Nautral Gas Fired Steam Boiler for textile industry
Process safety valve check valve gas nautral fired steam boiler for textile industry is one of the three safety accessories gas steam boiler, when the boiler pressure is too high, the pressure relief valve will automatically exhaust, gas steam boiler is the important safety equipment . The case of a new installation, overhaul, lack of consumer safety valve shutdown and restart more than three consecutive months, have had to re-check safety valve, safety valve to ensure accurate and reliable by the company safety officer, boiler technician, run operators, maintenance personnel together with the completion of the adjustment. Valve adjustment procedure is as follows: 1, the steam boiler when the gas vapor pressure close to the operating pressure of the safety valve, and retest check valve to the air motor exhaust, drainage accident flexibility and reliability of the electric valve, and the panel reinspection situ pressure gauge, the water level of accuracy, such as failure, not allowed to heat the school. 2, ready to call and check the quality of communication tools, a signal indicating whether the good. 3, adjust the safety valves, boiler pressure should be kept stable, pay attention to monitoring gas steam boiler drum level, and maintain normal. 4, steam boiler safety valve to adjust the pressure gauge in place of instructions shall prevail. If necessary using 0.4 or more for the accuracy of the gauge. 5, adjust the safety valve should be carried out only by descending. It should checksum gas steam boiler tuning high pressure safety valve, after the school seizure of the entire set of low pressure relief valve. 6, the following should be in the 0.3MPa, the movement preventing measures must do a good job of setting relatively low pressure steam boiler safety valve safety valve before adjusting. 7, by combustion, and exhaust steam adjust the degree of opening to the air slowly and smoothly up to the required setting pressure. 8, when the gas pressure steam boiler safety valve set pressure to rise if action is normal, then the action and reseating pressure values recorded. If action is not correct or not action should be immediately opened to the air exhaust valve, while the combustion boiler weakened, stop boost, and buck 0.3MPa or less, re-adjust the boiler technician as required by maintenance personnel, until the compliance date. (Lead or lag 0.05MPa action is normal). 9, after the completion valve to adjust gas steam boiler, boiler 0.3MPa or less down to the lifting device and can be installed and fastened to the protective cover, a braking measure required under check valve removal, then Articles 7, 8 verify until all required safety valve calibration check is completed. 10, the safety valve to adjust the gas boiler, check the results recorded in the "safety valve to adjust the recording Visa" within the participants should verify the signatures and Internet safety valve input to the corresponding data in the ledger. During operation gas steam boiler, not only to regularly check on the safety valve, at the same time, we must regularly monitor boiler inspection to ensure that the boiler fully meet the safety requirements!
Mr. Liu, a pedestrian to my company's remote monitoring cloud services platform is very interested that this is a powerful combination boiler industry and Internet technology-based platform enables real intelligent control mode boiler, the boiler industry's future development have a very high confidence. The delegation of the aspects of our company continue to promote scientific and technological innovation strength, low nitrogen emission technology upgrade, focusing boiler lifecycle management fully affirmed. Heartfelt praise to our initiative to extend the upstream and downstream industries, and actively challenge higher level field.
Vertical nautral fired steam boiler for textile industry What are the advantages? With the continuous development and progress of science and technology, the boiler applications also become increasingly wide range of vertical steam boiler is not only elegant appearance, small footprint, and low power consumption, strong performance advantage. So what are the advantages of low power consumption vertical steam boiler what else? Let us to understand a small taping, convenient vertical steam boiler ignition bathing water can be discharged outwardly after two minutes a suitable temperature, without pressure, safety, a normally open tube furnace to the atmosphere, does not have any valves, to ensure safe and reliable operation. And interior of the boiler can be extracted within a few minutes, making repairs or updating the boiler is also extremely fast, short, very convenient. Second, clean the inside of the boiler fouling is a killer, many products are not remove fouling or in addition to science is not complete, but the vertical steam boiler manually to complete the removal of internal boiler fouling, will not leave any dead ends. And heating water and bathing water is not mixed with, but also add a water softener water heating cycle intervention, will not make the whole boiler fouling, very clean. Third, energy saving vertical steam boiler when the water temperature of the furnace is low, reduces the heat loss. And the use of advanced environmental protection technology, can completely smoke-free dust-free, high environmental requirements for cities to achieve energy saving effect. During use, does not produce smoke, the onset of gas boilers together as a whole, the fuel on the grate in cast from the incineration stoker opening, using a high temperature steam and coal seam combined and allowed plenty of chemical attack the combustible gas after reaction, multiple backhaul several cycles, using the pipeline full heating surface, the progress of burning thermal efficiency, heat loss can be reduced to a large extent, energy saving. Vertical steam boiler since the sale of the trust of many old and new customers praise the majority of users. Simple vertical steam boiler maintenance is also very simple, and most businesses will be responsible for after-sales maintenance boiler work, professional service staff, so please do not worry, you can rest assured purchase!
The reason the gas boiler burner increased noise analysis when making use of the gas boiler and found this small fire normal, but this time turn the fire, extinguished or flashing instability. First speaking, that is because of this fire damper of the air volume setting is too large; i.e. after an oil fire because the micro-switch valve (damper outermost that group) inappropriate setting (set lower than the fire damper of the air flow larger) burner gas noise increases, mostly because the oil shut-off valve which is closed or lack of oil into the oil filter clogging; or, this is because of low temperature into the oil, the viscosity is too high or the pump into the oil temperature is too high; oil pump failure; fan motor bearing damage; there is because the fan impeller dirty equipment resulting in large noise. The above-described failure when using gas boiler, but also because the viscosity is too high oleaginous easy to be atomized (heavy oil); cyclones and because improper disc and the nozzle pitch; Note that because the fire is worn or dirty nipple; also because this preparatory tank the heating temperature is too high, causing the oil pump oil feed steam does not conform; or because the fuel inside the boiler resulting aqueous oil. When the above-described fault gas boiler used to perform this process, the test should be done gradually decreases; after heating temperature should be; adjusting the distance (between 0 ~ 10mm); clean or replace; is set to about 50 deg.] C to about; or drain oil change.