Automatic 1-2 ton Coal Fired Industrial Steam Boiler
To enhance the thermal efficiency gas boilers What environmental policy: the combustion efficiency of combustion represents the degree of complete combustion. To improve the combustion efficiency of gas boilers and environmental protection, we must try to adjust the combustion conditions and better organization of the furnace, fuel combustion, reducing q3 and q4. Gas boiler environmental protection reduce exhaust gas temperature: at present China's industrial boiler flue gas temperature is high, is one of the main reasons of the low gas boiler thermal efficiency and environmental protection. Each small boiler flue gas temperature decreased 15-20 ° C, 15 ° C decreased every large boiler, a 1% increase in the thermal efficiency of the boiler gas. Accordingly, to try to reduce exhaust gas temperature flue gas heat recovery, reducing heat losses q2, the fuel savings. Softened water supply and condensate recovery: boiler feed water softening treatment and condensate recovery measures is to improve the thermal efficiency of the boiler. Raw water contains various impurities and fouling material, if not the water treatment boiler fouling. Low thermal conductivity of the scale, so that once the heating surface fouling due to increased thermal resistance, gas boiler output decreased to increase coal consumption, reducing the thermal efficiency of the boiler. Boiler keeps running at rated load: When natural gas boiler overload, due to the amount of fuel to be increased, the coal seam thickened, grate speed, air volume must be increased to meet the increased load required. Thick coal seam and grate faster incomplete combustion of the solid increase in losses due to increased air volume, the short residence time in the furnace flue gas, some burning of combustible gas has not finished on the drain with the flue gas, so incomplete combustion gas heat loss is increased. Meanwhile, when the overload operation, since the furnace temperature is increased thickening seam, exhaust gas temperature increase accordingly, so that heat loss is increased. Boiler low load operation, the amount of reducing gas, the furnace temperature is lowered, deterioration of the combustion conditions, incomplete combustion loss q3, q4 is also increased. When the boiler load is only 50%, due to a significant reduction in temperature in the furnace, it is difficult to maintain stable combustion furnace. Low load operation relatively increased heat loss, the overload or low-load operation the boiler will result in reduced thermal efficiency of the boiler. Strengthen the insulation, sealing, anti-leakage, anti-risk: Due to the wall gas boiler, soda temperature heat pipe system is better than the boiler room air temperature is high, so that part of the heat pipe system and soda furnace wall to radiation and convection to the loss of ambient air, heat radiation loss becomes the boiler. Only the furnace heat of the heat loss, reduces the temperature of the furnace at the same time, it affects the combustion. Therefore, the use of advanced insulation materials to strengthen the walls and heat insulation boiler pipes, reducing heat loss and improve the thermal efficiency of gas boilers and environmental protection. Temperature and security issues to resolve gas automatic 1-2 ton coal fired industrial steam boiler
Do you know what it is gas energy saving boiler gas boiler energy-saving and environmental protection Many customers do not believe, how coal energy-saving environmental protection? Zheng Boiler Group today for everyone to analyze environmental history of the gas boiler. Energy saving gas boiler pot Zheng Group production of a new product, a gas automatic 1-2 ton coal fired industrial steam boiler. Energy saving gas boiler pot Zheng Group production of a new product, a gas steam boiler and gas hot water boiler, gas steam boiler models which are mainly DZL steam boiler gas chain, DHL chain gas steam boiler, SHL chain gas steam boiler SZL chain and energy-saving gas steam boiler and circulating fluidized bed boilers. Zheng pot boiler gas saving and environmental protection are "perfect green and environmentally friendly boiler boiler auxiliary boiler machine environmentally friendly application process installation service" model pioneered go on the road "environmental effects Enhancements". In addition to these types of environmental protection boiler, auxiliary equipment, environmental protection is also an important part of the environmental process. Energy saving boiler fuel gas separation efficiency as high as 97.97%, combustible low-quality coal, good desulfurization effect, can significantly reduce sulfur corrosion of equipment, in favor of low quality coal combustion, coal adaptability strong. Boiler fan low energy consumption, high economic efficiency, and can effectively avoid the fan big horse car phenomenon. To more than dust and coal in the coal auxiliary, not only an automatic cleaner, convenient safe, maintenance.
Shutdown four tons of gas boiler automatic 1-2 ton coal fired industrial steam boiler shutdown and maintenance of fire into pressure shutdown, normal shutdown, emergency shutdown. A pressure fire fire shutdown shutdown pressure applied to temporarily stop the supply of steam, the boiler is shutdown pressure hot standby state. 1, before the pressure reduction appropriately to fire the boiler load, and according to the length of the seam thicker shutdown time, (up to 200mm) to accelerate the speed of the grate, the grate is stopped when rotated about 1.5 meters from the coal seam to the shutter. 2, stop blowers, blower suitably adjusted flap subsections, relying on a lean-burn natural ventilation is maintained. 3, the sewage, to allow the water level in the boiler water level. 4, Yang fire regularly, to prevent rotation of the furnace grate extinguish the fire bed. Young fire first before sewage water, then rinse water level gauge. II. Normal shutdown Normal shutdown for heating period ends, boiler pour fire into the buck repair or maintenance. 1, make a record before shutdown problems in operation, so that after the shutdown process. 2, the coal bucket coal memory runs out, the amount of toner to reduce the wind. 3. Stop the blower, draft fan stop and then the opened door grate ash. 4, after the steam supply is stopped out, the boiler to the boiler water to maintain a high level. 5, close the main steam valve, if the pressure rises to open the air exhaust valve suitable pressure relief. 6, stop the water supply to the boiler and economizer attention to monitoring changes in water temperature, open return pipe if necessary. 7, 4 to 6 hours after the furnace fire bed down exhausted, continued rotation of the cooling grate. Throughout the boiler throttle, the door should be kept closed. Allowed to naturally cool. 8, appropriate to open the pump, the boiler water and sewage. When the pressure drops to zero, open the air valve. 9, when the boiler water temperature is below 70 ℃, boiler water can be exhausted. Shutdown is complete. 10, less than 24 hours during shutdown. Avoid Shutdown cooling process, step-down too fast. Third, emergency shutdown emergency shutdown applies to the boiler accident, g combustion equipment damage, furnace or boiler structure collapsed wall is red-hot, a serious threat to the safe operation of the boiler when; h boiler pressure parts found serious distortion, leakage. when i found flue gas explosion or secondary combustion, boiler and seriously endanger the safety of operating personnel;; when endanger the safety of operation.. the safe operation of the boiler j endanger other unusual circumstances when. 2, the emergency shutdown procedures to immediately stop a blowing coal and reduce the wind; B rotates quickly grate, the pour slag pit coal or sand, wet ash coal burning fire to extinguish. , but not to the firebox water;. c boiler air valve, the relief valve opens quickly exhaust the steam pressure is reduced;. d after the fire goes out, stopping fan, opening the ash door and door, promote air circulation accelerated cooling; 3, emergency shutdown Notes a. when an accident and emergency shutdown due to lack of water, boiler feed water is strictly prohibited to, and shall not be such as to open the air valve or exhaust valve work on preventing boiler from sudden changes in temperature or pressure to expand accidents;. b when filled with water due to an accident and emergency shutdown, should immediately stop the water supply, reduce combustion, open the drain valve and drain, due to lower the water level, while opening the main steam pipe, the sub-cylinder and steam traps mother tube, water and prevent steam pipe with a large number of water hammer occurs. c. emergency shutdown operation to ensure the safety of the main event of an accident to calmly deal with, timely reporting, and make relevant records in the "log table boiler." d. Whether shutdown any case, we must maintain timely contact with steam departments.
Hefei Limin Pharmaceutical Co., Ltd. Nanjing Military Region, formerly the backbone of pharmaceutical companies, the main drug is slowly swallow rather teabag, relying on advanced R & D platform to carry out contract manufacturing, OEM OEM and other business cooperation. China's environmental protection development trend began to take shape, many environmental policies have been put forward for a positive response to the national environmental policy, Limin Pharmaceutical decided to introduce a gas station automatic 1-2 ton coal fired industrial steam boilers. After an investigation of the boiler market, Limin Pharmaceutical fast boiler is strong comprehensive strength and wealth of experience working for many years in the pharmaceutical industry to attract, party fast according to the actual needs of customers for its recommendation of one of Taiwan 4 tons of steam condensate gas-fired steam boiler (WNS4-1.25-YQ).