high effiency automatical boiler
Circulating fluidized bed high effiency automatical boiler reduce the pollutant emissions:
Circulating fluidized bed boiler through reconstructing the flow of fluidized bed,under keep the advantages such as the CFB technical in strong adaptability of coal,pollution emission,control cost. in order to reduce the power plant and the available rate, reducing the emission of pollutants.
Group multiple departments quality systems, technology department, production systems, development systems, with the assistance of outside experts, please, to overcome the difficulties, overtime, and fulfill all the preparatory work. Assessor staff often give up personal time off from work carried ASME study and training, frontline staff overtime for practical operation of the exercise. All those involved in the trial personnel in the company "professional life, work lean" under the guidance of the core values of continuous fighting, the various problems couplet review group proposed were closed, one-time passed the ASME certification.
Daily Maintenance of environmental protection and efficient gas steam high effiency automatical boiler steam boiler gas are the main features of recent years because the state put forward higher requirements for environmental protection, many companies have purchased after rectification gas steam boiler, which allows gas steam boiler It has been more widely used, usually purchased with the strength of the manufacturers of the products, can use more secure stability, but also the stability of gas steam boiler and routine maintenance have a great relationship, here to introduce the gas steam boiler routine maintenance methods. First, the number of regular precipitation material will appear in the combustion chamber after long-term use of clean gas steam boiler the most practical, long-term accumulation of these deposits, is likely to cause instability phenomenon appears to run gas steam boiler. Thus every consumer should be a fixed time necessary for its complete cleaning, the use of high contamination factor in some environments, for periodic cleaning time shortened. Second, prevent bump gas steam boiler should not move it after installation, to prevent the move will lead to the internal components of the boiler loosening phenomenon. And during the move, the phenomenon is likely to occur and other items bump, although the product design anti-bump when will production, but severe shock and vibration inevitably will not have a serious impact on the internal boiler, boiler failure cause overhaul and had to stop production. Third, to avoid corrosion gas steam boiler must avoid being exposed to, once the boiler corrosion, which severely shortens the life and aesthetic appearance of the gas steam boiler corrosive materials, and therefore do not always pay attention to the corrosive Item close gas steam boiler, chemical cleaning agents are also used in cleaning corrosive cleaning. These are gas steam boiler easy to use method of routine maintenance, gas steam boiler does not require particularly careful care under normal circumstances, but about every six months to do some thorough cleaning is very necessary, in addition, if not compelling, do not move them, to prevent inflicting damage to the bump, with the article followed by contacting corrosive and do not let the gas steam boiler.
Europe and America in the early 1970s are already using condensing technology. Was condensed using a contact type technique, i.e., a high temperature flue gas into direct contact with water, a water absorption of latent heat, cooling flue gas emissions. This is the predecessor of the large industrial high effiency automatical boiler economizer is used. The following disadvantages: 1, will make the acidified water once, must be frequently and chemical bases, the cost is not low. 2, once the water is open, it can not be used in a closed system. 3, larger, not available for domestic boilers.