Fire Tube Energy Saving 1 Ton Oil Steam Boiler
Solutions and prevention of gas oil-fired boiler flameout Today we'll resolve what about gas fuel boiler flameout solutions and prevention fuel gas-fired boiler flameout Solution: First, the furnace pressure gauge indicates the value suddenly increases, the furnace black can not see the flame, burning furnace sounds disappear, extinguishing the flame supervision devices emit a signal; the temperature dropped sharply atmospheric pressure, the water level dropped after the first rise, and so are flameout phenomenon. Auxiliary flame caused by an accident, such as a fan, blower power interruption, there is an accident signal emitted; fuel supply as a result of intermittent, the boiler is oil or gas pressure drops to zero, only a single burner flame, the furnace may also be thrown skew central flame extinguished burner pressure change; as a result of the fuel supply interruption, the extinguished burner pressure or hydraulic indication may drop to zero, and the fuel consumption, the gas pressure is increased other operating burner. Causes gas boiler flameout are: sudden increase in gas pressure caused from the fire, the solenoid valve malfunction the gas supply interruption, the gas composition has changed so much moisture content is too high and so on. Blower, fan failure, the load is too low furnace pressure is too large excessive leakage and other excessive wind, so that the furnace temperature is too low can also cause the boiler flame. Cause misfire has oil-fired boiler: oil pump failure, the oil surface is exposed inhalation tube, clogging of the oil filter or oil supply pipe, a solenoid valve malfunction or misoperation caused by oil running intermittently. During transport the fuel with steam by heating water; inappropriate position inhalation tube with the pumping of water; improper contaminated oil floating on the water; poor dewatering tank drain plug such that the fuel with water. After the explosion should be taken to prevent the furnace boiler flameout, it must immediately cut off the fuel supply to the furnace, and then block the electromagnetic valve of the gas supply valve to seal off the fuel supply to run the burner. When the action to be fast in order to avoid inheritance or restore fuel supply during operation, causing the furnace explosion. And identify the cause of boiler flameout troubleshooting find a good job and then start the preparatory work. Before starting the boiler should be enhanced ventilation purge, purge time is more than 5min, then procedures ignition. It is forbidden to send fuel directly to the high-temperature furnace without using an ignition spark ignition device to prevent furnace explosions. If due to fan failure caused when the flame should be quickly cordoned off the fuel supply line of each valve, with special attention because the valve is not tight blockade caused by leaking fuel. Ventilation and purging of the furnace and flue in accordance with the approach of an emergency shutdown. Ignition step by step in the recovery operation after the fan. Single burner flame burner only block the fuel supply valve, the burner off a small damper identifying and troubleshooting and then re-ignition by the ignition process. Boiler flameout of prevention: For oil-fired boiler should minimize the possibility of fuel transport, storage and handling of water in all sectors. Tank initiative measures should dehydration and dehydration on schedule. In any case, it should ensure the security of oil supply. The supply of oil and acceptance testing, cutting oil change when the master species. When a large change in oil types, varieties and the need for the oil tank to store the original varieties contaminated test to determine whether the same storage tank, to prevent the density and viscosity differences between a large number of decomposed oil mixed insoluble material, clogging oil pipeline. For the operation of the gas boiler should be closely monitoring the evolution of gas pressure, the timely processing of exceptions thrown up air pressure, ensure the supply pressure in the normal range. To always understand, repair gas composition, gas composition changes when large, to take the necessary adjustment measures on the boiler operation.
Dezhou City, Shandong Province, located in northern China, the winter heating livelihood security is the top priority. According to statistics, the main city such as the German city of existing heating boiler 63 units, for the protection of the safe operation of the winter heating boiler, the past few days, the German city Bureau of Quality Supervision special equipment inspectors to carry out a comprehensive examination of special law enforcement actions against these heating boilers.
Check the main content around the registration and inspection of boilers, operator's safety if the holder case posts, etc to focus your heating boiler operating conditions, in particular the various safety accessories and safety devices especially by the attention of inspectors. By the inspection activities, it may be within the control range as much as possible, to ensure the safe use of heating boilers.
Condensing fire tube energy saving 1 ton steam boiler in order to save more fuel to improve combustion efficiency: In order to improve the combustion efficiency, saving fuel, the fuel quality should be controlled, uniform atomization burner. Non-pressure condensing steam boiler indirectly heated hot water boiler, combustor or the like. To achieve the above object, the following points should be noted: 1 to understand the combustion principle, adjusting the wind ratio of positive oil (gas), to achieve efficient combustion; 2, to maintain a good working condition of the nozzle, the nozzle is not easy too large or too small, the nozzle wear obstruction, carbon status, to ensure good atomization combustion conditions. 3, to maintain proper pressure or hydraulic, pneumatic or steam boilers, such as high or low oil pressure, and a hydraulic or pneumatic pressure is too large or too small, will affect the mixing of fuel and air uniformly. 4, to adjust the burner flame length brains spray angle size and shape of the combustion chamber with fire furnace chamber filled eye, achieve economic combustion. No black smoke, no soot, in the good sense of the coming year running.
Increase productivity boiler system must first be optimized for verification, including the entire steam system for a complete analysis, and focus on some of the energy waste places. Via check can often find opportunities to save energy, increase productivity, and environmental protection have a positive contribution of. Check includes a steam generation, distribution, use and condensate recovery. The main steam waste requiring special attention place: exhaust gas boiler: boiler efficiency emissions system the most important indicators, the loss of energy is the most important place. Combustion air: general air enters the combustion furnace of the genus room temperature, require a lot of heating energy, i.e., the most commonly used power saving mode using a high temperature exhaust gas to preheat the combustion air of boiler, boiler efficiency can be significantly improved. The fuel / air ratio: Proper oil / gas mixture can only complete combustion, if the lack of air, combustion is incomplete, not only smoky pollution, environmental protests caused nearby residents, and easy carbonized grease gun and boiler heating tubes affect performance. If excess air is formed wasted energy, reducing boiler efficiency. Via the oxygen content of the tail gas can appropriately adjust the oil / gas ratio. Oil-fired boiler exhaust gas which content 3%, i.e., the excess air of about 15%, as the standard combustion control.