. II. Combustion Adjustment 1, the amount of fuel to air required for combustion and the amount of a reasonable distribution. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. 2, the thickness of the seam and seam thickness configuration grate speed is 80 ~ 120mm grate speed at high, middle and low profile configuration of several commonly used methods:. 9a rapid combustion of thin seam b c thick seam in low combustion. 3 thick seam combustion speed, the segment with the wind blowing principle: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. Normal combustion conditions are: fuel from the coal at the beginning of the fire shutter 300mm, uniform flames, the fire bed formation, at the end of combustion from the end of the grate 300 ~ 500mm. 4. maintain proper furnace temperature to avoid coking. The fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. 6. The residence time of the fuel on the grate in less than 30 minutes.
Our Client from Russia, visited our factory, the boiler manufacturing line. Considering their snack food factory daily steam requirements and rice corn cob biomass fuel advantages, our engineer recommended 4 ton DZL series biomass boiler for him. DZL series biomass boiler, can burn coal fuel and biomass fuel together. This can save fuels costs, and enhance boiler thermal effect. Another feature is DZL series structure, the packaged boiler is easy to ship, small land occupation. We reach an agreements to delivery this boiler in 45 days after receiving the order payments. We can delivery this boiler by load or by sea into Russia. Its is a kind of chain grate boiler, running biomass fuels into its chamber by chain grate. In our company, coal and biomass boiler thermal transferring efficiency can reach 85%.