biomass micro steam pressure steam boiler
The 4ton biomass biomass micro steam pressure steam boiler is specifically designed to use biomass pellets as fuel. Installed at Vietnam, a tobacco processing facility, the boiler reduces the use of fossil gas. Operating at 16 bar pressure, the boiler has a nominal capacity of 4 ton per hour of dry, saturated steam.
7 ton wood fired biomass boiler
The 7-ton wood chip biomass boiler is a common application in hotels, food processing plants, wood processing plants, and wood is a very common biomass fuel, but it is not suitable for direct use in boilers. In general, biomass such as wood needs to be processed into granules for better utilization. Wood biomass boilers mainly use wood pellets as fuel to generate steam or hot water for various purposes.
In early 2013, fast boiler is a food processing company Luohe a 10-ton condensing biomass micro steam pressure steam boiler installed integrally cloud service monitoring module, by monitoring the data found in March, the maximum pressure in the boiler set small deviation, the small boiler load adjustment range, and it uses a continuous replenishment way. When such a large load changes, the burner will start and stop frequently, adversely affect the boiler. After the burner system to monitor working properly, timely communication with customers, to help customers put pressure adjusted to the maximum deviation of the normal range. Then return to the display data safe range, the maximum starting frequency is reduced to the burner 4 times / hour from 8 times / hour, reduced by the mean starting frequency of 3.7 times / hr 1 / hr reported in June. At the same time gas consumption decreased by 10% to obtain the customer's trust and recognition.
Biomass fired biomass micro steam pressure steam boiler combustion process
The biomass fuel is fed into the furnace screw feeder, where due to the high temperature flue gas and the role of the primary air gradually preheating, drying, fire, burning, this process a large number of volatile precipitation, burn vigorously. After the resulting erosion main heating surface temperature flue gas boiler, the boiler economizer heating surface of the tail and air preheater, and then into the dust, and finally through the chimney into the atmosphere. Not gasified fuel side to the rear of the grate movement until burnout, the last remaining small amount of ash fall behind the grate slag mouth.